Comfort Control has been the reliable company for value cooling and heating in Suwanee, GA and the surrounding areas since 1992.
Read our reviews from Suwanee, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
There could be a number of reasons why hot air is coming out of your vents instead of cool air in your home near Suwanee, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Clogged Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home, not allowing cool air to circulate.
- Low Refrigerant Levels - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Broken - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
You should have an HVAC maintenance service done on your unit twice a year in Suwanee, GA. This service is also known as a tune-up on your heating and cooling system, as the technicians performing the service will clean, inspect and correct any problems your system may be having.
The cost to repair your home air conditioning system near Suwanee, GA really depends on what is wrong with your system. On average, AC repairs cost about $350 as most of them are pretty minor in scope. Larger repairs, however, can cost as much as $2,000 for complicated leak repairs or compressor replacements.
To determine whether your indoor air is clean in your home near Suwanee, GA, the experts at Comfort Control can help. We will perform an Air Quality Evaluation to test your home’s indoor air quality. We will use a high-sensitivity laser particle scanner to measure the particulate parts per million in the air and then analyze the results. To schedule your evaluation, contact us today!
for Suwanee, GA
Denise - Suwanee, GA
LETICIA - Suwanee, GA
WILLIAM - Suwanee, GA
JAY - Suwanee, GA
STEVE - Suwanee, GA
We have used Comfort Control for many years and all their technicians are very professional and courteous.
Rich Johnson was great and very knowledgeable!
Steve - Suwanee, GA
JOHN - Suwanee, GA
Usual Great Service
Joe - Suwanee, GA
Great customer service
Brian - Suwanee, GA
Kiran - Suwanee, GA
BRANDY - Suwanee, GA
MARY - Suwanee, GA
Prices have become extremely high. Every time they come for biannual service they request to add on high priced ticket items.
Lawrence - Suwanee, GA
Very helpful and friendly.
MIKE - Suwanee, GA
Very easy to communicate with and great service.
Fall system tune up
MIKE - Suwanee, GA
Notification of service was great, technician was punctual. Technician was knowledgeable and friendly, he completed his tasks and left our home clean.
DANNY - Suwanee, GA
Great service !
Carol - Suwanee, GA
It was good!
JAY - Suwanee, GA
Caroline - Suwanee, GA
We had Vu Tran as our technician. He knows the stuff very well and is very informative. No doubt an excellent service!
Nice Young man
DAVID - Suwanee, GA
Vu was great to interact with. Very knowledgeable. He used a very methodical approach to solve the problem.
Mahendra - Suwanee, GA
By provided excellent work & service.
ERIK - Suwanee, GA
Reese did a great job and was very personable
Friendly, Quick, Knowledgeable
Angelia - Suwanee, GA
Our tech Jon was great. He was friendly, wore a mask and shoe covers, diagnosed the problem quickly and got it repaired for us.
Marcia - Suwanee, GA
Vu provides outstanding service. He is a very thorough technician. He found several issues that needed to be corrected in my new house. I can always depend on him to look out for the homeowner’s best interest. I have been a Comfort Control customer for over 20 years in my old house and look forward to having them service the units in my new home.
Reliable service on time
CARL - Suwanee, GA
Heating issues in Suwanee Georgia Furnace is not staying lit on the pilot due to a bad gas valve would Recommend replacing the heating system due to age .
Customer reported that furnace was not heating. Turned system on and could not get system to duplicate the problem. Changed filter. Performed maintenance. System is heating at this time. Due to age of furnace, recommend upgrading it to a more reliable and efficient furnace.
Furnace maintenance in Suwanee, Georgia. One system. Changed filter. Tested mechanical and electrical components. Found blower capacitor to be weak (20uf), recommend repair. It is a zoned system with no bypass damper, recommend installing bypass damper to relieve static pressure when not all zones are operating. System is heating at this time
No heat for main system in Suwannee. Check and find Heating furnace fail due to fail control board. Need to replace gas furnace control board. Customer declined repair and will call home warranty for repair. System not operating at this time. Suggest to upgrade system due to age and cost of repair.
Heating maintenance suwanee. Completed maintenance on 2 systems. Upstairs is working good with no issues. Clean inside. Changed filter. System does not have secondary water safety device or properly ran gas pipe sediment trap to avoid debris getting into gas valve in furnace. Insulation in attic is also below beams in some part and needs insulation blown in to avoid heat loss in cooler weather. Downstairs system is old and has over heating inducer motor and very dirty blower wheel. System also has no water safety attached. Furnace downstairs needs to be replaced for better efficiency.
No heat in suwannee. Arrived on site, found inducer fan motor failed some time last night. Quoted to replace. Customer declined repair. System is not operational at this time.
Complete tune up special in Suwannee. Check and find 22 year old Armstrong gas furnace pressure port clogged. Clear port and system operating at this time. Find gas furnace operating with worn ignition, high temperature furnace and can over heat, rusted evaporator coil and bio growth on plenum, flue pipe not code and no water protection. Customer want to wait to upgrade system.
Call back in suwannee. Arrived on site, found float switch on condensation drain line tripped, reset switch and cleared drain line for maintenance customer. Tested unit. Unit is operating normally at this time.
No heat suwanee. Completed diagnostic found wires for gas valve loose. System turned on after tightening wires. Static pressure test indicates bypass damper not opening like it should causing furnace to trip on high limit. Inducer motor is failing. Evap coil is rusted all over. System has no back up water safety. System needs to be replaced due to cost of repair and efficiency of current system.
Furnace maintenance in Suwanee, Georgia. One system. Changed media filters and water panel. Set humidifier to 45 percent humidity. Tested static pressure and found it to be good. Tested mechanical and electrical components, all in good shape. Found mold inside supply plenum, recommend pureairx air purifier to kill mold, bacteria, germs and viruses for improved air quality. System has no surge protection, recommend installing surge protection to protect equipment from power surges. System is heating normal at this time. Thank you so much for your buisiness today! If you were happy with your service, please take the time to leave us a five star review on Google! Be sure to leave my name, Reece Wilson, in the review! And again, thank you for choosing Comfort Control for your heating and cooling needs!
Water leak call back in suwannee. Arrived on site, found screw in heat exchanger assembly loose causing water to flow into pan, made sure there was no damages to the system, tightened assembly and sealed. Tested system. Unit is operating normally at this time.
Heating maintenance suwanee. Completed maintenance on 2 systems. Main floor is heating good but has no water safety attached in case of clog. Also is older and not running very efficiently. Upstairs is running good with clean blower and coil. Has both forms of water safety. Changed both filters. Air flow is restricted upstairs due to multiple junctions being used. Suggest redoing ductwork to allow all rooms to come off of plenum to allow optimum airflow.
Two system heat maintenance in suwannee. Arrived on site, changed filters and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Recommended installing secondary water safty switch on upstairs system and surge protection to both systems. Both systems are operating normally at this time.
Furnace maintenance in Suwanee, Georgia. Two systems. Did not change filters, customer prefers to use more breathable filters and filters had recently been changed. Tested mechanical and electrical components, found no pressing concerns. Systems are 15 years old and may not last much longer though. Tested static pressure. Found downstairs system to have high static pressure , recommend installing additional 10â€ return and 8â€ supply for system. Recommend installing surge protection for furnaces to protect them from power surges. Systems are heating normal at this time.
Water leak in suwannee. Found no water leak, paint is pealing, but no wet spot in ceiling. No issues present at this time
Furnace tune up in Suwanee, Georgia. Two systems. Changed filters. Tested mechanical and electrical components. Found downstairs system with rusty, corroded evaporator coil that is likely to leak refrigerant. Downstairs blower capacitor is weak (7.5uf). Downstairs water safety is code compliant but has no backup overflow protection switch to help protect furnace from potential water damage and to serve as a backup to primary water safety. Downstairs gas line is not up to code. Downstairs flame safety sensor is going weak. Static pressure on upstairs system is very high due to insufficient ductwork and restrictive filter setup as well. Recommend installing additional 10â€ return for system. Due to age and condition of downstairs system, recommend upgrading system to a more reliable and more efficient system. Ductwork on both systems is not of r8 insulation rating and therefore not up to todayâ€™s codes. Recommend ductwork renovation on both systems to improve efficiency and bring syst
Service call in Suwannee. System making noise. Find filter door cover loose and causing noise. Tape and seal door cover to help Reduce noise. Find system under size in return duct causing high static pressure for return air. Need additional 10â€ return to upstairs room to help reduce pressure and noise. Suggest inline water protection for system in attic and surge protection. Suggest air purifier system to help keep system clean and improve air quality. Warranty service call back from last service call. No charge to customer
Heating maintenance suwanee. Completed maintenance on 2 new systems. Both very clean inside. Changed filters. Both heating properly. All safety switches working. Suggest installing electro static filters for better filtration and keeping systems and home cleaner longer.
HVAC inspection in Suwanee. System operation normal. No Y2 is needed at thermostat for the system to run using both stages.
No cool upstairs system in Suwannee, warranty call back on tech. No charge to customer. Find drain pan flow switch was tripped, reset switch and ac unit operating at this time. Upstairs ac unit also 23 year old operating but in poor conditions, worn parts, missing starter kit and compressor run stress with high amp. Suggest to upgrade system.
Two system heat maintenance in suwannee. Arrived on site, changed filters and humidifier pad. Cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Recommend installing surge protector for each unit. Both systems are operating normally at this time.
Furnace maintenance in Suwanee, Georgia. Two systems. Changed downstairs filter customer provided. Tested mechanical and electrical components, all in good shape. Recommend surge protection to protect equipment from power surges. Recommend uv light systems to kill mold, bacteria, germs and viruses for improved air quality. Systems are heating normal at this time.
Furnace maintenance in Suwanee, Georgia. Two systems. Changed upstairs filter. Tested mechanical and electrical components. Found upstairs furnace with a very weak blower capacitor (7.5uf). Found upstairs with no water safety whatsoever which is not up to code. Strongly recommend installing water safety to protect ceiling from potential water damage. Found upstairs blower wheel to be dirty. Found upstairs evaporator coil to be rusty and corroded, and therefore likely to leak. Due to age and condition of upstairs system, recommend upgrading system to a more reliable, more efficient system. Downstairs system has no water safety and is therefore not up to code either. Recommend installing water safety to prevent water from flooding into finished area of basement. Systems are heating at this time.
Tune up 1 system in Suwannee/ found multiple issues on 26 year old furnace/ customer wants to upgrade the system/ also found hot water heater leaking / customer wants to replace 40 gallon gas heater / furnace and coil will have to come out to replace hot water heater / must be 40 gallon short / and must go back on stand /