Usually, AC repair costs average from $150-$550 near Hoschton and the northeast Atlanta area. However, prices can also be higher depending on the extent of the repair.
A repair like a thermostat, fuse or relay replacement typically will be near the lower end of the range. Replacing an evaporator coil or repairing a refrigerant leak can cost $1,000 or more.
Other factors that affect the price include:
- The size of the AC system.
- The make and model of the unit.
- The complexity of the repair.
According to EnergyStar, a typical HVAC system should last about 15 years in our area of northeastern Georgia.
Many factors can impact the lifespan, including:
- The make and model of the AC unit.
- How often the homeowner keeps up with routine maintenance, such as air filter changes.
- The frequency of professional inspections and service maintenance.
To learn more about typical lifespans of HVAC systems in our area or maintenance recommendations for the Hoschton area, schedule a Comfort Control appointment today!
You can check indoor air quality by purchasing an air quality monitor, using at-home tests for individual pollutants or working with a professional air-quality testing service.
- At-home tests and monitors allow you to get an initial idea if you have unacceptable levels of contaminants like radon, mold spores or volatile organic compounds (VOCs) in your home.
- Air quality professionals can help you confirm test results, recommend testing for specific allergens or pollutants and recommend and install solutions for air quality problems. A professional company may also save you time and hassle vs. DIY tests.
The residents of Hoschton, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Hoschton, GA area.
for Hoschton, GA
Rich - Hoschton, GA
Michael - Hoschton, GA
Great Service/Awesome Price
Ralph - Hoschton, GA
Very nice young man, friendly,Helpful with our questions & explanations . Through job with install and clean up and everything was very satisfactory . Thanks for such a quick response and install. Water heater was at a point it could have opened open and poured out the water. We only moved in three months ago and you have already resulted two major problems in our new residence. Thanks so much!
jud - Hoschton, GA
Young man is outstanding
Joanne - Hoschton, GA
ERNEST - Hoschton, GA
Brett provided great service and was very thorough
Extremely thorough effort by serviceman
Ken - Hoschton, GA
on time, courteous, explains possible issues
Robert - Hoschton, GA
IKEM - Hoschton, GA
First Service Call Review
Who is John Galt - Hoschton, GA
Jordan was professional, courteous, very knowledgeable about heat pumps, and arrived ahead of schedule! Agreed to 3 of 5 servicing items. Prices on 3 items seemed reasonable after discounts. Opted not to get the $1,400 ultraviolet system to prevent organic matter presence and was not offered any alternatives or how to self-clean. Company needs to revise the 'system check form' to properly annotate combustion checks do not apply to heat pumps. Otherwise, pleased with first service call with Comfort Control.
Allen - Hoschton, GA
Great, Fast Service, Awesome Price!!!
Carmen - Hoschton, GA
I am a real estate agent and needed a HVAC company to come out the same day to look at the unit on my seller’s home which we were closing on the next morning. Reece came out within 1 hour and fixed the issue for a great price. I would definitely recommend Comfort Control Heating and Air to anyone needing fast, reliable service at a great price!
Great & very effecient!
Mary - Hoschton, GA
Would definitely give a share with others😊
CAROLYN - Hoschton, GA
Philip - Hoschton, GA
Wonderful service and a great price !
Jorene - Hoschton, GA
Great service super kind
Barbara - Hoschton, GA
Very please with my service
Philip - Hoschton, GA
DAN - Hoschton, GA
Jon was great. He listened and explained everything to me.
ROBERT - Hoschton, GA
Great service, great employers
CAROLYN - Hoschton, GA
Jon was on time and did a great job
CHRIS - Hoschton, GA
Mr. Wilson quickly diagnosed the problem, fix the issue, and offered options going forward with our aging furnace. Well done!
Rich - Hoschton, GA
jud - Hoschton, GA
Chris is friendly and courteous. He knows how to operate our system and indeed he can explain it to us satisfactory. We struggle with changing the system, particular from one season to another. Nevertheless, Chris explains it in such a way that we understand!
Edeline - Hoschton, GA
On time, respectful, Very friendly great Coustomer service, due to service provided by tech I will recommend company and use again.
Service call in Buford. Changed filters on all 3 systems, UV bulbs are not the ones we have. UV Bulbs need to be ordered. All 3 systems are cooling at this time.
A/c diagnostic in Hoschton, system is not cooling properly, blower wheel is clean, evaporator coil looks good. Filter is clean.
Actually service in Hoschton. Discovered compressor blow terminals and is leaking refrigerant. System under warranty for outdoor replacement and ordered.
Ac service in Hoschton. Discovered system running with a 27* superheat, extremely rusted coil, blower motor leaking oil, water in furnace, outdoor air electrical switch starting to burn and becomes pitted. Due to age, compressor and type of refrigerant, replacement is HIGHLY recommended.
Year old Daiken system is not cooling, found the EEV valve to be stuck and not allowing enough refrigerant through. Unstuck valve and system is cooling with a 18Â° split. If issue persist the EEV valve will need to be replaced. Brought subcool up to 9Â° and superheat to 22Â°.
A/c diagnostic in Hoschton. Indoor unit is in the attic. System is cooling at this time. Fan speed is on high, filter is clean. Outdoor condenser is clean, had to adjust pressures and they are good now. Thermostat is set to 74Â° and room temperature was at 76Â°. With testing unit temperature went up to 78Â°. Did more diagnostic testing on the unit and everything is working properly at this time.
A/c diagnostic in Hoschton. System is not turning ON. Unit has no refrigerant at all, found leak in the evaporator coil. Evaporator coil is covered under full warranty.
A/c diagnostic in Hoschton. Unit had a really dirty filter, restricting airflow through the coils making it ice up. Last time we were out from the work performed in the history, is ( 8-1-20 )
No cool Hoschton. Completed diagnostic. Found system with completely clogged. Changed filter. Found no leaks in coil. Furnace is clean and all components inside and out are good. Pressures are good. System cooling at this time.
Ac service in Hoschton. Discovered failed outdoor temp thermistor. Order from east coast Suwannee
2.5 ton AC, Furnace and Coil 10 years parts 10 years labor Lifetime compressor warranty Lifetime heat exchanger warranty
A/c diagnostic in Hoschton. Main level system was not cooling found weak dual capacitor. Also condensate pump was dirty. Blower wheel is clean, evaporator coil is clean, flush drain line and cleaned condensate pump, changed filters.
GFCI outlet tied into condensate pump had tripped. Reset outlet and system began operating properly. If issue persist an electrician needs to be called. Performed tune up on system while here. Condensate pump is operating properly. Drain line is clear. Drain pan has sediment buildup across it. 20x25x4 filter is in fair condition. Return ducts are clean. Blower wheel has light accumulation. Blower capacitor is within range. Coil has corrosion present. Waived diagnostic and enabled membership, need to schedule membership cooling visit to clean coils.
System is a 2000 pAyne leaking r-22 refrigerant, gave options for system repairs and replacement. $2838 for repairs , $8614 for replacement. Customer wants to contemplate what route he wants to go. Thank you for choosing comfort control.
3 system maintenance in Hoschton. 1st unit main level in the attic system is cooling at this time. Changed filter, flush drain line, blower wheel is clean, evaporator coil is clean. 2nd unit 2 zone in the attic. Changed filter, flush drain line, blower wheel is clean, evaporator coil is clean. System is cooling at this time. 3rd unit is in the basement. System is cooling at this time, evaporator coil is clean, blower wheel looks good, changed filter, and cleaned drain line.
System is completely frozen. Need to reschedule for this weekend when system thaws out. Will be service call $79.
A/c tune up in Hoschton. 2 system in attic. 1st unit (upstairs) system is cooling at this time. Changed filter, blower wheel is clean, evaporator coil is clean, drain line was cleared. 2nd (downstairs)
501 filter was incorrectly installed causing poor return airflow. Replaced ezt225 with an SS1. Sealed air leaks in plenum on another unit as well. All work is out of warranty. Highly recommend a maintenance plan for the customers equipment.
Customer likes the house at 77 degrees, but has higher than comfortable humidity. Slowed the blower speed down to medium-low and adjusted charge for the new speed. Pressures and temperatures are well into the acceptable range. Delta T is at 18. Humidity dropped 2% after the final adjustment. If more dehumidification is wanted, we will slow the blower to low speed and adjust the charge accordingly.
Ac service in Hoschton. Discovered system leaking refrigerant heavily from evaporator coil. Thawed system out and homeowner has chosen to replace ac and coil with 16 SEER AC AND COIL C CABINET. Refilled refrigerant for temporary cooling. Collected deposit. Need to schedule install
Customer is renting home. Filter is good at the time. 4 in media filter. Customer does not want maintenance plan at this time.
Customer is checking with her son, Brian Polke, before making a decision.
Maintenance Hoschton. Completed maintenance on 14 year old system. Found evap coil leaking r22 Freon. Capacitor for blower is weak. Outdoor unit has pitted contactor. Blower wheel is slightly dirty. Insulation level in attic is very low. System needs to be replaced due to age and efficiency. Insulation needs to be blown in.
Maintenance Hoschton. Completed maintenance on 11 year old system. Pressures are ok. Coil is rusted. Blower is clean. Safety switches working. Electrical components outside are good. Inside capacitor is weak. Replaced capacitor. System cooling at this time.
Replaced evap coil under parts warranty. Pressure tested system. Found no leaks. Pulled vacuum down to 500 microns. Filled with 410 refrigerant. System cooling at this time.