The residents of Gainesville, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Some reasons your home air conditioner may be blowing hot air are:
- Your air filters are clogged.
- Your air conditioner has a refrigerant leak.
- Your evaporator coil is dirty or frozen.
If your home air conditioner is blowing hot air, you can try replacing the air filter or resetting the thermostat. If your air conditioner is still not working, you should have an HVAC technician repair it. To get your home air conditioner repaired, contact us today.
Residential air conditioning repair typically costs around $350-$600 in Gainesville, GA. The price can vary due to:
- The type of AC repair.
- How extensive the repair is.
- The HVAC contractor’s hourly fee.
Cold air may be coming out of your air vents when the heat is on because:
- Your condensate drain line is clogged.
- Your pilot light is out.
- Your air filters are blocked.
If your HVAC system is not working properly you should also always check to ensure that the thermostat is set correctly. Your thermostat should be set to HEAT and AUTO. To get your heating system repaired, call us today.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Gainesville, GA area.
for Gainesville, GA
Appreciatead John's professional attitude.
Becky - Gainesville, GA
Beata - Gainesville, GA
John came on time and fixed problems with our air conditioner. He answered all questions I had and he was very professional. In addition, he was very nice.
Steve - Gainesville, GA
Pleasant knowledgeable young man
Clair - Gainesville, GA
Wayne - Gainesville, GA
George - Gainesville, GA
Reese had to deal with an entirely nee experience - dehumidifying an indoor pool - he handled it exceptionally well
Outstanding service and demonstrated understanding of hiw field of knowledge
George - Gainesville, GA
Kimberly - Gainesville, GA
Jon was a great technician. He was very professional and he identified our issues quickly. I appreciate the text telling when and who would be coming to my house. I will definitely call Comfort Control for any future heating or air conditioning needs.
Wayne - Gainesville, GA
Bill - Gainesville, GA
Thank you for working with the schedule change making it more convenient for us. He was Very informative. Merry Christmas 🌟
Always prompt service
JAMES - Gainesville, GA
Great service and thorough
Jim - Gainesville, GA
JAMES - Gainesville, GA
I always get great service
David - Gainesville, GA
Ms - Gainesville, GA
WILLIAM - Gainesville, GA
Your service tech. is very good and goes over every item on the check list. This gives us as home owners a good feeling that our system is working well.
Thorough and knowledgeable.
Walter - Gainesville, GA
Julie - Gainesville, GA
Jon was very nice, professional, efficient and proficient! He was on time and is very friendly and courteous. He removed his shoes before entering the house and wore a face mask. Nice guy and great service!
JOANN - Gainesville, GA
Excellent service. Vu was very knowledgeable with how my unit worked .
Sid - Gainesville, GA
As always good service.
Bernice - Gainesville, GA
Kris - Gainesville, GA
I have been with this company for years even through a buy-out, I am always satisfied with their technicians and their recommendations. Will continue my wonderful service contract with them.
Brittany - Gainesville, GA
Jordan was very professional and nice . Very quick appointment time , and fix for our issues .
JAMES - Gainesville, GA
Service is always top notch and explains if anything needs attention.
Amazing and Quick service
Alan - Gainesville, GA
John was very professional, knowledgeable and courteous. He explained in detail the problem with one of my units. He suggested a solution and in 30 minutes problem was fixed. Very pleased with the level of service he provided!
No one was home and phone is incorrect - tech showed pictures of being at the location
Ac maintenance in Gainesville ga. One system. Checked all electrical and mechanical components. Did not change filter. Checked drain line. Found all functions functioning properly at this time. Found system to only have one form of water safety. Recommend having two. System cooling at this time.
Main level system not cooling diagnosed bad thermostat. Replaced thermostat with programmable Aprilaire. System is cooling at this time.
1 system ac maintenance in Gainesville. Checked mechanical and electrical components.cleared drain line. Recommend overflow protection switch to provide peace of mind against water damage. Recommend surge protection for both units. Recommend UV filtration system to kill mold and viruses and bacteria that are starting to grow inside the air handler. System is operating normally at this time.
Maintenance Gainesville. Completed maintenance on 2 systems. Both systems under 5 years old. Clean blower wheels clean evap coils. Pressures temp difference and air flow are good on both. Changed left side filter. Will change right side filter on next visit. Recommend UV light on left side of house for whole home purification.
Ac maintenance in Gainesville. Tested operation of 1 systems. Discovered compressor starter weak and outside of manufacturing spec. All other components tested within normal manufacturing spec. System would also benefit from a duct cleaning and surge protection as protection for the most expensive appliance in the home is beneficial. Systems cooling at this time. Homeowner was charge for 2 system maintenance plan but itâ€™s only a 1. Need to refund the difference
Tune up Gainesville. Completed tune up on 1 year old system. System cooling good. Changed filter. Everything clean inside and out. All electrical components working good. System needs water safety installed. System would benefit from hard start kit installed to outdoor unit. Home would benefit from having UV light installed to kill bacteria and viruses in air.
Package unit not heating in Gainesville, Georgia. Found faulty thermostat. Replaced thermostat with Honeywell 9000 thermostat. System is operating at this time. Customer used $50 gift card.
Ac maintenance in Gainesville. Tested operation of 1 systems. Discovered compressor starter weak and outside of manufacturing spec. All other components tested within normal manufacturing spec. Recommend ultraviolet light system to combat organic and viral growth in systems and throughout the home, duct cleaning to improve indoor air quality as well. Systems cooling at this time.
2 system ac maintenance in Gainesville. Changed filters. Cleaned condensate pumps. Cleaned outdoor unit/coil. Checked mechanical and electrical components. Recommend overflow protection switch for main level system.
Furnace repair in Gainesville. Discovered improper flue pipe ran horizontally in crawlspace for an 80% furnace. Pressure fort clogged and combustion motor weak and rusted. Cleared pressure port and system heating at this time. Homeowner does not want any repairs
Tune up Gainesville. Completed tune up on 2 year old system. Everything clean and working within range inside and out. Pressures and temp difference is good. Insulation is good. Recommend secondary water safety device to protect furnace from water damage. Recommend hard start kit to help compressor during start up and allow compressor to live longer.
No coil Gainesville. Completed diagnostic. Found older thermostat not working. Replaced thermostat. Got system running. Coil is clean blower is clean. All electrical components working. Temp difference is good. System cooling at this time. Customer needs more electro static filters. Sold more filters.
complementary custom consultation in gainesville
No heat in Gainesville. Arrived on site, found wire coming from the compressor had burned out on the capacitor terminal. Replaced capacitor and repaired the wire. Tested system, unit is operating normally at this time.
Maintenance Gainesville. Completed maintenance on 2 year old system. Had bad fuses in disconnect box. Replaced fuses. System came on. Pressures and temp difference is good. Blower and coil is clean. Changed filter. System cooling properly
Ac repair in Gainesville. Discovered drain line clogged and tripped water safety cutting communications to outdoor unit. Cleared drain and system operation normal at this time. Signed back up for maintenance membership.
Ac maintenance in Gainesville. Tested operation of 2 systems. Discovered upstairs system with weak secondary controller, main electrical switch and hard start, discovered downstairs system with weak hard start and main electrical switch. Downstairs outdoor compressor and fan motor pulling really high amps. System is 14 years old and replacement should be considered. Replaced hard starts and secondary controller. Systems cooling at this time.
Ac repair in Gainesville. Discovered system frozen over due to clogged filter. Ran system in heat mode. Homeowners stated they will leave the system off for a day and turn it back on. Cleared drain line and signed up for maintenance membership.
Hvac tune up in Gainesville, Georgia. Two systems. Upstairs system not working. Found popped fuse in air handler. Replaced fuse and cycled heat, emergency heat and cooling and could not get problem to duplicate itself. Inspected low voltage wiring and found no damage. Took anohm reading of contactor and it is good. Found extremely weak capacitor in main level system (45/5), recommend repair and installing hard start kit to reduce load on compressor so it starts smoother, runs smoother and therefore lasts longer. Replaced main level dual capacitor and installed hard start kit for main level as well. Systems are cooling at this time.
2 system maintenance in Gainesville. Media filter found to be clean. Checked mechanical and electrical components. Found mold in the supply plenum. Recommend uv light filtration system. System is operating at this time.
No heat Gainesville. Completed diagnostic found clog in drain line and clog in pump. Cleaned both out and tested pump. Ran system and found low on refrigerant. Did thorough leak test and could not find one anywhere inside or out. Filled system with 410a. System cooling at this time.
Water leak Gainesville. Completed diagnostic. Found condensate pump cracked and leaking. Replaced under full warranty with customer. System cooling at this time.
Ac maintenance in Gainesville. Tested operation of 1 system and 2 mini splits. Cleaned outdoor coils and checked all components. All components tested within normal manufacturing spec. Systems operation normal at this time.