Family Owned HVAC Repair Company
Comfort Control has been the reliable, 5 Star rated HVAC company for heating & AC repair service in Suwanee, GA and the surrounding areas since 1992.
Read our reviews from Suwanee, GA to see how our craftsmanship, professional trained technicians and customer service has provided complete satisfaction for our heating and air conditioning services.
Air Conditioner & Heating System FAQs
There could be a number of reasons why hot air is coming out of your vents instead of cool air in your home near Suwanee, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Clogged Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home, not allowing cool air to circulate.
- Low Refrigerant Levels - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Broken - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
You should have an HVAC maintenance service done on your unit twice a year in Suwanee, GA. This service is also known as a tune-up on your heating and cooling system, as the technicians performing the service will clean, inspect and correct any problems your system may be having.
The cost to repair your home air conditioning system near Suwanee, GA really depends on what is wrong with your system. On average, AC repairs cost about $350 as most of them are pretty minor in scope. Larger repairs, however, can cost as much as $2,000 for complicated leak repairs or compressor replacements.
To determine whether your indoor air is clean in your home near Suwanee, GA, the experts at Comfort Control can help. We will perform an Air Quality Evaluation to test your home’s indoor air quality. We will use a high-sensitivity laser particle scanner to measure the particulate parts per million in the air and then analyze the results. To schedule your evaluation, contact us today!
for Suwanee, GA
Speedy expert service
TONY - Suwanee, GA
Tech arrived per his estimate, quickly assessed problem & estimated price & time for repair
RICH - Suwanee, GA
Brett did a great job, very professional.. thank you
Mimi - Suwanee, GA
Good service as always
Walter - Suwanee, GA
Reese has serviced us before and he is respectful and knowledgeable. Great service
Great service and helpful
Lawrence - Suwanee, GA
Garrett was super helpful again with getting us a new AC unit. He’s is always a joy to work with.
Great friendly service!
Lawrence - Suwanee, GA
Christian was a great technician, very friendly, knowledgeable and helpful.
Excellent Service as Always
SCOTT - Suwanee, GA
Very quick, efficient and skilled.
Rajeev - Suwanee, GA
GREAT service. Very professional.
Tammy - Suwanee, GA
Chris was very upfront and professional.
Robin - Suwanee, GA
Professional;knowledgeable, on time. John was very courteous and was respectful of our property. Great job!
DANNY - Suwanee, GA
ARO - Suwanee, GA
Great and Thorough Service
John - Suwanee, GA
Tech was professional, respectful and timely. Advised me of everything that my system needed in terms I could understand. Arrived in the window of time quoted, Called 30mins prior to arrival to advise he was in route. Would Highly Recommend Brett Castell as a service tech.
JON - Suwanee, GA
Michael - Suwanee, GA
2 system ac maintenance is Suwanee. Changed filters with customer supplied filters. Cleared drain lines. Washed outdoor units/coils. Checked mechanical and electrical components. Recommend attic tent for additional efficiency, keeps conditioned air from escaping int the attic. Found main electrical switch for main condenser not functional, replaced under full warranty. System is operating now. Recommend compressor saver hard start kit for both condensers to take a load off the compressor on start up and help extend the life of the systems. Systems are operating normally at this time.
Water leak in suwannee. Arrived on site, found condensation pump running constantly, but not pumping water out of the house. Replaced condensation pump. Unit is operating normally at this time
Two system cooling maintenance in suwannee. Arrived on site, checked filter and cleared drain line, checked electrical connections, amp draw capacitance, cleaned outdoor coil and checked refrigerant pressures. On diakin mini split I found that the fan blades for the head had broken off in places, throwing off balance making loud noise and impeding free rotation. Main unit, recommend installing surge protector to each piece of equipment and compressor assist kit to outdoor unit to prolong the life of the compressor. Unit is operating normally at this time.
Maintenance suwanee. Completed maintenance on 3 systems. Main and basement systems are 3 years old. Both have clean blowers clean coils. Changed filter. Water panel is good. Safety switches working. Temp difference is good. Air flow is good. Replaced UV light. Upstairs system has clean blower wheel. Evap coil is rusted and has corrosion on it. Capacitor is slightly weak but still within range will keep an eye on that. Changed filter. Missing secondary water safety device to protect furnace from water damage. Also recommend putting UV light and surge protector on upstairs system. Water heater is old and having trouble getting up to temp. Recommend replacing.
Found cardboard flap still in condensate pump. Pulled flap out. System came on and started cooling properly.
Ac maintenance in suwanee Ga, two systems. Checked all electrical and mechanical components. Checked filters, cleared drain line. Chemically cleaned both ac condensers. Found down stairs blower capacitor to be weak(6/10). Replaced blower capacitor.All other functions are functioning properly at this time. System cooling at this time.
3 system ac tune up in Suwanee. Cleared drain lines. Changed filters including Aprilaire 810. Checked mechanical and electrical components. Recommend surge protection for each indoor and outdoor unit. Recommend compressor saver hard start kit for main level unit to start smoother and extend life. Recommend changing Aprilaire 810 filter for upstairs furnace. Recommend pull and clean service for all 3 blower wheels. Recommend replacement of Apco 2 year bulb for basement air handler. Systems are operating at this time.
Two system tune up in suwanee. Arrived on site, found 2systems from 2002-03. checked filter and drain lines, checked electrical connections, amp draw, capacitance, checked outdoor coils and refrigerant pressures. Upstairs, found corroded evaporator coil, potentially leaking refrigerant, found dirty blower assembly, over amping motor, and bad capacitor, unit has only one form of water safty, gas drip T is not up to code, weak flame sensor,and ductwork in attic is r6 and customer is loosing thermal value in unconditioned area. Outdoor unit is low on R22 refrigerant, with motors drawing higher than normal amp and condenser coil is dirty. Main level, outdoor unit had tripped breaker due to over amping compressor, unit is low on r22, fan motor is over amping as well, capacitor is weak and leaking oil, and contactor is burned and pitted. Indoor, customer wanted quote to install thermostat, found unit without aux drain pan and has no form of water safty, blower motor assembly is dirty, blower
One system cooling maintenance in suwanee. Arrived on site, checked filter and cleared drain line, checked electrical connections, amp draw, capacitance, cleaned outdoor coil and checked refrigerant pressures. Recommend installing uv purifier to improve indoor air quality as well as keeping the system clear of organic growth. Also recommend installing surge protector to furnace to protect electrical systems. Unit is operating normally at this time
2 system ac maintenance in Suwanee. Cleared drain lines. Checked mechanical and electrical components recommended overflow protection switch for both units. Recommend replacing both aprilaire 610 filters. Found weak dual capacitor(40/10) on upstairs condenser recommend replacement. Systems are operating at this time.
Presold repair in suwanee Ga. Installed surge protection to ac condenser and furnace. Also replaced weak blower motor controller. System cooling at this time.
No cool in suwanee, arrived on site, found main system not cooling and outdoor unit not functioning. Found where a rodent had chewed through a wire at one of the float switches. Repaired the wire and outdoor unit came on immediately. Tested system, no other issues present at this time
2 system tune up in Suwanee. Changed filters. Checked mechanical and electrical components. Found upstairs system to have a dirty blower wheel, weak blower capacitor, bad draft inducer motor, rusted evaporator coil, pitted contactor and malfunctioning thermostat. Due to the age and condition of the system I recommend upgrading to a newer and more efficient system at this time. Recommend overflow protection switch for downstairs furnace. Recommend surge protection for outdoor unit. Downstairs system is operating normally at this time.
Ac maintenance in Suwanee. Tested operation of 1 system. All components tested within normal manufacturing spec. Discovered dirty blower wheel and ductwork. System needs a compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the system. Discovered no drain line water safety in attic. Thermostats are worn out but still functional. Installed compressor saver on system. System cooling at this time.
Ac diagnosis in Suwanee, Georgia. Main level system. Condenser fan motor was not turning on due to bad capacitor. Replaced capacitor and installed hard start kit and system is cooling at this time. Two year parts and labor warranty on capacitor and hard start kit.
Tune up suwanee. Completed tune up on 2 systems both furnaces and downstairs ac are 24 years old. Upstairs is 17. Both have very dirty blower wheels and weak capacitors and no secondary water safety switch. Both coils rusted and corroded. Temp difference is good pressures are good fan motors outside running at high amps. Systems are very old and not cooling very efficiently. Should replace for lower power bills
Arrived on site, found no air flow coming from vents due to the evaporator coil being a solid block of ice. Unit is from 2003 and most likely low on refrigerant. Due to age of equipment and condition, I highly recommend replacing equipment. Unit is not operational at this time
Free consultation for new A/C system carrier Suwanee
Ac maintenance in Suwanee. Tested operation of 1 system. All components tested within normal manufacturing spec. Systems do not have drain line water safeties in the attic to help prevent flooding in the case of common drain line clogs. Systems need compressor savers to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the systems. Recommend installing g surge protection for systems. Systems cooling at this time.
2 system cooling maintenance in suwannee, arrived on site, changed filter and cleared drain line, checked electrical connections, amp draw, capacitance, cleaned outdoor coil and checked refrigerant pressures. Found main level R22 refrigerant pressures low with a corroded evaporator coil recommend installing surge protector to furnace and outdoor unit, as well as hard start kit to compressor. Upstairs, found corroded evaporator coil, recommend installing surge protector and compressor assist kit. Recommend installing UV purifier and stage one filter to improve indoor air quality and eliminate organic growth inside the system. At this time due to age and condition of equipment, I recommend replacing upstairs evaporator coil and main level evaporator coil and condenser.
Tune up suwanee. Completed tune up on 2 16 year old systems. Both systems with very rusted coils and clean blower wheels. Both indoor capacitor are weak. System has no back up water safety. Temp difference is good. Outdoor pressures are good. Downstairs system has weak capacitor both contactors are good.
Two system cooling maintenance in suwannee. Arrived on site, changed filter and cleared drain line, checked electrical connections, amp draw, capacitance, cleaned outdoor coil and checked refrigerant pressures. Recommended installing surge protector to each indoor unit to protect electrical systems. Upstairs recommend replacing plenum and relocation of large duct coming out of the top so that it is more conductive for air flow. Both systems are operating normally at this time.
Call back in suwannee. Arrived on site, found panel that goes inside the evaporator coil beside the unit, put it back in, also taped up some insulation that had come loose from supply plenum. Unit is operating normally at this time.
Inspection suwanee. Completed inspection found both furnaces with improper gas line ran and drain line not away from the house and line insulation falling off and crumbling. Took care of all issues. Systems cooling at this time.
Tune up suwanee. Completed 3 system tune up. All 4 years old with clean blowers and coils. Changed customer provided filters. Cleared drain lines. Pressures and temp difference are good. All electrical components good. Air flow for all 3 are high. Recommend adding return and supply for each. Left estimate.