The residents of Hoschton, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Hoschton, GA area.
for Hoschton, GA
jud - Hoschton, GA
Chris is friendly and courteous. He knows how to operate our system and indeed he can explain it to us satisfactory. We struggle with changing the system, particular from one season to another. Nevertheless, Chris explains it in such a way that we understand!
Edeline - Hoschton, GA
On time, respectful, Very friendly great Coustomer service, due to service provided by tech I will recommend company and use again.
James was good about giving me a courtesy call 1/2 hr before he arrived. He was good about showing me what was done. Good job !
Eileen - Hoschton, GA
James showed me where the furnace had NOT been replaced a few months ago by a different company. I pd. for a product that had not been installed which is a travesty. He also pointed b out some wiring that was not to code.
jud - Hoschton, GA
He was very professional
James - Hoschton, GA
Job well done!
MICHAEL - Hoschton, GA
Jan - Hoschton, GA
Jon was timely, professional in his review. Wore booties and mask and maintained social distancing during the service call.
Wonderful Service. Very effecient service & Tech.
Mary - Hoschton, GA
On time, efficient & great Tech!
Always great service.
ERNEST - Hoschton, GA
As usual great service. John took the time to answer all of our questions.
Prompt service on weekends
Robert - Hoschton, GA
Reece was on schedule in fact early and solved my heating issue in short order. He was very courteous and helpful.
CAROLYN - Hoschton, GA
Robert - Hoschton, GA
Prompt, friendly, knowledgeable, effieient
Joanne - Hoschton, GA
Water leak from rodent damage
Rich - Hoschton, GA
Rich - Hoschton, GA
Excellent on all levels
Joanne - Hoschton, GA
chi - Hoschton, GA
We will definitely use your service again in the future
PATTY - Hoschton, GA
Tune Up Service
Thomas - Hoschton, GA
Excellent job and can't beat the prices.
jud - Hoschton, GA
I am very please with your representative's work. He not only found the problem, but he also made a photo of the damage which will help me going forward with my claim with my insurance!!
Jim - Hoschton, GA
Garrett very knowledgeable and helpful Very good price
Philip - Hoschton, GA
Gayle - Hoschton, GA
Great Service very professional
James - Hoschton, GA
professional very comfortable and confident representative .
David - Hoschton, GA
â€¢Dropping off filters. Changed out fresh air X filters for all 3 systems . Left a box upstairs in the attic and basement . Left box supply of filters .
HVAC issues in Hoschton Georgia. Warranty System is taking to long to heat house and not getting to asking temperature. Looking into that issue now . Checking settings and controls . Running several test on the equipment. Set up several dip switches. Put system in a test cycle . Also today had to charge system to speck levels and will recheck pressures in the summer to make sure they stay stable . Had to also recalibrate the thermostat. System is heating now .
Customer concern in hoschton. Arrived on site, customer complaint of unit running longer than they think it should. Explained that they have a steam humidifier and that it was trying to satisfy humidity in the house. Humidity set to 45% and it was only at 43% uppon arrival. Set humidity control to 40% to try to eleveat run time. Unit is operating normally at this time.
No heating main level in Hoschton. Check and find main level furnace ignition fail. Replace ignition and complete combustion calibration service for Lennox furnace. System operating at this time.
Looking over air quality in Hoschton Georgia . Found the air handler does have biological growth growing in the system . Took pictures and videos . Found the growth growing on the drain pan for the Evap coil . Found the biological growth growing on the air handler doors and on the wiring . Biological growth is on the condensation drain line on the pee trap . Going to be giving the family some solutions on how we can create cleaner air and get rid of the biological growth. Would also recommend putting a vent on the drain line with it being in a attic . Family is going with the recommendations on improving the air quality. Going to complete as much as I can today and the rest tomorrow. Will collect half today and the rest when the job is completed. Today I completed the rest of the air quality repair . â€¢Completed heating maintenance. Checked safety and performance. Checked heating elements. Checked integrity. Checked heat pump . Checked heat kit . Completed maintenance cleaning. Sy
â€¢Completed heating maintenance Hoschton Georgia . Checked the safety and performance. Renewal visit today . Checked the integrity of the heating operation. Checked heating elements. Changed air filter 16x25x1 . Tested zone dampers . System is heating properly at this time . Total amps on furnace are at specks . â€¢Recommend some form of air filtration device with a UV light to kill and prevent biological growth and to keep the system clean and add longevity to the equipment.
Heat pump maintenance in Hoschton, Georgia. Deaton Creek. One system. Changed filter provided by customer. Tested static pressure. Tested mechanical and electrical components. Discovered pitting on main electrical switch, recommend replacing switch. System has no surge protection, recommend installing surge protection to protect equipment from power surges. System is heating normal at this time.
â€¢Completed a two system tune up in Buford Georgia. Checked the performance and safety of the heating operation. Checked heating elements and amps on motors . Checked integrity. Changed air filters . Equipment is from 2005 . Equipment is 15 years old . â€¢Main floor furnace has a weak ignition and has silca build up would highly suggest replacing that electrical part to prevent future issues with the heating equipment. â€¢Main floor has a rusty R22 coil that could eventually lead to R22 leaks . Took pictures. â€¢Would recommend the water safety mechanics be upgraded To a water pan switch. â€¢Flame reader wire terminal shows signs of burning the terminal and the insulation. Would recommend replacing the wiring for that electrical part. â€¢Main floor has a weak blower start cap that runs and starts the blower would highly recommend replacing the blower start cap to prevent future break downs. â€¢Main floor is heating at this time but would recommend the repairs above. â€¢U
No heat in hoschton. Arrived on site, found bad comfortnet thermostat. Swapped face out under parts warranty. Unit is operating normally at this time
Free consultation for ductless mini split.
â€¢Completed heating maintenance in Hoschton Georgia on 2 mini split systems. Checked the safety and performance of the heating equipment. Checked heating elements. Changed air filter 20x20x1 . Flushed drain line and added a union for easy service on the drain line . Checked the integrity. Renewing the maintenance program today . UV lights are working properly. Heating equipment is working properly. Thank you .
- Completed a two system heating maintenance in Hoschton Georgia. Prepaid visit today . Checked the heating operation. Checked heating safety. Checked heating elements. Changed air filters . â€¢Main floor furnace. Has build up and debris on the blower wheel which is causing stress to the motor and taking about from performance/ air quality. Would highly suggest having the blower housing and wheel cleaned and deep chemical washed . â€¢Gas line is not code for the main floor furnace. Would highly suggest bringing the gas line up to code . â€¢Basement furnace has a clogged inducer port and needs to be pulled out and cleaned and the Bvent has particle and debris in it . You can hear it getting thrown around when the inducer is running . Family is going to call the company that put the Bvent in and see if they will cover it .
One system heat maintenance in hoschton. Arrived on site, changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Unit is operating normally at this time. Suggest installing uv air purifier to system to improve indoor air quality.
Heating maintenance Hoschton. Completed maintenance on 13 year old furnace. System is running good. Blower and heating elements clean. Tightened all connections. Safety switches working. Combustion is good. Gas line not ran properly to utilize sediment trap. Need to re run pipe to allow full use of trap. System would also benefit from having electro static filter and UV light treatment installed to better filter air and kill bacteria and viruses that could cause harm to residents
One system heat maintenance in hoschton. Arrived on site, changed filter and cleared barometric ports. Checked ignition systems, electrical connections amp draw and capacitance. Found system constantly running bec thermostat humidity control was on , but humidifier was off. Turned on humidifier and system started working properly. Recommended installing surge protector to unit. Installed surge protector. System is operating normally at this time
Heating maintenance Hoschton. Completed one system heating maintenance. Found furnace working good right now. Very slight layer of dust on blower wheel changed filter. Inducer and blower motors are good. Capacitor is good. System has no back up water safety. Gas line is ran improperly. Needs sediment trap ran to catch sediment correctly. System would benefit from having electro static filter and UV light treatment installed to clean air in house. Insulation in attic is low and needs more blown in.
Furnace maintenance in Hoschton, Georgia. Deaton Creek. Two systems. Changed filters. Tested mechanical and electrical components, all in good shape. Found neither system with surge protection, recommend installing surge protection to protect equipment from power surges. Recommend overflow protection switch for basement system to help protect furnace from potential water damage and to serve as a backup to primary water safety. Systems are heating at this time.
Heating maintenance Hoschton. Completed 2 system maintenance on 2 13 year old furnaces. Both furnaces have slightly dirty blower wheels. Both missing secondary water safety device. Upstairs has weak capacitor and gas line not ran properly. Downstairs would benefit from having an electro static filter installed to better clean air.
Heating maintenance Hoschton. Completed one system heating maintenance on 9 year old system. System is heating. Ignitor is good. Gas valve is good. Flame sensor is showing signs of strain and has started to crack. Needs to be replaced before it fails. Inducer motor is running at slightly higher amps then rated for. Needs to be replaced before it fails. Capacitor is good. Blower wheel is clean and has good amps. All safety switches working. Left new filters for customer. Insulation and ductwork is good. Zone board does not have designated transformer. Needs one to prevent failing of zone board or control board in furnace.
Heating maintenance Hoschton. Completed 2 system heating maintenance. Found both furnaces heating at this time. Upstairs has clean blower good electrical components but bad static pressure. System has plenty of return but needs more supply to allow for better air flow. Suggest adding 2 supply vents to give better air flow. Also suggest adding electro static filter to also improve airflow. Downstairs has good heating components. Slightly dirty blower wheel zone board is good but basement vents are tied into upstairs zoning. Downstairs is also missing secondary water safety device to protect furnace from water damage.
Heating maintenance in Hoschton . Tested operation of one heat pump system. Discovered system locked out on high head pressure. Discovered clogged filter which would Create high pressure in the system. Removed filter and homeowner is going to order more. Reset outdoor system. Checked pressures and all components. Discovered week secondary motor controller And no drain line water safety. Discovered organic growth inside indoor unit. Replaced secondary motor controller added drain line water safety and installed compressor saver hard start kit to system. Need to return to install pureairX RM2 Ultraviolet light system to combat organic growth inside unit. Signed homeowner up for maintenance membership. System operations normal at this time. Returned and installed RM2. Sent estimate over for dehumidifier for crawlspace
One system heat tune-up in hoschton. Arrived on site, checked filter and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found unit with blower cap reading low and no overflow switch. Also recommend installing surge protection to Unit to protect electrical systems. Unit is operating at this time
Heating maintenance Hoschton. Completed heating maintenance. Found air handler heating properly. Emergency strips coming on with good amps. Blower is clean UV light is good changed filter. Static pressure is good. System heating properly.
Heating maintenance Hoschton. Completed heating maintenance on 3 year old furnace. System heating properly. Filter is good will need to be changed in spring. Motors are running good. Blower is clean. All safety switches working.
Heating maintenance Hoschton. Completed one system heating maintenance. Found 10 year old furnace running properly. Blower is clean. Static pressure is good relating to air flow. Filter is good. All safety switches work. Surge protector is good. uV light is over 2 guests old and needs to be replaced. Insulation in attic is good. Gas pipe ran properly. Motors have good amps. Capacitor is good.