The residents of Flowery Branch, GA have considered Comfort Control a dependable company for AC repair and heating services since 1992.
Read how we provide top quality air conditioning service and heating repair to homeowners in the Flowery Branch, GA area. Schedule an appointment today for air conditioner repairs.
HVAC Service FAQs
You call someone who fixes air conditioners an air conditioning repair contractor, or HVAC contractor. They are also known as AC technicians. If you are looking for a reputable air conditioning repair contractor near Flowery Branch, GA, we can help. Contact Comfort Control for prompt expert AC repair services today!
There could be a number of reasons why your AC is running but not cooling your home near Flowery Branch, GA:
- Tripped Outdoor Circuit - A central AC has both an interior and exterior breaker. If the outdoor breaker has tripped, the unit will continue working but will not produce cool air.
- Dirty Air Filter - When an air filter becomes very dirty, it clogs airflow throughout a home and cool air is not allowed to circulate.
- Refrigerant Levels are Low - Refrigerant runs on a closed circuit, so if levels are low it most likely means you have a leak. When levels are low, the unit cannot produce enough cool air to cool your home.
- Compressor is Faulty - The compressor works to circulate refrigerant, so if this important part is not working properly, the air coming into your home will not be cool.
The best way to keep your indoor air clean in your home near Flowery Branch, GA is to invest in an air purification system. Whole home air purifiers collect your home’s air, filter out and treat the air before returning it back inside your home, clean and pure. To learn more about the air purification systems we offer, or for more information on indoor air quality, contact Comfort Control today!
It costs around $150-$350 per year to service an HVAC unit in Flowery Branch, GA. HVAC service generally includes the following:
- A cleaning of your HVAC unit.
- An inspection of your HVAC unit.
- A lubrication of your HVAC unit’s moving parts.
- A replacement of your air filter.
Yes, HVAC service agreements are worth it in Flowery Branch, GA. HVAC service agreements provide the following benefits:
- Your HVAC system has a longer service life.
- Your HVAC system stays covered under warranty.
- Your HVAC system requires fewer repairs.
HVAC service agreements can also help reduce the cost of your monthly energy bills since regular servicing allows your HVAC system to run as efficiently as possible. To get your HVAC system on a maintenance plan, contact us today.
A few reasons you may want to replace your home heating and air conditioning system in Flowery Branch, GA instead of repair it include:
- Your HVAC unit is over 10 years old and requires many repairs.
- Your HVAC unit does not heat and cool well anymore.
- Your HVAC unit breaks down frequently.
- The repair cost is more than half the cost of replacement.
Another sign that you should replace your heating and air conditioning system rather than repair it is if your energy bills have drastically increased. To get your home heating and air conditioning system repaired or replaced, call us today.
for Flowery Branch, GA
Howell - Flowery Branch, GA
Pat - Flowery Branch, GA
Right on time did a very good job
Tech was great,friendly and knew what he was doing
Lowell - Flowery Branch, GA
Good Service and advice on AC Service
AW - Flowery Branch, GA
BETTY - Flowery Branch, GA
Great job, respectful and excellent service
LaCrisia - Flowery Branch, GA
Did a great job, worked efficiently and asked if I had any questions or concerns.
Susan - Flowery Branch, GA
Jordan was very thorough with checking the system . He also realized that my contract was not renewed in the spring something I completely missed. I appreciate his honesty today and ability to make sure the system was operating properly. I would like to request that he is my technician for future contacts if it is possible.
Garry - Flowery Branch, GA
Very quick to respond to an emergency situation. Signed up for an annual maintenance contract. Very professional.
Wendy - Flowery Branch, GA
Erik and his team were amazing.. They arrived early , protected my floors & cleaned all areas when they left.. Explained & showed photos of all compon
JULIE - Flowery Branch, GA
Great team, friendly & efficient..
Steven - Flowery Branch, GA
Awesome service again! Quick response!
Reliable and thorough service!
Christi - Flowery Branch, GA
James arrived on time and took care our unit! He communicated the problem immediately and was very polite!
Tyler - Flowery Branch, GA
Great service. Very nice.
Issue with air conditioning
CHERYL - Flowery Branch, GA
Happy with James.
Very professional and informative!
Larissa - Flowery Branch, GA
Russ - Flowery Branch, GA
very nice tech.. keep him
Ricky Fernandez was excellent! He called & let me know when he would be arriving.. & performed excellent in every area. The weakness lies in office co
JULIE - Flowery Branch, GA
Ricky spent a lot of time checking out the unit in the very hot attic..Said the filter was in serious need if changing..& actually had the correct size filter on his truck.( which was always a problem in the past) ..He was great .Spent time going over the newer unit in the basement installed 21/2 yrs ago that always had cold air leaking out due to a bad install .. The mechanical room is as cold as a meat locker & the temp is set at 78 for that area & the entire basement reads 72. He took time to cover leaking areas to keep the cold air from escaping..Hopefully that will help the first floor that remains 4 degrees hotter than it’s setting..that is on that system..Ricky was informative, hard working & extremely pleasant..Excellent worker !!! Only negative : Office communication needs work..extremely frustrating Which I generously gave an average..I think they just had a bad week…
Pat - Flowery Branch, GA
Very nice and explained every thing to me
Sharon - Flowery Branch, GA
Upon arrival, my technician was friendly and listened to me! We actually both used to live in Plantation, Florida! Service took about an hour! I get to sleep in the ac tonight!
Great maintenance service
CHARLES - Flowery Branch, GA
Air conditioner was serviced and all the findings by the tech were addressed and completed in a timely manner.
CHARLES - Flowery Branch, GA
The air conditioner stopped working last night. Made a service call the next morning and got a time for later during the day. The tech quickly found that the condenser unit’s contactor was shorted out due to a mouse getting into the control box.
David - Flowery Branch, GA
Great service “Jordan’s the man”
Dominick V - Flowery Branch, GA
Jordan was very knowledgeable on hvac systems. Not only did he explain how the system works and what he can do to fix it. He also walked me through what the exact problem was. Unlike other companies where you have to wait days for a part. Jordan was able to get the part in less then 24 hours and help my hot wife get cool ;). Again Jordan and comfort control will always be my go to hvac company.
Tammy - Flowery Branch, GA
Linda - Flowery Branch, GA
The tech was here for my problem so fast and at night ! Never expected that great of a time factor!
A/c diagnostic in flowery branch, upon arrival I found emergency pan filled with water, condensate pump was dirty and clogged, flush drain line and cleaned condensate pump. System came back ON. System is cooling at this time. Outdoor refrigerant pressures are good.
A/c diagnostic in flowery branch, indoor unit was running but not the condenser found one of the low voltage wire broke off do to age fixed problem. System is cooling at this time.
Tune up flowery branch. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel needs to be cleaned. Indoor capacitor needs to be changed. Condensate pan needs to be replaced. No water safety. Outdoor capacitor is within range. Pressures on system are good. System is cooling at this time.
A/c diagnostic Flowery Branch: we inspected system and diagnosed a faulty capacitor on the condenser. Replaced capacitor on condenser and checked the remainder of the complete system. All other aspects of the system are functioning properly and cooling well.
Tune up flowery branch. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Filter is clean. Drain line is clear. Outdoor capacitor is within range. Pressures are within range. System is cooling/heating at this time.
A/c diagnostic in Flowery Branch, unit located in the basement. found emergency pan filled with water, checked evaporator coil, coil is really dirty and rusted, also found a leak on the bottom left side. Evaporator coil has a metal drain pan that is rusted. Blower wheel is really dirty, unit is old R22. Condensate drain tubing is old and needs to be replaced.
Ac service in Flowery Branch. Discovered failed secondary controller. Replaced controller and installed compressor saver. System operational at this time but will need to be replaced in the near future.
No cool flowery branch. Customer called due inadequate cooling and said the line going from the outdoor unit to the indoor unit was frozen. Coil was thawed out when I got here so I did a leak search on the evaporator coil and found a leak. Recommend replacing the coil. Indoor capacitor is within range. Blower wheel is clean. Drain line is clear. Changed filter. Outdoor capacitor is within range. Compressor is still good. Pressures are low due to leaking evaporator coil.
Ac service in Flowery Branch. Discovered clogged filter, failed blower motor, and frozen system. Need to order motor on Tuesday.
Ac service in Flowery Branch. Tested system operation and system operation normal at this time. Homeowner concern with upstairs zone not turning system on. If problem persists may need to replace tstat and zone board
Ac service in Flowery Branch. Installed hard start kit to reduce stress on compressor. System operation normal at this time.
A/c diagnostic in flowery branch, checking 2 units in the attic. 1st unit indoor unit is running but not the condenser unit, found bad secondary motor controller. 2nd unit has a bad blower motor.
Ac service in Flowery Branch. Adjusted master bedroom thermostat offset. Homeowner needs restock of pure air x filters. Need to order and deliver. Collect on delivery.
A/c maintenance in flowery branch. 4 system maintenance, 1st unit is located in the attic. Blower wheel is clean, evaporator coil is clean, flush drain line, changed filter. System is cooling at this time. 2nd unit is in the attic. Blower wheel is clean, evaporator coil is clean, drain line was flushed, changed filter. System is cooling at this time. 3rd unit is in the basement, blower wheel is clean, evaporator coil is clean, flush drain line, changed filter. System is cooling at this time. 4th unit is in the basement, blower wheel is clean, evaporator coil is good, flush drain line, changed filter. System is cooling at this time.
Tune up flowery branch. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Filter is clean. Drain line is clear. Indoor capacitor is within range. Outdoor capacitor is within range. Pressures are within range. System is cooling at this time.
Need to rebuild the supply plenum for the upstairs system. When doing so we need the correct the duct placement on the plenum. Each run will have manual dampers. The longer runs will be placed closer to the top while the shorter runs closer to the bottom. ALL connections need to be sealed completely. Once ducting is corrected, I will make setting and refrigerant adjustments. Need to schedule a carpenter to address the attic stairs. They are offset and the molding needs to be replaced or corrected and painted.
Outdoor system is reading error code â€œopen start circuitâ€, checked run capacitor and run capacitor has failed. Replaced fun capacitor and system started properly. Let system run for 30 minutes with no fault.
Tune up flowery branch. Did a leak check on evaporator coil. Did not find any leaks. Filter is clean. Drain line is clear. Blower wheel is clean. Capacitor on indoor is within range. No cracks in heat exchanger. Capacitor on outdoor unit is within range. Compressor is good. Pressures are within range. System is cooling at this time.
Ac service in Flowery Branch. Discovered melted wires in outdoor unit. Failed secondary controller and compressor starter. Repaired wires and replaced controller,starter, and main electrical switch. System operation normal at this time.
No cool in Flowery Branch. Found a failed outdoor dual run capacitor. Replaced the capacitor, system started. Recommend replacing AC and Coil due to age and condition.
Ac service in Flowery Branch. Discovered failed condensate pump over flowing. Also discovered systems evaporator coil leaking refrigerant. System Is 15 years old and replacement is HIGHLY recommended over repair due to repair cost. Replaced pump as it would have to be replaced anyway. Need to follow up on issue with evaporator coil.
Tune up flowery branch. Cleared drain line. Changed filter. Checked evaporator coil for leaks. Did not find any leaks. Blower wheel is clean. Outdoor capacitor is within range. Pressures are within range. Customer wanted to get on the maintenance plan. Need to schedule an appointment 6 months out.
Maintenance flowery branch. Did a leak check on both Evaporator coils. Did not find any leaks. Drain lines are clear. Changed filters. Blower wheels are clean. Indoor capacitors are within range. Outdoor capacitors are within range. Pressures are within range. Both systems are cooling at this time. Changed out customers two thermostats with new google nest thermostats.
Water leak in flowery branch. Drain line was still a bit clogged. Also pvc pipe is sweating had to insulated a little bit. System is cooling at this time. Drain line was flush and clear. Outside drain now has a constant stream of water.
Customer mentioned noise that seemed to be coming from the outdoor AC system, described noise as a kind of grinding or humming sound. No noise was present during inspection. Reset both the outdoor and indoor system several times with no fault. Blower wheel is clean with no obstruction. Contactor for heat strips and indoor transformer are light humming, but that is to be expected. 20x25x5 air filter has some debris across it but not enough to cause major restrictions. Return side fins of the evaporator are clean with no restriction. Tested condensate pump and the motor is not loud. Drain is clear. Ducts are in fair shape, some debris buildup. With system running our pressures are in good condition (80Â° ambient) 116/310 with a 7.5Â° subcool. Manufactured calls for +/- 10Â°. VSAT is at 38Â°. Superheat is a cool 22Â°. The outdoor coil is clean. Defrost board is operating properly and not sending system into defrost. Reversing valve is transitioning smoothly without any fault or major nois