Family Owned HVAC Repair Company
Comfort Control has been the reliable, 5 Star rated HVAC company for heating & AC repair service in Suwanee, GA and the surrounding areas since 1992.
Read our reviews from Suwanee, GA to see how our craftsmanship, professional trained technicians and customer service has provided complete satisfaction for our heating and air conditioning services.
Air Conditioner & Heating System FAQs
There could be a number of reasons why hot air is coming out of your vents instead of cool air in your home near Suwanee, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Clogged Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home, not allowing cool air to circulate.
- Low Refrigerant Levels - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Broken - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
You should have an HVAC maintenance service done on your unit twice a year in Suwanee, GA. This service is also known as a tune-up on your heating and cooling system, as the technicians performing the service will clean, inspect and correct any problems your system may be having.
The cost to repair your home air conditioning system near Suwanee, GA really depends on what is wrong with your system. On average, AC repairs cost about $350 as most of them are pretty minor in scope. Larger repairs, however, can cost as much as $2,000 for complicated leak repairs or compressor replacements.
To determine whether your indoor air is clean in your home near Suwanee, GA, the experts at Comfort Control can help. We will perform an Air Quality Evaluation to test your home’s indoor air quality. We will use a high-sensitivity laser particle scanner to measure the particulate parts per million in the air and then analyze the results. To schedule your evaluation, contact us today!
for Suwanee, GA
VICTOR - Suwanee, GA
Response from Comfort Control Heating & Air:
Victor, so glad we were able to provide you with 5-Star HVAC Service!
Professional, kind and helpful
Abby - Suwanee, GA
He was extremely helpful. Will definitely use this company again!!
James - Suwanee, GA
The representative was very thorough and explained everything we needed to know. Very happy with the service.
Outstanding Customer Service
VICTOR - Suwanee, GA
Outstanding Performance “Again”
Glenn - Suwanee, GA
Once again Comfort Control H/A out performed our expectations. The entire experience from the initial inspection and recommendations done by “Jeff” to the tear out and install performed by “Gavin” and “Ronnie” was painless and transparent. We were kept informed every step of the way.
Carol - Suwanee, GA
I appreciate Jordan being honest on what he thought we should do! He seems quite knowledgeable!
James - Suwanee, GA
Techs from North Atlanta Plumbing were very courteous and proficient. Was a pleasure to have them in our home
Jason - Suwanee, GA
Jason - Suwanee, GA
Extremely professional and helpful
Did a great job!
Shonagh - Suwanee, GA
Arrived within the time window. Was polite and efficient!
The Tech was a good lid
TOM - Suwanee, GA
Not happy with my 5 week old system needing service already but liked the tech Alex. Had to change my Saturday schedule for the day to accommodate the service call
As always, Comfort Control provides dependable, GREAT SERVICE
WILLIAM - Suwanee, GA
"Ricky" expediently, expertly, and cordially took care of us, performing our annual Spring AC maintenance [late...OUR FAULT!] yesterday, 07-08-21. Purchase and installation of this Amana Heating/AC system from Comfort Control -- way back in 2011 -- was one of the absolute best home improvement investments we've ever made.
Brian - Suwanee, GA
Shelliy - Suwanee, GA
Came out fast, professional and fixed the problem
ELLY - Suwanee, GA
The technician who visited my home was very thorough and professional, while explaining the issues with my hvac, and my options. Jordan did an excellent job.
Air Conditioner not working. Clogged drain lines. Cleared drains, air conditioner blowing cold air near mcginnis ferry road
AC Repair on 12 year old 4 ton Carrier system. Air conditioning not cooling properly, clean drain lines, diagnose and repair.
Air Conditioning Repair Suwanee. Air conditioner not blowing cold air, technician came out and determined bad capacitor. Replace capacitor HVAC system is operating smoothly near suwanee creek.
A/c diagnostic in Suwanee. Found indoor unit running, outdoor unit fan was running but not the compressor. Condenser has a bad secondary motor controller. Replaced capacitor system is cooling at this time. Blower wheel is clean, evaporator coil is clean, drain line is flushed.
Maintenance in 2 Goodman gas furnaces and AC. Both systems working at normal operations. Replaced downstairs condensate pump and hose. Recommended blower motor cleanings for both furnaces. Replaced 1 16x25x1 filter upstairs. Downstairs media filter needs to be replaced.
Ac service in Suwannee. Discovered system frozen and leaking refrigerant from evaporator coil. Due to age and condition replacement is HIGHLY recommended. Homeowner chose to refill refrigerant with ABSOLUTELY NO WARRANTY. Refilled refrigerant. System cooling temporary.
Ac service in Suwannee. Discovered old pvc Union gasket failing to seal properly. Removed Union and installed coupling with glue.
No cool Suwannee. Customer called about inadequate cooling. Found a leaking evaporator coil. Very dirty blower wheel. And weak capacitor. Due to leaking coil and cost of repairs I recommend a new system. Changed filter. Compressor is still good. Outdoor capacitor is within range. Pressures are low due to leak.
Replaced upstairs and downstairs evaporator coils
Maintenance Suwannee. Did a leak search on both evaporator coils. Did not find any leaks. Blower wheels are clean. Changed filters. Drain lines are clear. No cracks in the heat exchangers. Outdoor capacitors are both within range. Pressures on both systems are within range. Systems are cooling at this time.
Tune up Suwannee. Did a leak search on both evaporator coils. Did not find any leaks. Upstairs systems capacitor was weak. I changed the capacitor. Main level units capacitor is within range. Both blower wheels are clean. Filters are clean. Drain lines are clear. No cracks in either heat exchanger. Pressures on both systems are within range. One of the outdoor capacitors was weak. I changed that capacitor. The other capacitor was within range. Both systems are cooling at this time.
No cool in Suwanee. System is cooling at this time, customer said unit is icing up From time to time. Blower wheel is a little bit dusty, evaporator coil is rusty and clean but no leaks was found, also did fine the filter was pressed against blower housing, ( filter is inside furnace no filter rack ). Outdoor unit refrigerant pressures are good and all electrical components are working properly at this time.
Tune up Suwannee. Did a leak search on evaporator coil. Did not find any leaks. Changed filter. Indoor unit capacitor is very weak. Recommend replacing the capacitor. Drain line is clear. Blower wheel is clean. Outdoor capacitor is within range. Pressures are within range. System is cooling/heating at this time.
Ac service In Suwanee. Discovered furnace control board and blower motor failing intermittently, compressor over heated and weak outdoor capacitor. Cooled compressor down and system running at this time. Furnace is original to home and ac and evaporator coil is 11 years old. Due to age of system furnace replacement at minimum is HIGHLY recommended.
Ac service in Suwannee. Discovered melted wires in outdoor unit. Heavily corroded evaporator coil. Homeowner has chosen to replace ac and coil. Collected deposit and got system running until we replace.
Maintenance Suwannee. Did a leak search on the evaporator coil. Did not find any leaks. Indoor capacitor is within range. Blower wheel is clean. Drain line is clear. No cracks in heat exchanger. Compressor is good. Outdoor capacitor is within range. Pressures on the system are within range. System is cooling at this time.
Ac service in Suwannee. Homeowner discovered drain line disconnected and re attached. I added taped to secure it better to sewer vent. Homeowner has water damage to ceiling and would like a call about compensation
Evaporator Coil changeout
Start capacitor had failed, reading OL MFD. burnt wiring and loose terminal on start capacitor. This had made the run capacitor fail, reading 3/45 MFD on herm. Replaced run capacitor and took off start capacitor.
Maintenance Suwannee. Did a leak check on both evaporator coils. Did not find any leaks. Both heat exchangers good no cracks found in them. Blower wheels on both units are clean. Filters are clean. Cleared drain lines. Outdoor capacitors are within range. Pressures on both systems are within range. Both systems cooling at this time.
A/c call back in Suwanee. System is cooling at this time, did another leak search on the condenser unit and evaporator coil. Didnâ€™t find any leaks at this time if problem continues we need to do a nitrogen test.
Ac service in Suwannee. Discovered clogged filter and bedroom vents mostly closed. Changed filter and opened vents. System operation normal at this time but coil is very rusted.
A/c diagnostic in Suwanee. System is cooling at this time. Customer wants me to check out unit and make sure everything is good. Found condenser missing a bit of refrigerant. Customer changed filter, blower wheel looks good, evaporator coil is clean. Customer changed out condensate pump tubing.
Ac service in Suwannee. Homeowner concern with high humidity in home. Discovered blower speed way too high for ac system. Adjusted blower speed system cooling at this time.
Ac maintenance in Suwannee. Tested operation of 1 system cleaned outdoor unit and tested all components. System operation normal at this time. Recommend surge protection for system.