The residents of Lawrenceville, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Lawrenceville, GA area.
There could be a number of things causing poor air quality in your home:
- Excessive Moisture - When humidity levels are too high, it can feel uncomfortable and hard to breathe.
- Products with VOCs - Volatile Organic Compounds, or VOCs, can be found in paints, cleansers and other household items. Limit your supply of products with VOCs, especially in spray form, to help lower contaminant levels inside.
- Pets - Dogs and cats create a lot of dander.
- Secondhand Tobacco Smoke
- Fireplaces and Chimneys
- Poor Ventilation
On average, you can expect to pay between $3,800 - $7,500 to replace the air conditioner in your Lawrenceville, GA home. This price depends on:
- The quality and energy efficiency of the unit you choose
- How big your house is
- If any ductwork need to be replaced
An AC tune up on your unit in Lawrenceville, GA involves many steps and checks performed, including but not limited to:
- Cleaning the filter and coils
- Checking and straightening coil fins
- Checking and clearing the condensate drain
- Checking the refrigerant levels, oils motors and belts
- Testing the thermostat
- Inspecting the entire unit
for Lawrenceville, GA
MIKE - Lawrenceville, GA
good job as usual. Great job Vu!
Highly professional attention from today's service technician!
ARNULFO - Lawrenceville, GA
Rawle - Lawrenceville, GA
Brian came promptly to my home and he gave me a courtesy call before he came. He had to diagnose where the source of the air flow to a certain vent in my basement . He methodically looked at what needed to be done giving the circumstances that particular vent is in a finished part with sheet rock. He had explained everything to me and showed me that he was unable to rectify the issue without cutting into the Sheet Rock. I decided to leave everything as is and my system still functioned well. Brian left his work site clean, he followed CDC guidance and he was polite. I would recommend Brian to provide service to anyone because his approach to rectifying a problem was through, methodical and with high quality.
ERIC - Lawrenceville, GA
Called on a Sunday morning of Labor Day weekend. Reece Wilson texted us and arrived in less time than what he estimated. Inspected all the units and diagnosed the issue. Explained everything he was doing and why. Had all the history of our system on his tablet from previous services. Thanks Reece for the great service. Highly recommend this service team !
Stuart - Lawrenceville, GA
Jon Fowler was on time for our service call and got a text with his picture attached and phone call saying he was on the way. He went through checking our two HVAC units and explained what heats doing and his recommendations all through the visit. He seemed very knowledgeable and polite. For COVID-19 compliance, he wore a mask and had put on boots as well I appreciate his help and knowledge.
Sarah - Lawrenceville, GA
Tom - Lawrenceville, GA
Reece was very helpful and went through ecobee set up
Sarah - Lawrenceville, GA
Very astute. Clear offered good alternatives. Pleasant manner
Mensah - Lawrenceville, GA
Detailed and knowledgeable
Rapid Service Response
Rawle - Lawrenceville, GA
Jon Fowler came out as an emergency service call and he was very much in line with the CDC Guidelines and wore shoes protection as he entered our home. He systematically checked everything to confirm that there weren’t any similar issues. He was able to identify the issue and quickly resolved the problem. Jon was very polite and courteous and I would highly recommend him.
Great installation of Daikin VRV 5 Ton System
Rawle - Lawrenceville, GA
Eric is part of Tom Kohberger crew of amazing, talented and awesome techs who came to my house to install an amazing Daikin VRV System with multiple Air Handlers.
KEVIN - Lawrenceville, GA
They kept me updated as to what time I should expect Chris. When he arrived he went straight to work and quickly figured out the problem and voila! We had cold air again! He didn't waste my time trying to talk me into "what else needs to be done to the system" as other companies have done in the past. He did ask about a maintenance service which I was going to sign up for anyway. So glad I went with this company.
Thanks for your service today, Reece!
Martha - Lawrenceville, GA
On the hottest day of the year, Reese came to our home and got us up and running in no time. Thank you for taking care of us Comfort Control. 😊
Chi - Lawrenceville, GA
Vu is a very nice and helpful. Highly recommended.
Very nice person
Evertt - Lawrenceville, GA
Very nice, professional and informative
STEPHANIE - Lawrenceville, GA
Mark was very knowledgeable and personable. He explained everything well.
MARGO - Lawrenceville, GA
Vu was excellent as always! He demonstrates and explains everything. He does the best for us and does not try to sell something we can’t afford!
Jessica - Lawrenceville, GA
Vu was friendly, timely, and professional. Would definitely recommend!
Rawle - Lawrenceville, GA
Abundant experience and knowledge for the equipment
Tandy - Lawrenceville, GA
He did a great job. Thank you Tandy kratzer
PEGGY - Lawrenceville, GA
I always relyon Comfort Control to take care of my AC/HC
Reece is great!
Dennis - Lawrenceville, GA
He always shows up within the arrival time stated, does a great job and explains things in a way that makes them easy to understand.
Michelle - Lawrenceville, GA
PAT - Lawrenceville, GA
I had excellent service for my maintenance check of my air conditioner. Vu Tran does a great job and does an excellent job in explaining things to me.
Willis - Lawrenceville, GA
Quick and professional....some confusion with the original dispatch. The person never scheduled the service....waited all day for a call from tech. Called back 1hr past dispatch. Second person took care of it.
Estimate for new compressor
Heating maintenance lawrenceville. Completed heating maintenance on 2 2 year old systems. Systems are coming on and heating properly. Combustion is good. Leaned inducer port. Changed filter. Blower whee is clean. System has no back water safety. Systems also have no IAQ equipment to clean and sterilize air. Attic has low insulation below beams. Needs insulation blown in to reduce heat loss and allow system to not run as long.
Completed a three system heating maintenance in Lawrenceville Georgia . Checked the heating elements. Heating integrity. Checked heating safety. Today was the prepaid visit . â€¢Main floor heating system . The Korbel plate is rusting and will eventually lead to cracking which will cause the furnace to short cycle and cause problems. Highly recommend re aligning the burners and adjusting the plate to prevent it from cracking . â€¢Basement system . Showing early signs of biological growth underneath the air coil . Would highly recommend putting a UV light in the system to prevent the biological growth from spreading and getting worse and decreasing air quality. Took video . â€¢Today were going to install the UV light system for the basement and do the burner alignment for the main floor system . Completed the repairs . Installed UV light and completed the alignment on the burner assembly.
Complete heating maintenance for Lennox 5 year old system in Lawernville. Change Aprilaire 610 filter, check operations and safety. Find furnace heating system operating with in manufacturer spec. No concern at this time.
Estimate for new system in Lawrenceville
Ac warranty in Lawrenceville. Found float on float switch stuck, fixed it and system is operating at this time.
Dental office is Lawrenceville Georgia is having HVAC problems . â€¢Unit is making a very loud noise and vibration took video . The fan motor is seizing up and over heating . Also the frame off this system is falling apart which is another reason with the vibration... would highly recommend a new system at this point due to age and conditions. Repair option would be to replace the fan motor . Gave options . â€¢Also found a ton of biological growth growing on the blower wheel took pictures. This is not good for the air quality nor for the equipment. Would either recommend replacing or pulling the wheel out and completing a deep chemical wash on the air movement system . â€¢Heat exchanger has cracks which is a huge safety issue Iâ€™m going to have to turn the gas off at this system . Wrote down cracked heat exchanger and turned gas off to the valve . â€¢Would highly suggest having a consultation for a new HVAC system . â€¢After installing the new fan motor the compressor was n
Remove and replace all existing and accessible flex from the upstairs system in Lawrenceville
One system heating maintenance Lawrenceville, arrived on site, changed filter and checked electrical connections, amp draw on motor as well as heat exchanger. Checked pressures for refrigerant circuit as well as electrical connections, amp draw, and capacitance on heat pump. Unit is operating normally at this time
Complete 2 furnace heating maintenance in Lawrenceville. Change 2 16x25x1 filter. Check operations and safety. Find both 26 year old Lennox furnace operating in poor conditions and overheating and intermittent shut off on high limits. Find both upstairs blower motor worn and leaking oil. Fin s blower wheel very dirty and blower motor not running at full speed. Find flame sensor weak, find air pressure sensor worn and not pulling in properly. Inducer assembly worn and furnace chamber rusting. Both furnace also operating with high CO level and not safe to operate per NCI Safety guide line. Downstairs flue pipe PVC, not code and need to be double wall flue pipe. Due to system conditions, furnace need to replace replace and not repair.
Ac repair in Lawrenceville, Georgia. Found system with bad thermostat. Replaced thermostat and system is cooling at this time. Found evaporator coil very rusty and corroded and therefore likely to leak. Found blower wheel to be dirty. Found dual capacitor to be weak. Customer used $50 coupon.
Basement is finished and had no way to trace that air duct . Family did not want to bypass that register and cap it off . So I left the register alone . Warranty today . Thank you .
Ac service lawrenceville. Completed diagnostic. Found system void of refrigerant. System is 24 years old with very dirty blower wheel and rusted evap coil. System running on r22. For better efficiency and financials system needs to be replaced to newer refrigerant. Having jim come out to give quote.
Replace Lennox manufacturer warranty compressor, with hard start kit and CCI plan. Per Jeff, flush line and replace line dryer. Pressure test and vacuum system to 500 micron level. Recharge system to manufacturer spec 8.5 lbs R410. Test and system operating at this time. Complete cooling pm check and change both filter.
Ac repair in lawrenceville. Replaced damper motor for downstairs. Tested and operation normal at this time.
No cool Lennox system in Lawrencevlle. Check and find upstairs 2 year old system with clogged system and inline water protection shut off ac unit. Flush drain for air conditioning unit. System operating at this time. Suggest hard start kit, CCI maintenance plan and surge protection for outdoor.
No cool upstairs Lennox system in Lawrenville. Check and find bad compressor. Need to replace warranty compressor under warranty but not labor
No cool in lawrenceville, arrived on site, customer states that upstairs kids rooms get hot. Suspect zoning issue. Thermostat is in Masterbedroom on opposite side of house. Checked electrical connections, amp draw and capacitance. Checked refrigerant pressures and state of system. Unit is operating normally at this time.
Ac repair in Lawrenceville, Georgia. System was not cooling because bad control board was not turning on blower motor. Control board needs replacement. Tested system and found no water safety and system is therefore not up to code. Recommend two forms of water safety to prevent water from being an issue in the garage from hvac system. System has no hard start kit, recommend adding on to take a load off of compressor so it starts smoother, runs smoother and therefore lasts longer. Recommend surge protection to protect equipment from power surges. Customer only wants to replace control board for now. Replaced control board, parts are under warranty. System is cooling at this time. Signed customer up for one system maintenance plan. Thank you so much for your business today! It is greatly appreciated! Its customers like you that keep us in business and keep our families taken care of! If you were happy with your service today and you wouldnt mind, please take a few minutes to give us a 5
Ac diagnostic in Lawrenceville, Georgia. Found system with leak in evaporator coil. System needs to be replaced. Sending consultant out for a consultation.
Ac repair in Lawrenceville, Georgia. Customer reported system was making a loud high pitched noise at upstairs condenser. Tested system. Found no issues other than a weak capacitor. Replaced capacitor and system is cooling normal at this time. Customer used $50 off coupon. Thank you so much for your business today! It is greatly appreciated! Its customers like you that keep us in business and keep our families taken care of! If you were happy with your service today and you wouldnt mind, please take a few minutes to give us a 5 star review on google! All you have to do is go to google.com and sign into your google account. From there, search for â€œComfort Control Heating and Airâ€. Click on â€œReviewsâ€. Write your review mentioning me, Reece Wilson and please be sure to leave 5 stars! Thank you so much and have a great day!
Water leak in Lawrenceville Arrived on site, found drain pan with water in it due to clogged drain line, cleared drain and tested system. Unit is operating normally at this time. No other issues present.
Sign 2 CCI plan and complete 2 cooling maintenance for both Lennox system in Lawrencevlle. Find both 6 year old system operating with low charge, needing hard start kit for both ac unit. Find both system missing in-line water protection for evaporator. Suggest surge protection for outdoor unit. Customer only want to recharge system for today visit. Both system operating at this time.
Ac repair in lawrenceville. Discovered system receiving too much voltage from main panel. Systems zone panel, and air handler control board is bad. Thereâ€™s is a huge hole in the return plenum which is pulling In attic air. The outdoor unit is new 410a but the indoor unit is and older R22 unit. The pan water safety is not wired in, the systems electrical wiring is hot to the touch which is cause for concern. The outdoor unit is not properly supported. The whole indoor unit, zone panel, and return plenum needs to be replaced.
Ac service lawrenceville. Completed replacement of condensate pump. Tested pump three times. Worked every time. System cooling at this time.