The residents of Duluth, GA have considered Comfort Control a dependable company for cooling and heating services since 1992.
Read how we provide top quality cooling and heating practices and continue to earn five star reviews in the Duluth, GA area.
for Duluth, GA
DANIELA - Duluth, GA
Reece was super profesional and found the problem with my furnace right away. I felt comfortable with him being in my home.
Colleen - Duluth, GA
All the reps / tech that was at my house installing 2 AC units were very professional
Colleen - Duluth, GA
TOM - Duluth, GA
Patrice - Duluth, GA
Reece was very helpful and got my system repaired and running. He was patient with me and explained well as he answered my questions.
JERRY - Duluth, GA
Always timely, polite, and knowledgeable
Great service and experience!
Jason - Duluth, GA
Garrett was great. Really enjoyed his expertise, courtesy, and cleanliness.
Great service! Technician was excellent!
Jason - Duluth, GA
TOM - Duluth, GA
One time and helpful
Tim - Duluth, GA
Stephen - Duluth, GA
Great service! Answered all of my questions. Sent me a quote for additional service (like he said he would)!
He is alright
Ged - Duluth, GA
He is alright..knows what he is doing..thanks
Great service by a great technician!
TRACY - Duluth, GA
Reece was awesome! He was prompt and took care of the issue in a short turnaround time. He was personable and nice. Great job!
ROSE - Duluth, GA
Mark - Duluth, GA
Provided thorough, detailed explanation
On time arrival. Great service. Timely completion
TOM - Duluth, GA
Linda - Duluth, GA
Great service always
Well pleased with price. Service was outstanding.
JACK - Duluth, GA
Reece Wilson was well trained in the situation I found myself in when working with my Total Home Protection service policy. He was easy to talk to and able to explain what was going on and thoroughly answer my questions.
Steve Austin - Duluth, GA
The tech kept me informed about arrival time and system condition. Very knowledgeable.
He's the best!
EVE - Duluth, GA
Reece is prompt, professional, and courteous! He is very thorough and knowledgeable. Does well explaining things where you can understand. Always a pleasure to do business with 🙂
Yvonne - Duluth, GA
Great service and very friendly
Patrice - Duluth, GA
Ta Kim was very knowledgeable and took the time to explain everything to me then answer my follow up questions! He was also very pleasant! So happy to have a warm home again! Will definitely continue doing business with Comfort Control!
GERARD - Duluth, GA
David - Duluth, GA
he called to see if he could come early,which was good,was very polite and seemed to be very efficient!thanks😁
TRUPTI - Duluth, GA
No heat in Duluth, arrived on site to new install found gas cock off, turned gas on to system and tested heat cycle. Unit is operating normally at this time
Heating maintenance one system Duluth. Arrived on site, checked electrical connections,amp draw and capacitance. Checked ignition system and filter. No issues present at this time. Installed surge protector for furnace.
Casey had reported crack inside furnace on backplate area connected to heat exchanger. Confirmed damage. Blower wheel is very dirty and ductwork is too. Recommend replacement of furnace and duct cleaning.will apply diagnostic fee towards installation
Ac service in Duluth. Discovered condensate pump safety had system shut off. Shook pump and realigned top with base and system came on. Added bleach to lime to kill mildew build up in pump. System cooling at this time
2 Ac coil replacements in Norcross
Ac service Duluth. Completed diagnostic. Found system frozen on arrival. System is leaking r22 Freon. Customer had it filled 2 months ago and has already leaked out to the point of freezing. System 17 years old. Ac and coil need to be replaced. Having jim come out to give quote.
Ac service Duluth. Completed diagnostic. Found bad condensate pump. Replaced pump. Required pump. Tested pump. System cooling properly at this time.
Thermostat failure in Duluth. Found intermittent Icomfort thermostat failure on main level system. Will need to replace under warranty.
Warranty no cool Duluth Arrived on site, found upstairs system not cooling, outdoor unit throwing code for open start sequence. Checked and found bad capacitor. Changed capacitor and tested system, unit is operating normally at this time
No cool main level air conditioning system in Duluth. Find Trane system tripped breaker due to stress compressor and weak starter. Find 26 year old Trane system with burnt and damage wire and connector. Repair wire for customer, replace starter kit and capacitor. Find upstairs 14 year Trane system with weak starter kit and damage line wire and burnt capacitor wire. Replace starter kit and repair burnt wire for customer. Find office 3 year old Amana system operating within manufacturer spec. Replace media filter 16x25x5 and APCO UV bulb. Clean both Tran electric air cleaner. All 3 system operating at this time. Sign 3 CCI plan and complete 3 cooling pm check. Customer have $50 off discount
No cool in Duluth for Amana system. Find air conditioning system fail due to bad capacitor. Replace capacitor under manufacturer warranty. Find system operating without hard start kit, suggest to install. Find main electrical switch worn/pitted. Find system in attic, system operating with low insulation in attic and R4 ducts system with poor runs. Air conditioning system operating at this time. Customer want to wait til spring visit to replace main electrical switch and hard start kit.
3 system heat maintenance in Duluth. Tested all components and combustion on 3 Lennox furnaces. All components and combustion tested within normal manufacturing spec. Changed filters. Recommend drain line water safety for master system and ultraviolet systems for all 3 units to maintain indoor air health and combat mold and virus growth. All systems heating normal at this time
Complete tune up special on Rheem air conditioning system in Duluth. Check and find ac unit not operating due to tripped breaker. Reset breaker and ac unit operating at this time. Find wrong size starter kit and capacitor getting week. Need to replace to help system run smoother. Give customer estimate to repair. Change 2 16x25x1 filter for customer.
Ac repair in Duluth. No cool main level discovered failed secondary controller and weak compressor starter and system locked out on high pressure. Replace components and reset system. Tested pressure and pressures are good. System cooling at this time. Homeowner did not want anybody in home so could not look at indoor unit
Complete air conditioning tune up special for 15 year old Trane system in Duluth. Did not change filter, check safety and operations. Find drain system not run properly and not up to code. Find system missing inline water protection. Find ac unit operating with no starter kit and contactor have minor pitted and worn. Give customer estimate to repair worn parts and redo drain system.
No cool on Amana air conditioning system in Duluth. Check and find 2 year old system with faulty capacitor. Replace capacitor under manufacturer warranty and labor warranty. No charge to customer. Test and system operating with in manufacturer spec. Replace 16x25x1 filter for customer. Suggest comfort control member club plan to help with system maintenance and cleaning. Suggest surge protection for outdoor system and suggest start assist kit.
Complete 2 Tune up special for both air conditioning system in Duluth. Find both amana equipment operating with in manufacturer spec. Filter dirty and need to be replace. Check drain, system safety and operations. Suggest more insulation in attic to help with house energy efficiency, suggest surge protection for both outdoor system. Suggest air purifier system to improve air quality and prevent molding. Sign 2 CCI plan and complete ac maintenance, Level outdoor unit and replace 2 20x25x5 Ultravition media filter.
Thank you for your business! Gavin & mark
Thank you! Gavin and Mark
Water leak call. Found system with low r22 levels causing coil to freeze and water to leak out. System is from 1998 and has a refrigerant leak. Due to age and condition of system, recommend upgrading system to a more reliable and more efficient system. Customer just wants to recharge system for now and understands refrigerant will leak back out and that thereâ€™s no guarantee on how long it will last. Added 1.5 lbs r22 into system. System is cooling at this time.
Arrived on site, found system a lb low on 410a. Cleaned blower motor assembly (presold) and charged unit to manufacturer spec. System is operating normally at this time.
Found upstairs supply duct to have fallen off of supply plenum. Reattached duct. Signed customer up for one system maintenance plan and performed cooling maintenance. Found system with blower motor capacitor starting to go bad, recommend repair. Changed filter. Chemically washed condenser coil. Replaced blower capacitor. System is cooling at this time.
1 system ac pm check complete. Changed filter. Tested mechanical and electrical components, all in good shape. Changed uv bulb. System is cooling normal at this time. Thank you so much for your business today! It is greatly appreciated! Its customers like you that keep us in business and keep our families taken care of! If you were happy with your service today and you wouldnt mind, please take a few minutes to give us a 5 star review on google! All you have to do is go to google.com and sign into your google account. From there, search for â€œComfort Control Heating and Airâ€. Click on â€œReviewsâ€. Write your review mentioning us, Reece Wilson and Jon Fowler and please be sure to leave 5 stars! Thank you so much and have a great day!