Comfort Control has been the reliable company for value cooling and heating in Sugar Hill, GA and the surrounding areas since 1992.
Read our reviews from Sugar Hill, GA to see how our craftsmanship, professional training and customer service has provided complete satisfaction for our heating and air conditioning services.
for Sugar Hill, GA
Good dependable service
KEVIN - Sugar Hill, GA
As usual, Vu does a thorough job with a strong attention to detail. He is courteous and knowledgeable. He is a great representative of your company.
Same Day Diagnostics
JUAN - Sugar Hill, GA
Jordan arrived in a prompt and courteous fashion to accurately diagnose my heating problem. He quickly ordered the Warranty part and had me back up and running within 48 hours of the initial service call. I have enjoyed Comfort Control's Elite Series products for the last 7 years, and look forward to many more years of reliable service and support.
Prompt and Great Service
ARLENE - Sugar Hill, GA
Love an early appointment, prompt arrival by the technician, inspection thorough, and smooth. Thank you.
AWESOME TECHS & HIGHLY RECOMMENDED
Ivan - Sugar Hill, GA
Today 11/12/202, I had the pleasure of meeting 2 gentlemen from Comfort Control Heating & Air . Jordan was the service tech that showed up to service the unit. He was very professional and knowledgeable . Jordan recommended that we upgrade to a newer unit since my old unit uses R-22 which has already been phased out. I agreed. So then he advised his dispatcher and had Garrett come out to give me a quote. He was very professional and suggested a couple of options that would fit into my budget . He then made a call to his dispatch and set up an appointment for them to come out the next day and do the complete install . I was very happy and my wife was too . I cannot thank them for their service to our community and an AWESOME group of highly reputable team . Thank You Tom! You have AWESOME personnel working for you .
MAURICE - Sugar Hill, GA
This is the second time Jon has serviced my HVAC. He is very accommodating and answers any question I may have, even if they are not directly related to the current service visit. All the techs have been great.
STEVE - Sugar Hill, GA
Good job Reece. I will see you in the spring for air conditioning maintenance. Thanks steve Underwood.
MARY - Sugar Hill, GA
Very nice yet professional. Told us options for possible repairs, but was not pushy.
James is great!
Shannon - Sugar Hill, GA
COLLEEN - Sugar Hill, GA
The technician was professional and took the time to explain the issues. My unit was fixed and cooling in less than an hour.
GARY - Sugar Hill, GA
Fast, professional, quality and reasonable!
ROUMEN - Sugar Hill, GA
ERIC - Sugar Hill, GA
The technician was on time and professional. Offered a few options to fix my problem and other services that the company offered.
Issac - Sugar Hill, GA
Our technician was Chris Southerland. He was extremely professional and respectful of our home. He worked quickly to identify the problem and repaired it just as quickly. Thanks to Chris we have a nice cool home again!!!!
LARRY - Sugar Hill, GA
Reece was very professional, cared for our needs, and very informative about what we needed to have done.
Casey - Sugar Hill, GA
Very professional and friendly!
GEORGE - Sugar Hill, GA
Well done, timely but forgot to put on mask.
Khrishna - Sugar Hill, GA
Emil - Sugar Hill, GA
Great Customer Service!
MIKE - Sugar Hill, GA
Miranda - Sugar Hill, GA
Jon did an excellent job! He was professional and answered all questions. Very informative
Gary - Sugar Hill, GA
Knowledgeable & Polite
Glenn - Sugar Hill, GA
Vu did and great job And protected me and my family with ppp.
KEVIN - Sugar Hill, GA
Vu is highly knowledgeable and very customer service focused. We are very comfortable when he is in our house and we trust him fully. He is an excellent representative of Comfort Control !
Emil - Sugar Hill, GA
Great customer service
Gina - Sugar Hill, GA
Christian was very professional and knowledgeable. He is a great asset to your company.
No heat in sugar hill. Arrived on site, customer complaint of System not keeping up with living room area of split level house, recommend moving thermostat to middle level instead of upstairs in hallway. Customer has home warranty company coming out to look at the unit, customer declined repair at this time, but may want to do it by the end of month. System is operating normally at this time.
Furnace not heating in Sugar Hill, Georgia. Found bad flame safety sensor. Found worn igniter. Found worn inducer motor. Found gas line not up to code with flexible gas line inside furnace. System has no water safety whatsoever. Due to age and condition of system, recommend upgrading system to a more reliable and more efficient system. Sending consultant out. Will apply service fee towards cost of installation.
No heating on main level in flowerybranch/ found filter stopped up/ check system and found that ignition was bad and flame sensor/ also found duct work leaking in areas under home / found that evaporate coil is leaking back into furnace/ coil is in cased in supply plintum/ ac is 24 years old / recommend upgrading to a new ac and coil
Two system heat maintenance in Buford. Arrived on site changed filter and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found both units from 2006, both have dirty blower assemblies, no water safty, gas valves and inducer motors are pulling higher than normal amp, and evaporator coils should be cleaned. Upstairs also has a warn ignitor and flame sensor. Both units are operating at this time
Sign 2 comfort control maintenance plan and complete heating maintenance in Sugar Hill. Check both 22 year old carrier gas filter, change filter, check safety and operations. Find upstairs furnace operating with high CO level due to in-complete combustion and under-fire, find inducer assembly making noise and worn blower assembly. Find downstairs furnace operating with worn ignition. Customer want to wait on upgrading system. Customer want repair for today visit. Replace downstairs ignition and complete combustion calibration service for upstairs furnace.
Free consultation sugar hill Georgia 30518 new hvac system
Free consultation sugar hill Georgia heat pump for basement
3 system maintenance in Sugarhill basement system is in bad shape / 19 years old / heat strip burnt and removed/ blower motor is bad / customer said he would call for estimate to replace / offered to set up for him and he declined
1 system maintenance/ customer wants to be served in may please 1 system maintenance
Furnace maintenance in Sugar Hill, Georgia. One system. Changed filter. Tested mechanical and electrical components, found no issues. System is heating at this time.
AC service in Sugar Hill
Heating repair in sugar hill. Replace upstairs blower motor under full warranty from 10yrs parts and labor. Ran for 30 mins without issue
One system heat maintenance in Buford. Arrived on site, changed filter and checked heat strips. Checked electrical connections, amp draw and capacitance. System is operating normally at this time
Heat repair in Sugar Hill. Upstairs Icomfort thermostat showing code for high limit open. Tested all safeties. All safeties tested normal. Reset power to the system. Turn furnace on and it started heating. Tested operation. Furnace operation tested normal. Ran system for 15 mins and the blower motor stopped working. Order board and motor under parts warranty from Lennox Alpharetta
Heating maintenance in Sugar Hill. Tested operation of 1 furnace. All components tested within normal manufacturing spec. Attic insulation is low and needs to be addressed for proper efficiency. System heating at this time
Free consultation sugar hill Georgia hvac replacement
Ac repair in Sugar hill. Discovered system completely empty on charge. Evaporator coil rusty, contactor burnt, wires melted. System is 20 year old and needs to be replaced along with electrical whip. System is not functional at this time
Heating maintenance in Suagr Hill. Tested operation of 1 furnace. Al components tested within normal manufacturing spec. System and home would greatly benefit from ultraviolet light system to combat organic and viral growth in system and throughout the home. System heating at this time.
Complete 2 heating maintenance in Sugar Hill. Change both filter, check safety and operations. Replace both weak flame sensor for 2 Lennox gas furnace. Find furnace operating within manufacturer spec. Suggest in-line water protection for system in attic and surge protection for both system. Both 10 year old gas furnace operating at this time.
Heating maintenance sugar hill. Completed maintenance on 2 systems. Main and upstairs zoned system is 6 years old and basement is one year old and heating properly. Everything is installed correctly. Filters are good. Everything clean on inside of systems. All safety switches work. Zoning works upstairs. Recommend UV lights in systems to take care of bacteria and viruses inside home.
Heating maintenance sugar hill. Completed one system maintenance on 8 year old furnace. All heating elements clean and working. Blower is clean. Filter is good. All safety switches work. Gas line ran properly. System would benefit from having electro static filter installed to better filter air and keep system and house cleaner longer. As wel as UV light to kill any bacteria or viruses in air.
Furnace maintenance in Sugar Hill, Georgia. One system. Changed filter. Tested mechanical and electrical components, all in good shape. Recommend pureairx electronic filter to reduce static pressure and improve air quality. Recommend surge protection to protect equipment from power surges. System is heating at this time.
Two system heat maintenance in sugar hill. Arrived on site changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Recommend installing secondary water safty switch to each system and surge protection to protect electrical systems. Both units are operating normally at this time
Heating maintenance sugar hill. Completed maintenance on 4 year old furnace. Furnace is heating. Changed filter. System has only one form of water safety. UV light will need to be replaced in spring. All electrical components are good. Heating elements are good. No sign of rust or over heating.
Heating tune up sugar hill. Completed one system tune up. Found furnace heating properly. All heating components working and clean. All safety switches working. Zone board working with its own transformer. Gas pipe ran properly. Insulation is good. Filter is good.