Comfort Control has been the reliable company for value cooling and heating in Sugar Hill, GA and the surrounding areas since 1992.
Read our reviews from Sugar Hill, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
for Sugar Hill, GA
COLLEEN - Sugar Hill, GA
The technician was professional and took the time to explain the issues. My unit was fixed and cooling in less than an hour.
GARY - Sugar Hill, GA
Fast, professional, quality and reasonable!
ROUMEN - Sugar Hill, GA
ERIC - Sugar Hill, GA
The technician was on time and professional. Offered a few options to fix my problem and other services that the company offered.
Issac - Sugar Hill, GA
Our technician was Chris Southerland. He was extremely professional and respectful of our home. He worked quickly to identify the problem and repaired it just as quickly. Thanks to Chris we have a nice cool home again!!!!
LARRY - Sugar Hill, GA
Reece was very professional, cared for our needs, and very informative about what we needed to have done.
Casey - Sugar Hill, GA
Very professional and friendly!
GEORGE - Sugar Hill, GA
Well done, timely but forgot to put on mask.
Khrishna - Sugar Hill, GA
Emil - Sugar Hill, GA
Great Customer Service!
MIKE - Sugar Hill, GA
Miranda - Sugar Hill, GA
Jon did an excellent job! He was professional and answered all questions. Very informative
Gary - Sugar Hill, GA
Knowledgeable & Polite
Glenn - Sugar Hill, GA
Vu did and great job And protected me and my family with ppp.
KEVIN - Sugar Hill, GA
Vu is highly knowledgeable and very customer service focused. We are very comfortable when he is in our house and we trust him fully. He is an excellent representative of Comfort Control !
Emil - Sugar Hill, GA
Great customer service
Gina - Sugar Hill, GA
Christian was very professional and knowledgeable. He is a great asset to your company.
Andrea - Sugar Hill, GA
He was great, he explained everything. Thank you
Patrick - Sugar Hill, GA
Chris was fast and efficient!!! He was done sooner than expected, which was great for us. Thank you
Patrick - Sugar Hill, GA
Austin - Sugar Hill, GA
CHINIQUA - Sugar Hill, GA
Mark was courteous and took the time to explain each step of the process and the impact of the items he found during his inspection of my system.
MARY - Sugar Hill, GA
Alixandra - Sugar Hill, GA
Great experience! I enjoy comfort control. I have always had professional and kind technicians.
MELISSA - Sugar Hill, GA
Heating maintenance in sugar hill, Georgia. Completed heating maintenance at sugar hill animal hospital. Checked heating integrity. Changed air filters . Checked heating elements. Checked safety/ performance. â€¢Flex gas line running into the gas furnace . Took picture . Model N8MSN0701716A . Would highly recommend being hard pipe for safety and code . â€¢System #3 has a very dirty air movement system and causing the system to work harder and causing the air quality to drop . Would highly recommend a deep chemical wash on the blower air movement system . System isnâ€™t wired for heat on the mother board would highly recommend wiring up . â€¢Furnace 5 . Has water stains in the overflow pan . Would highly recommend water safety. Flex gas line needs to be hard piped into the furnace for code and safety. Also the heats not wired up for this system on the mother board would highly recommend.
Boarding room AC system is down due to the compressor on a thermal overload . Would highly recommend having a compressor saver on the system also on the data plate they are recommended to have due to our humidity in Georgia . Also systems are due for a maintenance program... outside coils are getting dirty would also encourage a maintenance program to keep the warranty valid with the manufacture and keep the systems at speck levels . Animal hospital is going with signing up for the maintenance and going with adding the compressor saver start assist to the machine that feeds the boarding room . Office will call and schedule first maintenance visit . After installing the compressor saver the inrush amps are at specks and system is now operating. Thank you 🙂 .
Evaporator coil replacement in sugar hill. System found with leaking evaporator coil, replaced evaporator coil and adjusted charge. System operating and cooling.
Heating tune up sugar hill. Completed 2 system tune up. Upstairs is new with 3 forms of water safety. Clean blower whee and evap coil. Changed filter. All heating elements working properly. Thermostat is good. Insulation in attic is low. Suggest blowing in insulation to avoid heat loss in heating seasons. Downstairs system is 22 years old. Heating fine with slightly dirty blower wheel. Changed filter. Evap coil has little to no corrosion. Heating elements are working properly. System will need to be replaced soon if cost of repairs out weigh advantages of replacing.
Ac service in sugar hill. Discovered failed secondary controller, clogged filter, and system does not have drain line water safety. Replaced filter and secondary controller. System cooling at this time
No cool in sugar hill. Arrived on site, found system turned off by customer per CSR request. Turned system on and checked both zones. Found no issues. Checked refrigerant pressures. No other issues present at this time.
No coolin sugar hill. Arrived on site to system not cooling due to compressor not functioning. Found bad capacitor, replaced with new and signed customer up for maintenance. System is operating normally at this time.
Full system installed with 10 inch return in bedroom in sugar hill
Ac service sugar hill. Completed diagnostic. Found evap coil leaking r22 Freon. Also found inducer assembly failed due to clog in port. Both need to be replaced. Due to age of system recommend replacing system for better efficiency.
New hvac system sugar hill
Ac repair in sugar hill. System completely frozen over to the outdoor unit. Cannot properly diagnose while system has any ice. Need to let system thaw out and return tomorrow for repair. System has airflow which points to system being low on refrigerant which means there is a leak. System 14 years old and uses R22 which manufacturing has been banned by the epa. Recommend replacement over repair
Ac repair in Sugar Hill, Georgia. No cool. Tested system and found the following issues: evaporator coil is very rusty and corroded. Blower wheel is very dirty. Blower capacitor is weak (5uf). Dual capacitor is not functional causing compressor to not turn on (35/5uf). System is operating at high pressure due to dirty condenser coil. Due to age and condition of system, recommend upgrading system to a more reliable and more efficient system. Chemically washed condenser coil and replaced dual capacitor. System is cooling at this time.
Ac tune up in Sugar Hill, Georgia. For upstairs system. Found system not cooling due to clogged drain line. Cleared drain line. Tested mechanical and electrical components, found capacitor to be weak (70/5 uf) recommend repair. System is cooling at this time.
Ac repair in sugar hill This isn't the optimal way to make the correction. Tie the 10" duct into the back of the furnace and repair the 12" to reconnect it in the side of the furnace.
Ac tune up in Sugar Hill, Georgia for two systems. Left behind replacement filters. Tested mechanical and electrical components. Found downstairs blower wheel to be dirty. Found downstairs evaporator coil to be very rusty and corroded and likely to leak. Found upstairs blower capacitor to be weak (5uf). Found downstairs dual capacitor to be weak (35/5uf). Found upstairs dual capacitor to be weak (40/5uf). Found both drain lines to be clogged, cleared both drain lines using nitrogen and water. Both systems have primary water safety and are therefore up to code but have no backup. Recommend overflow protection switches to help protect furnaces from potential water damage and to serve as a backup to primary water safety. Neither system has a hard start kit installed. Recommend installing hard start kits to reduce load on compressors so they start smoother, run smoother and therefore last longer. Neither system has surge protection, recommend adding on to protect equipment from power surge
Ac service sugar hill. Completed diagnostic. Found blower wheel very dirty. Blower motor failing. Capacitor failing. And housing warped. System needs to be replaced. Having Jim come out to give quote.
No cool on carrier system in Sugar hill. Check and find 24 year old carrier air conditioning unit tripped breaker due to worn compressor. Compressor operating with high amp and not starting up properly and making noise. Contactor worn and pitted and fan motor not balanced and worn. Find evaporator coil in attic badly rusted and missing water protection. Filter dirty. Blower motor dirty and worn. Customer need consultation visit. System operating at this time but not reliable.
Ac maintenance sugar hill. Completed one system maintenance on 4 year old Amana system. Evap coil is clean. No corrosion or freezing. Blower wheel has slight layer of dust build up. Suggest installing electro static filter to better filter air and keep system and home cleaner longer. System only has one form of water safety. Suggest adding secondary wet switch for extra water safety. Changed filter. Drain line is clear. Outdoor unit has good pressures. Washed off coil. Amps on motors are good. Capacitor is good. System would benefit from having hard start kit installed to take load off compressor during start up and allow compressor to live longer. System would also benefit from having surge protector installed to protect all electrical components in outdoor unit which is most vulnerable to power to power surges.
Dehumidifier install sugar hill. Installed new dehumidifier in basement with new condensate pump and drain pan with float switch. Tested pump and system. All running good. System has 5 year pets warranty and 1 year labor with aprilaire and 2 year parts and labor with comfort control. System is running at this time.
AC maintenance Buford. Completed first maintenance on new system. Changed electro static filter. Blower wheel is clean. Coil is good. All safetyâ€™s work. Drain line is clear. All wires installed correctly. Outdoor unit has good pressures and clean working electrical components. All wires installed correctly and tight. System cooling properly at this time.
Completed consultation on new dehumidifier. Will return tomorrow to install.
Arrived on site. Found unit not running. No power going into unit, breaker not tripped. Found broken furnace switch. Replaced and unit started operating normally. Tested unit. Operating within manufacturer specs at this time.
No cool upstairs zone. Everything working properly at this time. Issue is most likely the damper but hard to pinpoint problem when everything is working. Homeowner does not want any repairs at this time. Signed up for maintenance membership
Internal drain pan cracked on old system. Recommend replacement over repair due to costs. Need to schedule consultation with garret for replacement options
No cool. Found high voltage fuse popped. Replaced fuse provided by customer. Found blower wheel to be dirty. Found weak capacitor. Recommend replacing capacitor, installing hard start kit, installing surge protection and pulling and cleaning blower wheel. Replaced filter.System is cooling at this time.