Family Owned HVAC Service Company
Buford, GA has turned to Comfort Control Heating & Air since 1992 for professional AC repair and heating service including HVAC installations and maintenance. Need a new air conditioning or heating system? How about a more energy efficient HVAC system?
Count on Comfort Control Heating & Air for all your air conditioning repair service needs 24 hour a day.
HVAC Service FAQs
It costs around $150-$350 per year to have your air conditioner serviced in Buford, GA. Getting your air conditioner serviced has many benefits such as:
- Your AC unit lasts longer.
- Your AC unit breaks down less.
- Your AC unit requires less repairs.
If you get your air conditioner on a maintenance plan, your energy bills will be lower and your air conditioner will be covered under warranty. To find out more about getting your air conditioner serviced, call us today.
AC repair service usually costs about $350-$600 in Buford, GA. However, the price can vary depending on:
- The cost for replacement parts.
- The type of repair.
- How extensive the repair is.
In some instances, the cost of the repair can also fluctuate depending on the age of your AC unit since some older AC units use parts or require refrigerant that are harder to obtain now. To get your AC unit repaired, contact us today.
A few signs your indoor air is clean in your Buford, GA home are:
- You do not have increased allergies while at home.
- You are comfortable in your home and do not experience dry nose, throat or eyes.
- You do not notice excess dust in your home’s indoor air.
These are a few signs that your indoor air may be clean. However, there are some other signs of poor indoor air quality that would require a test of your indoor air quality. To learn how to improve your indoor air quality, call us today.
It should cost around $1,000-$3,000 to have a water heater installed in Buford, GA. Some of the things that can affect the price include:
- The type of water heater you want installed.
- The size of the water heater you want installed.
- The contractor’s hourly rate.
Getting a new water heater installed is a great way to save money on energy as well as to ensure that you consistently have access to hot water. To get a water heater installed in your home, call us today.
Yes, an HVAC service plan is worth it in Buford, GA. Some of the benefits of HVAC service plans are:
- Your monthly energy bills are lower.
- Your HVAC system lasts longer.
- Your HVAC system is covered under warranty.
When you get your HVAC system on a service plan, your HVAC system will also break down less and require repairs less frequently. To find out more about getting your HVAC system on a service plan, contact us today.
HVAC maintenance typically includes the following in Buford, GA:
- A thorough cleaning of your HVAC unit.
- An inspection of your HVAC unit.
- A lubrication of your HVAC unit’s parts.
- A replacement of your HVAC unit’s air filter.
If you get your HVAC system on a maintenance plan, you may also get discounts on repairs and service calls depending on your HVAC contractor. To learn more about getting your HVAC unit maintenanced, give us a call today.
Local HVAC Contractor Service Reviews
Check out the reviews below and see how we deliver air conditioning repair and heating service that residents of Buford, GA turn to us for again and again.
for Buford, GA
Honest and reliable
Abby - Buford, GA
EDDIE - Buford, GA
Excellent service. Always appreciate the folks at Comfort Control!
Easton - Buford, GA
John is awesome.
Gary - Buford, GA
Showed up on time did some troubleshooting tested the system and a tune up . Very fair price and the young service man was very nice !
Renee - Buford, GA
Alex is the best Technician EVER! Very knowledgeable and great personality. He did a great job getting us up and running and we are VERY appreciative. You have a very valuable employee. Thanks again.
PATRICIA - Buford, GA
Thank you for quick, honest service on a crazy hot summer weekend!!
Thank you Jeff..!!
ROBERT - Buford, GA
Great service and great price.
Karen - Buford, GA
On time and fixed the problem quickly for a great price.
Dolores - Buford, GA
Gentlemen went right to work. Very polite and respectful. Made sure things were working correctly before leaving. Will use them again.
Excellent timely service
Pete - Buford, GA
Jon Fowler called in advance, quickly diagnosed the issue, brought the repair option/cost to me, and then immediately solved the problem.
Mario - Buford, GA
Corliss - Buford, GA
Awesome service. Technician very knowledgeable and pleasant.
They saved the day!
Atherstine - Buford, GA
My air went out and I did a quick online search. I found Comfort Control and was impressed by the 4.9 rating as well as all the great reviews. I can attest that they are all true! I was able to get same day service when others were booked out for weeks. The prices were reasonable and the service is impeccable!! Ricky was so personable and efficient.
Above average service.
Min - Buford, GA
Efficient and issue resolved quickly
Rashad - Buford, GA
Tamara - Buford, GA
Jazmine - Buford, GA
Glad I called this company, they were very informative and professional.
MISTY - Buford, GA
Mary - Buford, GA
Alex was great. Fixed the problem
Tammy - Buford, GA
Appreciate the prompt professional service.
BOB - Buford, GA
It was great service all round
WILLIAM - Buford, GA
Awesome,tech was professional
Mark - Buford, GA
Outstanding service tech! Upheld the standard in every way. Your company should be proud to have him
Timothy - Buford, GA
This young man has been out to our house twice now and he upholds the standard in every way. Would welcome him back anytime so grateful we got someone like him! Thank you!
Excellent customer service!
Dana - Buford, GA
From my initial phone call to the on-site service, I received excellent customer service! Great overall experience!
A/c diagnostic in Buford. Replaced indoor unit main board, Bluetooth control. System has a bad 12 inch zone damper and needs a coil sensor/Plenum sensor. Provided quote to the customer for those items. Customer wishes to speak with Jeff Schmitt before agreeing to any more costly repairs.
Carrier Greenspeed 4 ton with zoning Supply Plenum 16" damper 12" damper Infinity zone controller Infinity UI Infinity zone sensor
Maintenance Buford. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Changed filter. Drain line is clear. No cracks in heat exchanger. Outdoor capacitor is within range. Compressor is good. Pressures are within range. System is cooling/heating at this time.
A/c diagnostic in Buford, unit is located in the crawl space condenser unit is old R22. Tempstar horizontal left hand 75,000btu 3ton slab coil with a 12â€ transition with metal supply, low voltage wire from unit to condenser needs to be replaced. Load center is Cutler-Hammer (pics attached).
Ac service in Buford. Discovered clogged drain line, furnace pan in horrible condition and needs to be changed, due to the age of the furnace replacement of it is HIGHLY recommended as well.
ECM condenser fan motor under part warranty. Rheem/Rudd. 15PJL36A01. Will be out of town until next weekend.
Replaced furnace control board. System operational at this time
Ac service in Buford. Discovered out fan motor failing, secondary motor weak and outside of manufacturing spec, system needs compressor saver to reduce stress on compressor, and system needs outdoor coil cleaned.
Ac service in Buford. Discovered loose wire in furnace preventing outdoor unit from coming on. Corrected and system cooling at this time
A/c diagnostic in Buford. 2 zones Unit located in the attic. System is cooling at this time, found zone 2 for the bedroom not operating properly and not opening. Found aluminum tape wedged in between the shaft not letting damper opening. Fixed problem, turned dampers OFF AND ON 3 times and they are now opening and closing at this time.
Ac service in Buford. Discovered dirty filter and weak blower motor controller. Removed filter and tested system operation. System operation normal at this time. Also discovered organic growth inside indoor unit. Recommend installing ultraviolet light system to combat organic and viral growth in system and throughout the home.
Ac service in Buford. Verified leak.
Complimentary duct cleaning
16 seer 2.5 ton horizontal heat pump system 10 year parts warranty 10 year labor warranty Lifetime outdoor unit replacement compressor warranty Supply plenum Return plenum Nest pro thermostat
Ac service in Buford. Discovered damaged low voltage wire at outdoor unit. Replaced section of wire and communicating voltage normal now. Cleared all fault codes. Spoke with Matt and system should be fixed now. System operation normal and is cooling.
A/c diagnostic in Buford. Unit is located in the garage, indoor unit is running but not the condenser, found bad secondary motor controller. Blower wheel is clean, evaporator coil is clean, drain line looks good, Filter needs to be changed. ( Donâ€™t have filter size in stock at this time.) system is cooling at this time.
Not cooling. Found melted disconnect to the outdoor unit. Replaced disconnect under 10/10 warranty.
Tune up Buford. Did a leak check on all three evaporator coils. Did not find any leaks. Main level and upstairs indoor capacitors are weak. Recommend changing those soon. Basement capacitor is within range. All three blower wheels are clean. Changed filters. Cleared drain lines. No cracks in heat exchangers. All three outdoor capacitors are within range. Pressures on all three systems are within range. All three systems are cooling at this time.
A/c diagnostic in Buford. Customer stated return had a pulsing loud noise, reduce fan speed to medium noise is gone. System is cooling at this time. Pressure are good.
A/c diagnostic in Buford. Unit is located in the attic. Customer is listing the house for sale. Inspector said ceiling has a bit of water stain on the drywall from one of the supply vents do to the condensation. Went up to the attic and supply flex tubing is properly sealed and insulated, supply vent is sealed to the ceiling. Vent is right next to the window making vent have condensation from the cool supply air and the heat from the window.
Ac service in Buford. Discovered failed compressor tripped breaker. Due to age, system needs to be replaced. Homeowner to reach out to home warranty
A/c diagnostic in Buford. Unit is located in the basement. Found drain pan full of water and condensate pump full and clogged, water level triggered safety switchâ€™s shutting off unit. Cleared out water and flush drain line, and cleaned condensate pump. System is cooling at this time. Refrigerant pressures are good.
Ac service in Buford. Replaced blower motor, wheel, and housing on righ furnace. System operation normal at this time
A/c call back in Buford. Drain line was clogged, also had to rewire safety switchâ€™s. System is cooling at this time. Pressure are good.
2014 Rheem AC was frozen over yesterday, upon arrival Mr. Clay has had the AC shut off to thaw out. No freezing occurring on outdoor when system is turned on. Suction pressure is very low indicating a possibly bad metering device (86/320). Vapor saturation is low, 24.8Â°. Outdoor coil has a lot of debris built onto it. Super heat is high, 38Â°. Indoor coil is leaking refrigerant and the TXV is blocking not allowing enough Freon to move past it. Did not charge diagnostic due to customer moving forward with repair. Mr. Clay is replacing coil and we will need to order and come install.