The residents of Flowery Branch, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Flowery Branch, GA area.
You call someone who fixes air conditioners an air conditioning repair contractor, or HVAC contractor. They are also known as AC technicians. If you are looking for a reputable air conditioning repair contractor near Flowery Branch, GA, we can help. Contact Comfort Control for prompt expert AC repair services today!
There could be a number of reasons why your AC is running but not cooling your home near Flowery Branch, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Dirty Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home and cool air is not allowed to circulate.
- Refrigerant Levels are Low - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Faulty - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
The best way to keep your indoor air clean in your home near Flowery Branch, GA is to invest in an air purification system. Whole home air purifiers collect your home’s air, filter out and treat the air before returning it back inside your home, clean and pure. To learn more about the air purification systems we offer, or for more information on indoor air quality, contact Comfort Control today!
for Flowery Branch, GA
David - Flowery Branch, GA
Great customer service.
Mazzie - Flowery Branch, GA
prompt knew who was coming update and picture Great job
JAMES - Flowery Branch, GA
Response time was outstanding. A/C not working so I called to schedule appointment time (between 3 to 5 PM). Reece called and arrived much earlier. He checked system and made repair immediately. He answered several questions. Would highly recommend Company and Reece.
Wendy - Flowery Branch, GA
Excellent technician AND price!
LISA - Flowery Branch, GA
Service tech Christian was excellent. From beginning to end, this was quite a pleasant experience. He called to advise of arrival time, and was right on time. Once here, he repaired the issue quickly, and was extremely polite and friendly. The price was more than fair! My first time using this company, but definitely not my last. Thanks Comfort Control, and Christian for great service!!
Stephen - Flowery Branch, GA
Charged my system and was very nice.
Laurie - Flowery Branch, GA
We had a tech at our house within 2 hours of calling for an appointment. Mark, the AC tech, was awesome. He was thorough, knowledgeable, and took time to answer all of my questions. He was kind and respectful. I would call them again.
Lynn - Flowery Branch, GA
Efficient and fast service
Daniel - Flowery Branch, GA
Lacrisia - Flowery Branch, GA
Good info given.
Good job and very pleasant.
Betty - Flowery Branch, GA
Respectful young man and knowledgeable.
Very clear and efficient!
Diana - Flowery Branch, GA
I am extremely impressed with his work. He examined everything thoroughly, gave me 3 different options, and finished the job in a very timely manner.
Richard - Flowery Branch, GA
It was great
Great, as usual!!
Joseph - Flowery Branch, GA
Reece called just before he arrived, and arrived within the appointment time. He was polite, upbeat and very professional. He took his time to analyze our complete system, and cleaned the outside unit.
Great Service, Highly Professional Technician
James - Flowery Branch, GA
Vu Tran, the service Technician, was very thorough conducting the inspection and condition of both units. I commend Vu for doing a very good job. Thanks, Vu. James
As always great!
Austy - Flowery Branch, GA
Mary - Flowery Branch, GA
I had a great experience with your company today. Garrett was so helpful in getting my family and I the Unit we needed. It was a great experience to work with this kind young man.
Mary - Flowery Branch, GA
Jordan was knowledgeable about the work he was doing in my home. Help to find a resolution to the problem with my AC unit.
GLORIA - Flowery Branch, GA
Tech was very respectful, pleasant & soft spoken. I would have him come to our home again. Job oriented.
Clayton - Flowery Branch, GA
Margie - Flowery Branch, GA
Janice - Flowery Branch, GA
Very Professional and took time to explain the work he was doing!
Best service hands down
KYLE - Flowery Branch, GA
Amazing service and explanation of what was being done. Great help and really went the extra mile. Vu was outstanding.
we're very pleased with chris as he will be our new person since steve left.
Cheryl - Flowery Branch, GA
great job chris thank you.
Dru - Flowery Branch, GA
Reece was informative thorough and got my air up and running
Heating maintenance flowery branch. Completed heating maintenance. Found everything clean and working properly. Flame sensor is discolored but still working within spec. Capacitor is good. Blower whee is clean. Cleaned induction port. Changed filter. Zone board working properly. System heating at this time.
Heating maintenance flowery branch. Completed heating maintenance on 4 year old system. Everything turning on properly. Flame sensor is clean. Cleaned inducer port. Combustion is good. Sold box of 4 replacement filter. Blower wheel is clean. Capacitor is good. Showed customer how to work dampers on ducts at the plenum. System is working properly.
Heating maintenance flowery branch. Completed 2 system maintenance. Main floor furnace is 12 years old and has good blower with new filter. Inducer motor is good. Cleaned inducer port. Flame sensor is good. Ignitor has silicon build up. Burners have slight rust inside and around openings. If rust gets bad enough it will make a hole and allow carbon monoxide slip into house. Systems are heating properly at this time.
Tune up flowery branch. Completed 2 system tune up. Found both units 7 years old. Upstairs has clogged drain line and very dirty filter. Changed filter cleared drain line that was causing water damage. Downstairs system has clean blower wheel and coil. Replaced filter and added algae tablets to pump downstairs. Both systems have good pressures and are cooling properly at this time.
Heating maintenance flowery branch. Completed one system heating maintenance on 2 year old furnace. Blower is clean. Capacitor is good. Flame sensor and ignitor are both clean. Heat chambers of no sign of rust. Changed filter. Combustion readings are good. Cleaned inducer port. Gas line is up to code. Zoning is correct. No signs of leaks in duct work. System heating properly at this time.
Water leak flowery branch. Completed diagnostic. Found drain line clogged and secondary water switch tilted up and would not activate causing excess water to drain into system and down return duct. Cleared drain line. Reset switch and cleared return box of water and re sealed return duct. System cooling at this time.
No cool 20 year old heatpump system in flowery branch. Check and find Armstrong Evaporator coil in atttic freezing up and leaking charge. Find system housing dirty, and water in side system and drain pan, customer have no water protection in attic. Find heatpump system operating with worn pitted contactor, and compressor operating with high power usages. System 20 year old operating in poor conditions, suggest to replace system and not repair. Customer want to add charge for today visit and also need consultation visit.
Ac service flowery branch. Completed diagnostic. Found drain line clogged at p trap. Cleared drain line. Evap coil has no signs of freezing. Ensured condensate draining properly. System has concerning amounts of mold in and around system. Recommend pure air treatment installed to kill mold bacteria viruses and allergens that could cause harm to residents. System has no water safety installed recommend inline float switch to turn system off in case of clogged drain line. Outdoor unit has good pressures. System not low on refrigerant. System cooling at this time. Customer needs hard copy mailed to her.
Ac service flowery branch. Completed diagnostic. Found bad thermostat and wired wrong at thermostat. Replaced thermostat and wired correctly. Tested system. System cooling at this time.
ac service flowery branch. Completed diagnostic found capacitor dead on compressor side. Replaced capacitor under warranty. System running at this time. Will pay service Wednesday morning.
Ac repair in Flowery Branch, Georgia. Found system with bad blower motor. System is a zoned system and has no bypass damper like it is supposed to. Ductwork is undersized. Recommend replacement of blower motor, Installing an 8â€ return, installing a 10â€ bypass damper, and installing a 10 inch supply duct that branches out into two 8â€ ducts upstairs. Customer just wants to replace motor for now. There is no labor warranty on motor because of undersized ductwork and no bypass damper, customer understands that. Replaced blower motor and system is cooling at this time.
Signing family up for a two system maintenance:) . Checked safety and the performance of the cooling equipment. Completed chemical washed on both outside coils . Concerns found today will be below ... â€¢Downstairs system is very low on R22 due to a leak in the system . The system has hardly any pressure in the system . Would highly recommend upgrading the system due to age and with the R22 phase out by the EPA . â€¢Downstairs outside dual start cap is getting rusty and could eventually leak oil would recommend replacing that electrical part . â€¢Downstairs doesnâ€™t have any form of water safety would highly recommend to prevent water damage. â€¢Downstairs coil has a leak took pictures of the coil conditions . Very rusty with lots of corrosion. Would highly recommend a new system . System also has water damage inside the furnace and has bacteria growing in the system . Took pictures. â€¢Downstairs blower motor is running hot . Family is scheduling a visit for a consultatio
No cool flowery branch. Arrived on site, found outdoor unit not functioning due to bad capacitor. Replaced under parts warranty. Checked pressures and electrical systems. Unit is operating normally at this time
No cool flowery branch. Arrived on site to find unit freezing up due to leak in refrigerant system. Recommend replacing equipment. Turned system off at thermostat as well as furnace switch till customer comes home and we can discuss replacement. Unit is not functioning at this time.
Ac diagnostic in Flowery Branch, Georgia. Upstairs system was not cooling. Found water inside emergency drain pan causing water safety switch to trip and shut off outdoor unit. Removed water from pan. Found drain line backed up. Cleared drain line, added cleaner to drain line, added drain pan treatment into system and added chlorine tablets into system. Tested mechanical and electrical components and found no issues. Found early signs of mold in system. Recommend uv light system to kill mold, bacteria, germs and viruses for improved air quality. Recommend hard start kit to reduce load on compressor so it starts smoother, runs smoother and therefore lasts longer. Changed filter. System is cooling at this time. Thank you so much for your business today! It is greatly appreciated! Its customers like you that keep us in business and keep our families taken care of! If you were happy with your service today and you wouldnt mind, please take a few minutes to give us a 5 star review on google
No cool in flowery branch. Arrived on site to find unit not keeping up. Checked indoor unit and found corroded evaporator coil that was freezing up and a weak blower capacitor. Outdoor found refrigerant pressures low as well as a burnt and pitted contactor. Due to age and state of coil, recommend replacing equipment
Ac repair in Flowery Branch. Found system with bad dual capacitor. Replaced dual capacitor and system is cooling at this time. Blower capacitor is weak as well. Customer used $35 off coupon
No cool. Found system low on r410a and leaking at evaporator coil. System is not under warranty. We could either replace the evaporator coil or replace the system.
Warranty in flowery branch. Arrived on site, found no power going to Thermostat. Found secondary water safety switch tripped due to clogged drain line. Cleared drain line and reset switch. Unit turned on and started operating normally. No other issues present at this time
2stage dual fuel 96% furnace installation complete! Thank you for your business! Gavin and Mark
No cool Trane air conditioning system in flowery branch. Check and find Trane Airhandler system in attic wet switch sensor shut off ac for safety. Reset wet switch and system operating at this time. Find filter very dirty, replace filter customer provided in attic 20x25x1. Find drain system not level, dirty and missing P-trap. Find Trane heatpump system operating with low R410A, missing hard start kit and worn/pitted and buzzing contactor. Give customer estimate to repair system.
Complete 2 air conditioning tune up special in flowery brand. Find 2 Trane 4 year old air conditioning system operating with in manufacturer spec. System cooling properly at this time. Find both evaporator coil in attic with no in-line water protection from drain system, find both ac unit missing hard start kit. Suggest to install hard start kit for both Trane system, suggest in-line water protection for both system in attic and suggest surge protection for outdoor system. Change 2 16x25x1 filter, clean ac unit and dig drain line out of ground for customer. Install 2 starter kit for air conditioning system.