AC Repair Experts in Johns Creek
Johns Creek, GA has turned to Comfort Control since 1992 for professional AC repairs, heating repairs, installations and maintenance. W are local too, so when the AC goes out in the Georgia summer, we can be the to repair your air conditioner and make your family comfortable again. Call Us for all of your heating and cooling repairs, we guarantee your satisfaction.
The national average for central air conditioning repair is between $50 and $100 for a service charge and $300 for both labor and parts. For required services, heating, ventilation, and air conditioning (HVAC) providers typically charge fixed prices. Your costs will be determined by whether the technician has to replace components or add refrigerant, the distance between you and the HVAC company, and the season (rates tend to be higher in the summer). As a rule, the older the unit, the more expensive a repair is likely to be.
Central air conditioners generally have a lifespan of 12 to 15 years. A central cooling unit's lifespan may be lowered if its capacity is not adequately matched to the cooling load of the residence. Oversized air conditioners "short-cycle," rapidly switching on and off, causing undue wear and tear on the compressor. The compressor, like the furnace heat exchanger, is the most expensive component in the system. A worn-out compressor in an out-of-warranty unit is frequently a compromise that necessitates upgrading to a newer, more energy-efficient air conditioner rather than fixing the present one.
If your air conditioner is not cooling when the system is turned on, you may have a clogged or obstructed condenser coil. Unfortunately, a wide range of clogging matter, including grass, mud, and other impurities, can make their way into this equipment. This can cause a major blockage and, as a result, a system breakdown.
Check the condenser and clear away any dirt to remedy the problem. This region may be cleaned by gently wiping away dirt and grime with a hose If you still are having problems with your air conditioner running but not cooling, it may be time to contact a specialist.
Check out these reviews and see how we deliver air conditioning and heating service that residents of Johns Creek, GA turn to us for again and again. All your Johns Creek neighbors cant be wrong.
for Johns Creek, GA
Narendra - Johns Creek, GA 30022
No difference before and after the service, same issue with the A/C cooling.
Ac repair in Johns Creek. Discovered failed main electrical switch on rooftop package unit. Replaced switch and repaired wires. System cooling at this time.
Ac repair in Cumming Ga. discovered system frozen. Thawed out over night. Discovered system low on charge. Performed leak search but could not detect leak. Recharge system. System spoiling at this time.
Complete new system inspection in John Creek. Check and find new Carrier package unit on rooftop operating with in manufacturer spec. No concern on unit. Suggest to upgrade thermostat, suggest CO detector for building, suggest pureAireX air purifier system.
Installed new Carrier Roof top unit.
Estimate for 4 ton heat pump package unit.
Performed cooling tune up checked electrical, mechanical components, changed filters, dusted electrical cabinets, chemical washed units. Found weak capacitors recommend to replace. Recommend surge protection for all units. Recommend start assist kits to both outdoor units. Recommend pureairx for indoor air quality. Systems are cooling at this time.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Installed APCO SI in supply plenum along with single UV to kill biological growth supply. Setup lead for CA to go out and give options for adding a system to the basement and replacing main system in house.
Completed heating maintenance. Replaced filter. Found supply section of the system full of biological growth. Recommend adding a air purifier to system to clean area and increase air quality in house. Schedule install for Tues 8-10. System should have a inline safety switch installed on drain in attic. System is heating good at this time and running at safe levels.
Complete 1 system a/c repair and preventative maintenance check. Systems very old and need to be replaced. No water safety on either system. Added 1lb r22 to downstairs system
Found system low on r410a and frozen up. De-iced System. Found leak at king valve. Adjusted valve and replaced cap. Recharged system. System is cooling at this time. Unit has an assured warranty, office needs to contact Goodman to collect payment.
Completed 3 system furnace repair and preventative maintenance check. Main level and basement systems. The main level system for the front of the building was found to have a blower motor which was making a whining noise. Also, the basement heat pump had a burnt and pitted contactor.
Furnace repair. Checked and failed due to cracked ignition and a bad flame sensor. Replaced both parts under extended warranty with labor but no parts. Repaired furnace ignition and flame sensor, system operating at this time. Completed combustion calibration. Sign up 1 Comfort Club Membership and complete heating preventative maintenance check.
Installed 6" supply in the bedroom.
Here are the options to replace the Condenser and Coil. Good option is Standard change-out similar to what you have. Better option is a upgrade efficiency condenser. Going from a 14 seer to a 16 seer. Best option is the 2 stage condenser. Starts at 16 seer full capacity but will increase in efficiency when only in half capacity.
Found leak in the evaporator coil. Will call back tomorrow with options to repair and replace.
2 system a/c repair, preventative maintenance, and Comfort Club Membership renewal. Replaced filters, cleared drains and cleaned a/c coils. Found a rusty coil but did not detect a leak. Added 1 lb to the upstairs system and 7 lbs to the downstairs system with leak a seal. Both systems are charged with 10-degree subcooling per manufacture chart and cooling normally at this time
Found the system out of charge. Discovered a leak at the king valve for the suction line. Tightened valve. Believe this is from the cold weather freezing the gasket and thawing. No other leaks discovered. Checked evaporator coil and line set. Condenser holds 16.75 lbs of 410a. Quotesdd the customer for both the refridgerant as well as the trip and diagnostic charge. The customer wants to discuss reimbursement with warranty company before paying for refrigerant.
Complete 3 a/c preventative maintenance check. Found main system operating with pitted and burnt main electrical switch, weak capacitor and missing additional water protection for the drain line. Find basement new Trane system operating normally. Find guess room system operating normally. Suggest customer repair main system but customer denied repair suggestion at this time. All 3 system cooling at his time but the main system is not reliable.Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for spring and summer weather.
Heating repair: no heat main floor system zone. Found no signal from the thermostat to the system. Bypass thermostat to test and system came on and shut off. Replaced flame safety sensor and system came on. Thermostat did not send a signal to the furnace to operate. Reset thermostat and now working normally. Suggest replacing the thermostat.
2 system furnace prepaid preventative maintenance service. Replaced filters, checked electrical and safety switches all ok at this time. Both systems need a combustion calibration, to get CO levels within safe range. Both systems heating normally.
Installed Guest room HVAC system
3 heating system preventative maintenance check complete. Changed upstairs and guest house filters. Found guest room system shutting off on low-pressure lockout due to it being void of refrigerant. Having no refrigerant in the system indicates a major leak. Recommend upgrading system. Found main level/ upstairs furnace with very high, unsafe levels of carbon monoxide, recommend recalibration to reduce co levels down to safe levels. The furnace also has a worn ignition system and weak blower motor controller. Basement system is also going off on low pressure due to it being void of refrigerant. Replaced blower motor controller and ignition system, and recalibrated CO levels from 133 ppm down to 22 ppm.