Family Owned HVAC Repair Company
Comfort Control has been the reliable, 5 Star rated HVAC company for heating & AC repair service in Suwanee, GA and the surrounding areas since 1992.
Read our reviews from Suwanee, GA to see how our craftsmanship, professional trained technicians and customer service has provided complete satisfaction for our heating and air conditioning services.
Air Conditioner & Heating System FAQs
There could be a number of reasons why hot air is coming out of your vents instead of cool air in your home near Suwanee, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Clogged Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home, not allowing cool air to circulate.
- Low Refrigerant Levels - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Broken - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
You should have an HVAC maintenance service done on your unit twice a year in Suwanee, GA. This service is also known as a tune-up on your heating and cooling system, as the technicians performing the service will clean, inspect and correct any problems your system may be having.
The cost to repair your home air conditioning system near Suwanee, GA really depends on what is wrong with your system. On average, AC repairs cost about $350 as most of them are pretty minor in scope. Larger repairs, however, can cost as much as $2,000 for complicated leak repairs or compressor replacements.
To determine whether your indoor air is clean in your home near Suwanee, GA, the experts at Comfort Control can help. We will perform an Air Quality Evaluation to test your home’s indoor air quality. We will use a high-sensitivity laser particle scanner to measure the particulate parts per million in the air and then analyze the results. To schedule your evaluation, contact us today!
for Suwanee, GA
James - Suwanee, GA
Techs from North Atlanta Plumbing were very courteous and proficient. Was a pleasure to have them in our home
Jason - Suwanee, GA
Jason - Suwanee, GA
Extremely professional and helpful
Did a great job!
Shonagh - Suwanee, GA
Arrived within the time window. Was polite and efficient!
The Tech was a good lid
TOM - Suwanee, GA
Not happy with my 5 week old system needing service already but liked the tech Alex. Had to change my Saturday schedule for the day to accommodate the service call
As always, Comfort Control provides dependable, GREAT SERVICE
WILLIAM - Suwanee, GA
"Ricky" expediently, expertly, and cordially took care of us, performing our annual Spring AC maintenance [late...OUR FAULT!] yesterday, 07-08-21. Purchase and installation of this Amana Heating/AC system from Comfort Control -- way back in 2011 -- was one of the absolute best home improvement investments we've ever made.
Brian - Suwanee, GA
Shelliy - Suwanee, GA
Came out fast, professional and fixed the problem
ELLY - Suwanee, GA
The technician who visited my home was very thorough and professional, while explaining the issues with my hvac, and my options. Jordan did an excellent job.
Atchyut - Suwanee, GA
Explained it very well as per his knowledge.
JOHN - Suwanee, GA
Reese did quickly diagnosed and repaired the issue with our HVAC unit. He is a “Pro”
JOHN - Suwanee, GA
Great, professional attitude and service. Technician was very good/truthful about status of system.
ANNIE - Suwanee, GA
He did awesome!
KIRK - Suwanee, GA
Jason - Suwanee, GA
Coil was never cleaned during maintenance, washed out coil. Need to return to do a FULL chemical clean on coil.
Called, left voicemail, knocked twice and rang bell. No answer.
Ac service in Suwannee. Discovered failed secondary controller. Replaced controller installed compressor saver and changed filter. System cooling at this time.
Installed two window units until part arrives.
No cool suwanee. Completed diagnostic found leak in evap coil. Needs to be replaced for permanent fix.
No cool suwanee. Completed diagnostic. Found drain line filled up due to cut wrong going into pump. Cut drain line properly. Ensured proper drainage. Tested pressures. System cooling at this time.
2.5 ton AC, Furnace and Coil 10 year parts 10 year labor lifetime unit replacement compressor and heat exchanger warranty supply plenum
No cool suwanee. Completed diagnostic. Found evap coil leaking heavily. Ac is 12 years old. Furnace is considerably older. Recommend replacing full system for optimum efficiency.
3 ton AC and Coil 10 year parts 10 year Labor Lifetime outdoor unit replacement compressor warranty Move unit to the right where bush is/was Fix gas leak on furnace at T connection
Maintenance Suwannee. Leak checked both evap coils, found no leaks. Capacitors for both indoor units are within range. Cleared drain lines. Blower wheels are clean. Outdoor capacitors are within range. Pressures are within range. Main floor unit is old and struggling but still cooling at this time. No water safety on either indoor system, recommend installing float switches on both. Both systems are cooling at this time.
A/c maintenance in Suwanee. Unit is in the garage. Changed filter, blower wheel is clean, evaporator coil is clean, flush drain line. System is cooling at this time.
Compressor is over amping and fluctuating amps, evaporator coil is leaking R-22 refrigerant, coil is dirty from dryer vent above it, small gas leak on T joint sediment trap going to system. Install set for Wednesday. 3 ton B width. Thank you for choosing comfort control.
Maintenance Suwannee. Checked for leaks in both indoor units, no leaks detected. Checked filters, filters were clean. Checked drain lines. Both blower wheels were clean. Capacitors indoor and outdoor were in range for both units. Pressures for both units were within range. Cooling at this time.
2 A/c maintenance in Suwanee. 1st unit is in the attic. System is cooling at this time. Flush drain line, blower wheel is clean, evaporator coil is clean, changed dirty filters. 2nd unit is in the basement. Blower wheel is clean, evaporator coil is clean, flush drain line. Changed filter. Basement: customer wants industrial duct work look. Basement is 18â€™ x 26â€™
Follow up on Monday
Completed check on pressures. Pressures are still good at 9.8 subcool matches with manufacturing spec of 9 degree subcool needed. System cooling properly at this time.
Ac maintenance in Suwanee. Tested operation of 2 systems. Discovered main level system with weak secondary controller, both systems need compressor savers to reduce stress on compressors. Both systems need duct cleanings and ultraviolet light systems to combat organic and viral growth in systems and throughout the home. Replaced secondary controller in downstairs system and installed compressor savers in both systems. Systems cooling at this time.
New system is freezing at the coil. Threw system in heat to melt ice on coil. Leak on system. Recharged to proper pressure. Need to come back a week from now to see if pressures are same.
A/c maintenance in Suwanee. Unit is located in the attic. Changed filter, blower wheel is clean, evaporator coil is clean, flush drain line. Condensing unit was clean. Pressure are good. System is cooling at this time.
3 A/c tune up in Suwanee. 2 units are in the basement. 1st unit is for the basement. Unit was not cooling when I got here I diagnosed unit and found unit not turning on. Basement unit has a leak in the evaporator coil. Unit does not have any refrigerant at this time. Evaporator coil needs to be replaced. Coil is still under warranty. 2nd unit is the main level. Unit is cooling at this time. Did find a really dirty filter and evaporator coil was a bit iced up. Blower wheel is clean, evaporator coil is clean. Drain line looks good. 3 unit is in the attic. Blower wheel is clean, evaporator coil is clean, drain line looks clean. System is cooling at this time
Maintenance suwanee. Completed maintenance found upstairs and main system with weak capacitor. Found main system with dead outdoor capacitor. All three systems slightly dirty blower wheel. Cleared all drain lines. Changed all filters. Replaced weak and dead capacitors. Main and basement system missing secondary water safety. Found no leaks in all coils. System is cooling at this time.
Ac service in Suwanee. Discovered both indoor coils leaking refrigerant from evaporator coil. Continuously got detection with leak detector. Gave estimate for replacing both indoor coils. Homeowner does not want maintenance membership. Bill cain was the reference.
Maintenance. Suwanee. Complex maintenance on 2 systems. Changed filters. Cleared drain line. Upstairs blower is dirty and needs to be cleaned. Upstairs coil is clean with very little rust. Downstairs blower is clean and coil is rusted and corroded. Did not find any leaks at the time. Outside. Upstairs fan motor is bad and needs to be replaced as well as downstairs outdoor capacitor. Replaced both parts. Systems cooling at this time.
Found short in low voltage wire. Replaced wire to outdoor unit and furnace. System working at this time.
Ac service in Suwannee. Gathered filter information to order and signed homeowner up for maintenance membership. Order filter, need to return to change and perform maintenance