The residents of Lawrenceville, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Lawrenceville, GA area.
There could be a number of things causing poor air quality in your home:
- Excessive Moisture - When humidity levels are too high, it can feel uncomfortable and hard to breathe.
- Products with VOCs - Volatile Organic Compounds, or VOCs, can be found in paints, cleansers and other household items. Limit your supply of products with VOCs, especially in spray form, to help lower contaminant levels inside.
- Pets - Dogs and cats create a lot of dander.
- Secondhand Tobacco Smoke
- Fireplaces and Chimneys
- Poor Ventilation
On average, you can expect to pay between $3,800 - $7,500 to replace the air conditioner in your Lawrenceville, GA home. This price depends on:
- The quality and energy efficiency of the unit you choose
- How big your house is
- If any ductwork need to be replaced
An AC tune up on your unit in Lawrenceville, GA involves many steps and checks performed, including but not limited to:
- Cleaning the filter and coils
- Checking and straightening coil fins
- Checking and clearing the condensate drain
- Checking the refrigerant levels, oils motors and belts
- Testing the thermostat
- Inspecting the entire unit
Home air conditioning units typically last around 15 years in Lawrenceville, GA. Although, the lifespan of your home air conditioning unit can also depend on the type of air conditioner you have and how often you have it maintenanced. Regular maintenance ensures that your system runs smoothly all year round and that it has a longer service life. To learn more about getting your home air conditioning unit replaced or on a service plan, give us a call today.
A few ways to fix a central air conditioner that is not cooling in Lawrenceville, GA are:
- Adjust your thermostat to AUTO and COOL.
- Replace your air filters.
- Clean your condenser coils.
Resetting your thermostat and changing your air filters can be a simple solution to the problem. However, sometimes your air conditioner may not be cooling due to a bigger issue and will require the expertise of an HVAC technician to repair it. To get your central air conditioner repaired, call us today.
Some things that can happen if your Lawrenceville home air conditioning unit is not serviced on a regular basis include:
- Your energy bills will increase.
- Your air conditioning unit warranty may be voided.
- Your air conditioning unit will not last as long.
If your air conditioning unit is not serviced regularly, it can also break down more frequently, costing you more on repairs in the long run. To get your home air conditioning unit on a maintenance plan, contact us today.
for Lawrenceville, GA
JOE - Lawrenceville, GA
Knowledgeable and got the job done
Alex was great, he did an awesome job and I appreciate him coming on a Sunday.
Kirk - Lawrenceville, GA
Alex was great, he did an awesome job and I appreciate him coming on a Sunday.
Great service/Even greater technician
MAXINE - Lawrenceville, GA
Great technician (I think his name is Gavin); he was efficient, courteous, clearly knows his job well!)
Paula - Lawrenceville, GA
Great service, reasonable price
MARY - Lawrenceville, GA
Jeff was thorough and patient explaining the options available, even when he had to repeat once I got my husband on the phone.
AC was not cool
Bryan - Lawrenceville, GA
Service technician is very knowledgeable, friendly & explain to every questions regarding that customer had. Thank you
Great and Quick Service
TRUDI - Lawrenceville, GA
Chris was very helpful in diagnosing and correcting the problems to get the system cooling properly! tjn
Tech was professional
Willis - Lawrenceville, GA
KEVIN - Lawrenceville, GA
Ty Fisher was great!
Kevin - Lawrenceville, GA
My technician, Ty Fisher, was great! I hope that he is my technician going forward. Ty was clean, professional, and a pleasure to talk with. I was disappointed with my initial call to schedule service because the representative could not give me a definitive price on my routine maintenance that I was scheduling. Also, the day of my service I called the office to get an estimated time of arrival for my technician, and I was told that because I initially talked with the company’s answering service (many days prior) that a technician was not assigned for my appointment, and that I could be squeezed in on today’s calendar.
AL - Lawrenceville, GA
On time, quick to resolve, dependable and competatively/ priced. What else can you ask for.
Awsome customer service
MARIE - Lawrenceville, GA
The technicians were very professional and detailed.
Great Service As Always
SANDRA - Lawrenceville, GA
Friendly and professional and today Reese and Chris handled my maintenance.
Prince - Lawrenceville, GA
Very professional tech
JACK - Lawrenceville, GA
Outstanding Professional Service
SANDRA - Lawrenceville, GA
Chris was great! What I really appreciated was his product knowledge and the options he made me aware of. He is such a personable young man and his courtesy and professionalism are off the charts!
CHARLES - Lawrenceville, GA
Did fix everything well. Did know that we were elderly and isolating but stayed in our house too long and did not wear mask when he was in basement. Have paid bill through office but no receipt yet.
Rawle - Lawrenceville, GA
Reece came on time and he is very knowledgeable. He provided periodic maintenance service to our Daikin VRV with 5 Air Handlers. He provided valuable recommendations in which we will have done during the next visit. I would recommend Reece to provide service to everyone.
MIKE - Lawrenceville, GA
Jon did a fine job with the upgrade. Hoe I can continue to have him as my service tech.
Service was OK
FRANK - Lawrenceville, GA
Arrived early which was good. Didn't replace filters! Attached some pictures of furnace. Not sure which one?
Very thorough & informative
Mil - Lawrenceville, GA
Technician Brett Castell was very thorough, informative & professional. Would highly recommend to any one needing quality service, maintenance or repairs!
Top of the line service
GLEN - Lawrenceville, GA
Jordan serviced our 2 HVAC units. He took his time & was very thorough. He pointed out a few things that had wear - some good wait & a few that needed doing. An example, 1 problem calls for 2 items to be replaced; however, he said most of the time it is just 1 item that is the cause & recommended we replace just that one. Extremely pleased w/the work Jordon did & his professional demeanor.
Great service, awesome prices
WINSTON - Lawrenceville, GA
Ty, was very pleasant and knowledgeable. Like the updates and the review of the system. Will definitely use the company again in the fall for service
Toby - Lawrenceville, GA
Eric was very knowledgeable in the explanation of the unit. He installed everything as necessary. He explained the entire unit thoroughly.
Jordan an awesome and was very efficient!
HOWARD - Lawrenceville, GA
16x25x1 filter in attic was very dirty, replaced and superheat went down. System has a refrigerant leak on its interior coil, coil should be replaced for system to cool efficiently and properly. Quoted $2350 for coil of replacement is needed, B width 2.5 ton system.
Ac service in Lawrenceville. Discovered failed compressor tripping breaker. Homeowner has chosen to replace with 14 seer Goodman B cabinet ac and coil. Need to schedule. Paid in full.
No cool Lawrenceville. Outdoor system was turning on and freezing up immediately. Indoor system blower motor would not turn on. Getting adequate voltage from board to motor. Motor needs to be replaced.
A/c maintenance in Lawrenceville. 2 system in the attic. 1st unit is the downstairs. Filter was very dirty customer had flood sanded and redone, changed filter, blower wheel is good, evaporator coil is clean, flush drain line. System is cooling at this time. 2nd unit upstairs, filter was really dirty blower wheel is clean, evaporator coil is clean, flush drain line. System is cooling at this time.
Zone board for communicating Lennox needs replacement. Disabled zoning so home could cool until replacement. When replacement is scheduled we preferably need to do a heating maintenance on the system. Thank you for choosing comfort control!
Chemically cleaned coil, adjusted subcool, and masticked supply duct to bedroom. System is cooling properly at this time.
A/c diagnostic call back in Lawrenceville. Customer said outdoor unit wasnâ€™t turning ON customer turned off breaker and on and its working now. Refrigerant pressures are good. And all components are good.
Maintenance Suwannee. Checked the capacitors on the indoor units, all capacitors are within range. Checked all three evaporator coils for leaks, did not find any leaks. Cleared drain lines. Replaced filters. Blower wheels were clean. Outdoor capacitors are within range. All three system pressures are within range. All three systems are cooling at this time.
Ac tune up in Lawrenceville. Tested operation of 1 system. Discovered system leaking refrigerant from evaporator coil, pitted and corroded main electrical switch. Due to age of equipment, replacement is HIGHLY recommended.
A/c diagnostic in Lawrenceville. Unit is in the attic. 2 zone system. Indoor unit was on and working. All zones are open. Found condenser unit not turning ON system had a bad secondary motor controller. Replaced with new one. System is cooling at this time. Pressure are good.
A/c diagnostic in Lawrenceville. Found system not cooling. Outdoor unit was off but indoor unit fan motor was turning off and on constantly. Outdoor unit not getting low voltage. Replaced transformer. System is cooling at this time.
Changed out gas valve for Rheem water heater. Need to return to exchange warranty valve.
16 seer AC and â€œBâ€ width Coil 10 years parts warranty 10 year labor warranty Lifetime outdoor unit replacement compressor warranty Correct sediment trap Furnace is in great condition (would benefit with a blower wheel cleaning)
No cool lawrenceville. Completed diagnostic. Found outdoor capacitor dead on compressor side. Replaced under parts warranty. System cooling properly at this time.
Tune up lawrenceville. Checked both evap coils for leaks, did not find any leaks. Cleared both drain lines. Changed filters in indoor units. Blower wheels were clean. Pressures on both systems are within correct range. Capacitors were both within range. Both systems cooling at this time.
Drain line float switch tripped. Clogged drain line. Cleared drain line. Ran system for 10 min. System draining good with no clogging.
No cool lawrenceville. Checked evap coil for leaks, did not find any leaks. Pressures were within range. Checked indoor capacitor was dead, replaced indoor capacitor. Found outdoor capacitor was weak, replaced outdoor capacitor. Blower wheel was very dirty, cleaned blower wheel. No water safety on drain line. Checked outdoor motor and compressor amps, amperage was good.
Maintenance lawrenceville. Cleared drain lines. Filters were good left inside left new filters for customer to change later. Checked on condition of coil, good at this time. Checked capacitors on outdoor units, both are within range. Checked pressures, pressures on both units are within range. Systems are cooling at this time.
EZ TRAP shutoff switch tripped, reset and system began operating. (Warranty)
â€¢â€¢â€¢â€¢ UPSTAIRS - cleared drain line at union. Drain pan is clear. Float switch is working properly. Blower capacitor is reading 5.1/5 MFD across it. Blower wheel is clean. Replaced 16x25x1 filter. 2013 evaporator coil is currently not leaking. Ducts are sealed properly. â€¢â€¢â€¢â€¢ MAIN LEVEL - condensate pump is operating properly at this time. Float switch is shutting off the system when opened. Drain pan is clear. Slight leak on male fitting. Added sealant to prevent water buildup. ECM motor is operating properly, blower is very clean. New control board. 16x25x1 filter was recently replaced by customer. Blower motor is operating under the FLA. Coils were very dirty, cleaned.
Ac service in Lawrenceville. Discovered system with barely any R22 refrigerant in system. System is leaking from the indoor coil. Due to age of system and repair cost, replacement is HIGHLY recommended. Homeowners have chosen replacement of system. Waiting on pricing for 90% furnace before making decision between 80 and 90. Both exhaust options are available at this application. Deposit of $720 collected
Replaced 45/5 dual capacitor / 5 year warranty. Need to charge $242, customer wants to be billed.
Ac service in lawrenceville. Programmed furnace control board with shared date loader
16 seer 3 ton AC, Furnace and Coil 10 year parts warranty 10 year labor warranty Lifetime unit replacement compressor warranty Lifetime heat exchanger warranty
Rewire a defrost board.