Comfort Control has been the reliable company for value cooling and heating in Sugar Hill, GA and the surrounding areas since 1992.
Read our reviews from Sugar Hill, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
for Sugar Hill, GA
Jon gave great service, he was professional and personable
CHARLIE - Sugar Hill, GA
Very knowledgeable and great customer care.
Adam - Sugar Hill, GA
Gary - Sugar Hill, GA
Great service. Awesome price.
Emil - Sugar Hill, GA
Very knowledgeable. Professional!
Great service. Awesome price.
Emil - Sugar Hill, GA
Very knowledgeable, professional.
Samantha - Sugar Hill, GA
Knowledgeable and Helpful
Samantha - Sugar Hill, GA
Took time to explain
Good dependable service
KEVIN - Sugar Hill, GA
As usual, Vu does a thorough job with a strong attention to detail. He is courteous and knowledgeable. He is a great representative of your company.
Same Day Diagnostics
JUAN - Sugar Hill, GA
Jordan arrived in a prompt and courteous fashion to accurately diagnose my heating problem. He quickly ordered the Warranty part and had me back up and running within 48 hours of the initial service call. I have enjoyed Comfort Control's Elite Series products for the last 7 years, and look forward to many more years of reliable service and support.
Prompt and Great Service
ARLENE - Sugar Hill, GA
Love an early appointment, prompt arrival by the technician, inspection thorough, and smooth. Thank you.
AWESOME TECHS & HIGHLY RECOMMENDED
Ivan - Sugar Hill, GA
Today 11/12/202, I had the pleasure of meeting 2 gentlemen from Comfort Control Heating & Air . Jordan was the service tech that showed up to service the unit. He was very professional and knowledgeable . Jordan recommended that we upgrade to a newer unit since my old unit uses R-22 which has already been phased out. I agreed. So then he advised his dispatcher and had Garrett come out to give me a quote. He was very professional and suggested a couple of options that would fit into my budget . He then made a call to his dispatch and set up an appointment for them to come out the next day and do the complete install . I was very happy and my wife was too . I cannot thank them for their service to our community and an AWESOME group of highly reputable team . Thank You Tom! You have AWESOME personnel working for you .
MAURICE - Sugar Hill, GA
This is the second time Jon has serviced my HVAC. He is very accommodating and answers any question I may have, even if they are not directly related to the current service visit. All the techs have been great.
STEVE - Sugar Hill, GA
Good job Reece. I will see you in the spring for air conditioning maintenance. Thanks steve Underwood.
MARY - Sugar Hill, GA
Very nice yet professional. Told us options for possible repairs, but was not pushy.
James is great!
Shannon - Sugar Hill, GA
COLLEEN - Sugar Hill, GA
The technician was professional and took the time to explain the issues. My unit was fixed and cooling in less than an hour.
GARY - Sugar Hill, GA
Fast, professional, quality and reasonable!
ROUMEN - Sugar Hill, GA
ERIC - Sugar Hill, GA
The technician was on time and professional. Offered a few options to fix my problem and other services that the company offered.
Issac - Sugar Hill, GA
Our technician was Chris Southerland. He was extremely professional and respectful of our home. He worked quickly to identify the problem and repaired it just as quickly. Thanks to Chris we have a nice cool home again!!!!
LARRY - Sugar Hill, GA
Reece was very professional, cared for our needs, and very informative about what we needed to have done.
Casey - Sugar Hill, GA
Very professional and friendly!
GEORGE - Sugar Hill, GA
Well done, timely but forgot to put on mask.
Khrishna - Sugar Hill, GA
Emil - Sugar Hill, GA
Found bad icomfort thermostat. Replaced under full warranty. System is operating at this time.
Replaced inducer motor per customer. System came on and heating as of now.
Complete 2 Heating Tune up inspection special in Sugar Hill. Find upstairs 6 year old Rheem gas furnace operating with in manufacturer spec, find system missing water protection in attic, poor duct system with leakage. Poor conditions evaporator coil and incorrect set up. Insulation in attic poor. Find downstairs Lennox gas furnace 9 year old operating with dirty blower assembly, furnace flame sensor and ignition worn. System missing in-line water protection.
No heat sugar hill. Completed diagnostic. Found high limit switch failing intermittently. Needs to be replaced. System has slightly dirty blower wheel good capacitor and combustion. Air flow is good. Filter is good. Evap coil is very clean. Flame sensor and ignitor are good. System has no back up water safety device to protect furnace from water damage. System would also benefit from having UV light treatment installed to kill bacteria and viruses in air that could cause harm to residents.
Heating repair in Sugar Hill. Discovered a failed thermostat. Inspected rest of the system and discovered big blower motor controller, weak flame safety, extremely worn ignition, dirty ducts, dirty blower wheel, and no drain line water safety to help prevent flooding of furnace and ceiling in the case of common drain line clogs. Replaced thermostat and signed up for maintenance membership. Homeowners going to discuss repair options and get back to us. System operation normal at this time.
No heat sugar hill. Completed diagnostic found inducer assembly failed. Locked up rotor. Need to replace. Custer approves. Ordered part will be delivered to office then put on schedule to replace. Blower is very dirty. Flame sensor is worn. Evap coil is covered in rust in corrosion. System is 19 years old. Customer is selling home and just wants inducer done for now.
Furnace Tune up in sugar hill , Georgia. Two systems . Checked all electrical and mechanical components. Upstairs system does not have pan water safety switch. Recommend installing to prevent water overflow on to ceiling. Recommend surge protection to protect equipment from power surges. Recommend pureairx air purifier. To kill bacteria, germs and viruses for improved air quality. Systems are heating at this time.
Complete 2 tune up special inspection in sugar hill. Check safety and operations. Change filter 2 16x25x1 and 1 16x20x1. Find both upstairs and downstairs 15 year old Goodman gas furnace operating with worn flame sensor and ignition, bad capacitor reading and dirty blower assembly. Find evaporator coil rusted in attic. Find downstairs furnace inducer assembly making noise due to worn motor bearing. Find basement 9 year old Airhandler operating with in manufacturer spec. Find heatpump unit operating with weak capacitor, pitted contactor and missing starter kit. Find both ac unit 15 year old operating with weak capacitor, worn/pitted contactor and cracking point. Find basement disconnect box damage.
Water leak sugar hill. Customer is selling home. Inspector noted drain line outside sloping up. Needed that fixed. Repairs drain line. System draining properly at this time.
Two system maintenance in Sugar Hill. Arrived on site, changed filters and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found left side system without secondary water safty switch. I also recommend installing surge protecton to each piece of equipment as well as compressor assist kits to each outdoor unit to assist compressor on startup. Both units are operating normally at this time
Heating maintenance in Sugar Hill. Tested operation of the system. Both systems with dirty blower wheels. Downstairs system has duct leakage at supply plenum. Both systems need duct cleanings. Both outdoor units need coil cleanings. Downstairs system would Benefit from filter grill as changing the filter With current configuration is difficult. Downstairs system inducer showing signs of bearing failure. Upstairs has no drain line water safety. Systems operational at this time. Homeowner declined repairs for now as he is selling the house
No heat Buford. Completed diagnostic. Gas was turned off to furnace on arrival with no red tag. Turned on gas. Furnace came on and satisfied twice with no issues. Thermostat is good. Blower is clean. Capacitor is good. Combustion is good. Evap coil is clean. System has no back up water safety to protect furnace from water damage. Air flow is good. Coil and condenser are 12 years old. Contactor and capacitor are looking worn but still running within manufacturing spec. Signed customer on maintenance plan. System heating at this time.
No heat sugar hill. Completed diagnostic. Found main floor furnace with faulty control board. Not sending power to high limit switch intermittently. Turning system on and off. Needs to be replaced. Both blower wheels are dirty and need to be cleaned. Both capacitors are weak and need to be replaced. Both of these will cause extra stress on motor and cause them to fail prematurely. Main floor system has restricted air flow in return side. Need to add return to main floor system. Upstairs evap coil is very corroded which can lead to leaks and system freezing up which can lead to total failure. Recommend replacing coil. Upstairs system is very moldy inside and out. Recommend UV light inhibitors to both systems to sanatize air and keep residents healthy. Due to age and cost of repairs recommend replacing both systems to better efficiency systems.
Hvac tune up in Sugar Hill, Georgia. One system. Changed filter. Tested mechanical and electrical components. Found system with pitting on main electrical switch, recommend repair. System has no hard start kit, recommend adding on to reduce load on compressor so it starts smoother, runs smoother, and therefore lasts longer. Ductwork is not of r8 insulation rating, is not properly secured and is falling apart, recommend ductwork renovation. System is operating at this time.
Complete heating maintenance in Sugar Hill. Check and find 2 Year old Trane furnace operating with in manufacturer spec. Check safety and operations. Find duct system R-6 not code in attic and need to be R-8 rated. Duct system also under size for operations causing high static pressure. Find system missing in-line water protection in attic. Surge surge protection and air purifier system. Give customer options. Install surge protection for furnace in attic.
Heating repair in Sugar Hill. Discovered failed blower motor with extremely dirty and unbalanced blower wheel. Ducts need cleaning. There is no for of water safety on system to help prevent flooding in the case of common drain line clogs or system freeze ups. Signs of organic growth. System is 33 years old and replacement is HIGHLY recommended over any repair. Jim scheduled for consultation today
zero rez completed job and billed us; we never marked invoice complete
Heating repair in Sugar Hill. Discovered failed ignition. Replaced ignition and system heating at this time. Recommend routine maintenance. System is 18 years old. Typical lifespan for a system is 10-15years. System may need to be replaced in the near future
Heating repair in Sugar Hill. Discovered system with failed gas control module and failed ignition. Also discovered system blower wheel dirty and motor with signs of wear. Combustion chamber is rusted and likely to leak carbon monoxide. Gas line is not up to code as flexible pipe is ran through cabinet which vibration can cause leaks. Due to age and condition of system replacement is HIGHLY Recommended.
Heat pump replacement in sugar hill Georgia.
Free consultation for heat pump system sugar hill Georgia 30518
No heat in sugar hill, arrived on site, found outdoor unit not coming on due to bad compressor, will need to replace equipment. Unit is not operational at this time
Warranty sugar hill. Completed diagnostic. Found system low on refrigerant causing heat pump to freeze over. Did thorough leak test couldnâ€™t find any leaks. Filled system with 3 pounds refrigerant. System running at this time.
No heat sugar hill. Completed diagnostic. Found bad thermostat. Replaced thermostat. System heating properly.
Installed 10 inch return to the bedroom in Sugar Hill Georgia . Ran new 10â€ R8 duct run . Sealed boot . Completed heating maintenance. Filter location has changed . Took pictures of the new filter location and filter size is 20x20x1 . System is heating at this time.