Comfort Control has been the reliable company for value cooling and heating in Suwanee, GA and the surrounding areas since 1992.
Read our reviews from Suwanee, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
There could be a number of reasons why hot air is coming out of your vents instead of cool air in your home near Suwanee, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Clogged Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home, not allowing cool air to circulate.
- Low Refrigerant Levels - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Broken - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
You should have an HVAC maintenance service done on your unit twice a year in Suwanee, GA. This service is also known as a tune-up on your heating and cooling system, as the technicians performing the service will clean, inspect and correct any problems your system may be having.
The cost to repair your home air conditioning system near Suwanee, GA really depends on what is wrong with your system. On average, AC repairs cost about $350 as most of them are pretty minor in scope. Larger repairs, however, can cost as much as $2,000 for complicated leak repairs or compressor replacements.
To determine whether your indoor air is clean in your home near Suwanee, GA, the experts at Comfort Control can help. We will perform an Air Quality Evaluation to test your home’s indoor air quality. We will use a high-sensitivity laser particle scanner to measure the particulate parts per million in the air and then analyze the results. To schedule your evaluation, contact us today!
for Suwanee, GA
Mike - Suwanee, GA
Great Service/Excellent Help in solving the problem.
JOLIE - Suwanee, GA
Very knowledgeable in work.
David - Suwanee, GA
They are professionals and did the job right the first time.
BOB - Suwanee, GA
JOLIE - Suwanee, GA
JOLIE - Suwanee, GA
VIMAL - Suwanee, GA
We were happy with Vu’s service
Great service with smile
VIMAL - Suwanee, GA
We had excellent experience with Vu Tran he was good in explaining the problem and quick in fixing it we were Very happy with service.
DONALD - Suwanee, GA
Glenn - Suwanee, GA
Garrett. Followed up on a service call that took place this morning to go over our options of replacing our heater. He was very pleasant, knowledgeable, understanding and helpful. We were able to collectively agree on our selection. I am very satisfied
Great evaluation of the problem
Glenn - Suwanee, GA
Vu Tran demonstrated his knowledge and ability to evaluate our problem. We are very pleased with the service.
Josh - Suwanee, GA
LEVORN - Suwanee, GA
DAVID - Suwanee, GA
Denise - Suwanee, GA
LETICIA - Suwanee, GA
WILLIAM - Suwanee, GA
JAY - Suwanee, GA
STEVE - Suwanee, GA
We have used Comfort Control for many years and all their technicians are very professional and courteous.
Rich Johnson was great and very knowledgeable!
Steve - Suwanee, GA
JOHN - Suwanee, GA
Usual Great Service
Joe - Suwanee, GA
Great customer service
Brian - Suwanee, GA
Kiran - Suwanee, GA
BRANDY - Suwanee, GA
Heating tune up suwanee. Completed tune up on 3 year old system. System heating and cooling properly. All safety switches working. All heating components working and clean. All electrical components inside and out working good. Blower and coil clean. Pressures are good. Recommend compressor saver outside to lesson load on compressor and allow it to leave longer. Recommend air quality treatments installed to better clean air inside house
One system maintenance in Suwanee Georgia. Changed filter. Checked mechanical and electrical components. Found weak blower capacitor and replaced it under warranty. Cleared drain line. Chemically washed condenser coil. Found dirty blower wheel. Found no water safety devices. Static pressure is high due to undersized return. Recommend surge protection and air purifier to kill bacteria, germs and viruses. System is operating normally at this time.
Complete heating maintenance in Suwannee. Did not change filter, check safety and operation. Find 5 year old Lennox furnace operating with minor ware in flame sensor and need to keep check. Find system have no inline water protection and not surge protection. Suggest safety for equipment and suggest air purifier to improve air quality and prevent molding. System operating at this time.
Three system cooling maintenance in suwannee. Arrived on site, changed filters and cleared drain lines, checked electrical connections, amp draw, and capacitance cleared outside coils and checked pressures found upstairs system without secondary water safty switch, recommend installing to protect electrical systems from water damage. Also recommend installing surge protection to each piece of equipment to protect electrical systems. Used the last of filtration media for PureAirX. Installed overflow switch and supplied customer with (1 box(4 uses)) PureAirX 16x25x1 media. All units are operating normally at this time.
No heat in Suwannee. Check and find new installed system not operating properly. Check and reset system setting. Test both zone and system operating at this time. Warranty service call. No charge to customer. Need to schedule for spring visit to check on system for cooling.
Furnace not heating in Suwanee, Georgia. Main level system. Found beckett tubing for condensate pump clogged causing water safety switch to trip. Unclogged tubing and system is heating at this time.
No heat in suwannee. Arrived on site, customer complaint of main level furnace not heating, found bad flame sensor. While in attic I also found that the upstairs system had a bad flame sensor and a warn ignitor. I replaced both ignitors and cleaned both flame sensors until we can get them in stock and come back to replace them (eta, mid following week). Got both systems operational again for the moment. Went through the check list, also found a weak capacitor on both systems. Should read 5mfd, out of spec reading (3.7mfd main level) and (3.5mfd upstairs) recommend replacing both. Both systems are without secondary water safty to protect unit
Complete 2 tune up special inspection in Suwannee. Check both 7 year old heating furnace. Check safety and operations. Did not change filter. Find both furnace in attic operating with in manufacturer spec. Suggest surge protection for both system, suggest air purifier system to improve air quality and prevent Bio growth.
Heating tune up in Suwanee, Georgia. Three systems. Changed filters. Tested mechanical and electrical components. Found upstairs system with dirty blower wheel. Recommend blower wheel pull and clean. Found upstairs gas line not up to code, it does not have a drip leg installed. Recommend installing drip leg on upstairs gas line to bring it up to code. Recommend installing overflow protection switches for downstairs and basement systems. Found basement main electrical switch with electrical pitting present, recommend repair. Systems are heating at this time.
Tune up suwanee. Completed tune up. Found blower and coil clean. Flame sensor and ignitor clean. Inducer motor is running high amps and could burn out. Capacitor for blower is very weak and needs to be replaced. Combustion is good. Air flow is good. Coil does have rust and corrosion on it indicating copper thinning. System has no secondary water safety to protect furnace from water damage or surge protection or indoor air quality.
Free consultation Suwanee Georgia 30024
Heat pump not heating in suwanee, Georgia. Down stairs system . Tested system and found , dirty blower wheel . Blower motor leaking oil. Found heat kit to be broken and bypassed. Found zone board with no dedicated transformer. Found evaporator coil very rusted , corroded, and actively leaking. Found mold inside system. Found dual capacitor to be weak (35/5). Found main electrical switch with electrical pitting present. Found evidence of system being grossly overcharged. Found compressor shutting itself off. Reduced refrigerant pressures to more appropriate levels and Compressor is still shutting itself off. Due to age and condition of system along with cost of repair, recommend upgrading system to a more reliable, more efficient system. Sending consultant out for a free consultation
Service call in Suwannee. Customer stated that master bedroom not comfortable due to lack of air flow. Check new carrier system. Adjust air flow to increase air flow to master bedroom. Reduce air flow to office. Complete combustion calibration service to increase temperature and efficiency of furnace. System operating with in manufacturer spec. Warranty service from install. Suggest zoning to improve control of comfort
Complete 3 heating tune up special inspection in Suwannee. Change filter, check safety and operations. Find both Lennox 9 year old furnace operating with under-fire furnace and not calibrated properly. Find downstairs furnace missing in-line water protection, flue pipe not code. Find basement Airhandler Trane 15 year operating with worn main electrical switch for heating kit. Find upstairs ac unit operating with weak condenser capacitor. Find main unit missing starter kit. Find basement heatpump missing starter kit. Find upstairs air distribution box have bio growth, suggest UV KIT to help kill and prevent molding. Sign 3 comfort control club care. Complete 3 heat maintenance. Install 2 PureAireX UV kit kill bio growth and prevent molding. Complete 2 Lennox combustion calibration service to improve temperature and efficiency. Replace basement Airhandler blower capacitor and main electrical switch. Install u starter kit for downstairs ac unit and basement heatpump unit. Replace upstai
Furnace maintenance in Suwanee, Georgia. Two systems. Changed upstairs pureairx filter pad. Tested mechanical and electrical components. Found upstairs furnace with weak blower capacitor (7.5uf). Recommend repair. Neither system has surge protection installed, recommend installing surge protection to protect equipment from power surges installed surge protection for furnaces and condensers. Replaced main level blower capacitor, part was under warranty, labor was not. Systems are heating at this time.
No heat in Suwannee. Discovered furnace with bad blower motor. Furnace is 28 years old and replacement is highly recommended over repair. Need to call on Monday to schedule consultation. Homeowner wants to shop around
Service call sunroom in Suwannee. Replace Lennox mini split head control system. Test and system operating at this time. Customer have $50 off coupon.
Furnace tune up in Suwanee , Georgia. 1 system . Did not change filter . Cleared drain line . Tested mechanical and electrical components . Found weak blower capacitor, changed it under warranty. Found system with only one form of water protection , recommend installing overflow protection switch to help protect furnace from potential water damage and help to serve as a backup to primary water safety switch . System has no surge protection . Recommend installing surge protector to protect equipment from power surges . System is heating at this time .
Two system heat maintenance in suwannee. Arrived on site, changed filters and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found both systems without secondary water safty and main level with no water safty. Both systems are dated from 2000 and are showing signs of wear except for the upstairs outdoor unit and evaporator coil witch have been changed out. Unis have dirty blower assemblies and blower motor with bearings that are starting to leak. Both blower capacitors are reading low, inducer motors are over amping and flue pipe is improperly tied into to inducer assemblies. Recommended installing uv purifier to each system to eliminate organic growth in system and improve indoor air quality. Units are operating, however I recommend replacing equipment due to age and condition of units.
On system heat maintenance in suwannee. Arrived on site, changed filter and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found system without any form of water safty as well as a clogged filter. Blower motor assembly is dirty and should be pulled and cleaned. Recommended installing uv purifier as well as surge protector for outdoor unit and furnace. Unit is operating, however due to age and condition I recommend replacing the furnace.
Service call in Suwannee. Replace fail limited sensor. Complete combustion calibration service to help reduce heat to prevent overheating of furnace and reducing CO level. Replace filter 16x25x5 media. Reduce fan speed for both heating and cooling system to help reduce high static pressure to .98 w.câ€. Give customer estimate to install additional duct system to help reduce pressure. Give customer estimate to replace gas heating furnace with smaller furnace to match with 2.5 Ton cooling system. Give customer estimate to install air purifier system. Give customer estimate to install humidifier to help improve comfort. System operating at this time.
No heat main level in Suwannee. Check and find 2 year old Lennox gas furnace overheating and causing limited switch to fail. Find furnace over size for duct system. Need to replace limit switch, change filter, and need to do combustion calibration service. Need to order parts and come back to complete work. System off at this time.
No heat on sunroom mini split system. Warranty service call back from yesterday. Check and find Lennox mini split head screen display not operating but system operating. Check and find mini split head control board fail and not operating properly. Need to replace board. Need to check with manufacturer for cost and availability. Need to call customer on Monday with prices.
No heat on mini split in sunroom in Suwannee. Check and find Lennox split unit. Check and find remote Tstat batteries fail. Replace batteries customer provided. Turn on system and test. Find head supply 110 degrees and line temp and 150 degrees. Check control and operations. Find system operating with manufacturer spec. System operating at this time.
Heating maintenance suwanee. Completed maintenance on 2 systems. Both furnaces 17 years old with very dirty blower wheels and very weak capacitor. Both evap coils very rusted and corrosive and likely to leak. Both systems missing secondary water safety devices to protect furnace and home from water damage. Insulation in attic is good. Air flow on both systems are good. Left new filters for customer. Ac system running on r22. Recommend replacing both systems due to age and efficiency. Systems heating at this time.