Comfort Control has been the reliable company for value cooling and heating in Suwanee, GA and the surrounding areas since 1992.
Read our reviews from Suwanee, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
There could be a number of reasons why hot air is coming out of your vents instead of cool air in your home near Suwanee, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Clogged Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home, not allowing cool air to circulate.
- Low Refrigerant Levels - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Broken - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
You should have an HVAC maintenance service done on your unit twice a year in Suwanee, GA. This service is also known as a tune-up on your heating and cooling system, as the technicians performing the service will clean, inspect and correct any problems your system may be having.
The cost to repair your home air conditioning system near Suwanee, GA really depends on what is wrong with your system. On average, AC repairs cost about $350 as most of them are pretty minor in scope. Larger repairs, however, can cost as much as $2,000 for complicated leak repairs or compressor replacements.
To determine whether your indoor air is clean in your home near Suwanee, GA, the experts at Comfort Control can help. We will perform an Air Quality Evaluation to test your home’s indoor air quality. We will use a high-sensitivity laser particle scanner to measure the particulate parts per million in the air and then analyze the results. To schedule your evaluation, contact us today!
for Suwanee, GA
JAY - Suwanee, GA
Caroline - Suwanee, GA
We had Vu Tran as our technician. He knows the stuff very well and is very informative. No doubt an excellent service!
Nice Young man
DAVID - Suwanee, GA
Vu was great to interact with. Very knowledgeable. He used a very methodical approach to solve the problem.
Mahendra - Suwanee, GA
By provided excellent work & service.
ERIK - Suwanee, GA
Reese did a great job and was very personable
Friendly, Quick, Knowledgeable
Angelia - Suwanee, GA
Our tech Jon was great. He was friendly, wore a mask and shoe covers, diagnosed the problem quickly and got it repaired for us.
Marcia - Suwanee, GA
Vu provides outstanding service. He is a very thorough technician. He found several issues that needed to be corrected in my new house. I can always depend on him to look out for the homeowner’s best interest. I have been a Comfort Control customer for over 20 years in my old house and look forward to having them service the units in my new home.
Reliable service on time
CARL - Suwanee, GA
Great Thorough Service!
CARL - Suwanee, GA
Great service, great technician very thorough. I have confidence that we will have a smooth running system.
Never use any other company!
Jennifer - Suwanee, GA
This company is awesome. All staff are knowledgeable and nice. Prices are very reasonable! I really appreciated the cooler with cookies inside!! Kids love them!!
Emergency a/c service
JOHN - Suwanee, GA
Blower fan motor and transformer broke on (hot) Sunday afternoon. Contacted Comfort Control and they had a tech out within 3 hours. After short consultation of options tech made immediate repairs and had system up and running in a short time. Great service from a great company.
prompt, efficient service
WILLIAM - Suwanee, GA
We've been very happy with the new furnace/AC we purchased from and had installed by Comfort Control several years ago. And following a twice-per-year check/maintenance/service has kept everything running A-o.k.!!
STAN - Suwanee, GA
The Best Service ever!!
PETER - Suwanee, GA
Professional, straight to the point, knowledgeable, would recommend Vu to anyone that needs their system looked at.
Josh - Suwanee, GA
Great service, very helpful Technician
Lawrence - Suwanee, GA
Jennifer - Suwanee, GA
Vu was sent out to us after our home warranty company sent us 3 techs from 2 different companies. Vu was very through and explained everything and took pics. He showed us what the previous techs did and didn’t do. While we continue to still have the issue, Vu was great. Called company and you all have a tech in the way.
Latetia - Suwanee, GA
ROBERT - Suwanee, GA
Priya - Suwanee, GA
Brian - Suwanee, GA
Brennen - Suwanee, GA
Terrific service once again!
LIZ - Suwanee, GA
Tracey - Suwanee, GA
Very informative in helping us make decisions!!
BRANDY - Suwanee, GA
Mark was excellent. Very professional and personable.
HVAC heating issue in Suwanee Georgia . Looked over heating system . â€¢Got the pilot lit for the furnace in the basement . Going to complete a tune up for the basement furnace. Checking the performance and safety for this heating system . â€¢Found the inducer has high amps . Due to age of the equipment. â€¢ High limit switch was tripping on todayâ€™s visit and has burn marks on the switch. High limit switch is going bad . Would suggest replacing that part . â€¢Flue pipe is single wall would highly recommend being double wall due to the way the furnace combust . â€¢System has no form of water safety to prevent water damage in the basement would highly recommend. â€¢Would highly recommend upgrading the HVAC equipment due to age and conditions/ lack of efficiency of the old technology . If not interested in upgrading at this time would suggest putting this machine on a maintenance program . â€¢Indoor coil is very rusty and will eventually lead to the R22 leaks . Set up a
â€¢Completed two system heating maintenance in Suwanee Georgia . Checked safety and performance. Checked heating elements and heating integrity. Today is the prepaid visit for the maintenance. â€¢Main floor furnace . Found the flame reader is getting weak took pictures. Would highly recommend replacing that electrical part to prevent future issues. $159.80 part is under warranty but the labor and time is not . Family is going with replacing the flame reader today . Replaced electrical part and working at speck levels . â€¢Upstairs furnace . Replaced restricted air filter with a new April air 610 filter . $55 . System is heating at this time 🙂 . â€¢Also sending the family a proposal on installing UV air purification systems to the air plenums on the HVAC equipment. â€¢Total today $214.80
Free consultation in Suwanee for new hvac system
Complete 3 heating furnace tune up special in Suwanee. Change all 3 filter, check safety and operations. Find both upstairs and main level Armstrong gas furnace 19 year old operating with weak flame sensor, worn ignition, weak blower capacitor, rusted Evaporator coil and missing water safety. Find upstairs furnace power switch overheated and damage and control board resistor overheating. Find downstairs furnace overheating and high supply temperature and flue pipe operating at 420 degree. Blower assembly very dirty. Find basement Airhandler system operating with rusted evaporator coil and bio growth. Due to system age and worn conditions, suggest to upgrade system.
Complete 2 heating maintenance pm check in Suwanee. Change filter, check safety and operations. Find upstairs air conditioner unit was not operating due to breaker was set on off, turn on breaker and system operating. Find 6 year old carrier furnace operating but oversized for house, missing return box. Find downstairs heating furnace operating with rusted heat exchanger, worn motor, gas valve and high CO level. Due to system age and poor conditions, suggest to upgrade system. Customer need consultation visit
Water leak suwanee. Completed diagnostic. Drain line was clogged. Float switch did not kill system. Cleared drain line. Repositioned float switch and tested. Float switch works. Tested drain. Water flowing properly. No water accumulating in return box. Freon levels are good. System cooling at this time.
Replace Lennox 4 Ton evaporator coil in attic with 5 Ton Lennox evaporator and replace metering device for system. Pressure and recharge system to manufacturer spec. Replace furnace control board. System operating at this time. Need to schedule in November to do heating maintenance.
No cool main level Goodman 15 year old air conditioning system in Suwanee. Sign 3 CCI plan and complete 3 heating maintenance. Change 2 16x25x1 filter, check drain and clean 3 condenser coil. Find both heating system operating with weak flame sensor, worn ignition and weak blower capacitor. Find both Evaporator coil In attic leaking and baldy rusted. Both system missing in-line water protection. Find both condenser with low charge and burnt damage capacitor and line wire. Due to system age and conditions, suggest to upgrade equipment. Customer want to repair system for now. Recharge both system with R22, replace main level unit capacitor and repair wires. Replace flame for upstairs system in attic. All 3 system operating at this time.
1 Ac coil complete in Suwannee. thank you for your business! Mark and Gavin!
5 - 8â€ 3 - 6â€ 2 - 4â€ 8â€ in each bed room and hallway. 6â€ in master bath and by master bed. 4â€ in master closet and hall bathroom Add 8â€ return in bonus up high. Add 8â€supply in bonus room on opposite side close to window wall.
No cool master bathroom system in Suwanee. Check and Find system short cycling due to compressor not starting properly and shut off on safety. Install hard start kit and sureswitch main electrical kit with time delay to prevent system coming on and off. System operating at this time.
No cool in Suwannee, arrived on site, found 1/3 of the plenum for main level system had torn away from unit creating a massive air leak. supported front of plenum and Re-sealed. No other issues present at this time. Signed customer up for a 2 system maintenance to start in fall
Replace the outdoor 2.5 ton unit. Attic insulation is far below codes R38. Trusses are exposed, currently averaging r19 or less. This will allow substantial heat gain into the home from excessive attic heat. Upstairs ducting is grossly undersized and poorly insulated. There is currently a 7 degree temperature rise in air between the supply plenum and the registers. This is also being read early in the day before attic temperature is high. Strongly recommend correcting ductwork and attic insulation for optimal capacity and efficiency. System will continue to struggle until these are addressed.
No cool upstairs system for Payne system in Suwanee. Test replaced evaporator coil and system still not operating properly. Check and find duct system in poor conditions and undersize. Find low insulation in attic. Customer have 2.5. Air conditioning system and duct capacity of 1.5 Ton. Find ac unit compressor also not operating properly and not compressing proper charge. Working with Jeff on duct Upgrade. System operating at this time. Warranty call back.
NO cool in Suwannee. Arrived on site, found system not cooling properly due to clogged condenser coil and active leak in evaporator coil. Signed up for maintenance program and cleaned outdoor unit. Charged with 1lb of r22. Found other concerns with unit, customer knows and is planning on replacing equipment soon. Unit is operating, but not at peak efficiency. Recommend replacing equipment.
Water leak in Suwanee. Arrived on site to find system off due to aux pan full of water tripping safty switch. Found clogged p trap. Replaced with EZ trap. Tested system. Unit is operating normally at this time.
No cooling in Suwanee, Georgia . Tested system and found the following issues: blower capacitor is weak, system is very low on r22. Sending consultant out to give pricing on new system.
Warranty callback, no charge to customer. Find inducer assembly motor keep running for furnace due to fail control board. Control board already been order. Remove inducer motor power and stop the noise. System operating at this time.
Ac tune up in Suwanee, Georgia. Two systems. Tested mechanical and electrical components. Found basement system with very weak blower capacitor (5uf). Main level system has a very weak blower capacitor as well (7.5uf). Main level blower wheel is very dirty. Found basement system low on r22. Basement main electrical switch is worn. Because of age and r22 refrigerant leak, recommend upgrading basement system to a more reliable, more efficient system. Chemically washed condenser coils. Customer just wanted electrical repairs for now. Replaced both blower capacitors and basement main electrical switch.Systems are cooling at this time.
Ac maintenance in Suwanee. Cleaned outdoor coils and checked all components. All components tested within normal manufacturing spec. System has no drain line water safety or compressor saver to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the system. System cooling at this time
No cool Lennox system in Suwanee. Find drain system clogged and water back up into furnace. Find furnace control board fail and calling inducer assembly to operate for heat and not heat are being call. Find 3 year old Lennox air conditioning system miss match, evaporator coil 4 Ton capacity and ac unit 5 Ton capacity. System not cooling will. Need to replace e with 5 Ton evaporator coil in attic, need clear clogged drain line and need to install inline water protection in attic. Need to replace furnace control board. Sold CCI plan and new evaporator coil in attic. Clear drain for customer and vacuum water. Add inline water protection and hard start kit. System operating at this time. Need to wait for coil and control to come in.
Ac service suwanee. Completed diagnostic. Found reversing valve wire in b slot at thermostat. Moved to o slot. System is cooling.
No cool main level system. Check and find tempstar system fail in Buford due to condensation pump not empty condensation water from air conditioning system. Find find safety switch not yet remove from install. Remove safety switch connector and system operating at this time. Warranty call form service call. No charge to customer.
Ac repair in Suwanee. Discovered upstairs drain line clogged and tripping drain safety which shuts system down. Cleared drain line. System operation normal at this time