Top Rated Cooling Repair Service
Buford, GA has turned to Comfort Control since 1992 for professional AC repair and heating service including HVAC installations and maintenance. Need a new air conditioning or heating system? How about a more energy efficient HVAC system? Count on Comfort Control Heating & Air for all your HVAC service needs 24 hour a day.
HVAC Service FAQs
It costs around $150-$350 per year to have your air conditioner serviced in Buford, GA. Getting your air conditioner serviced has many benefits such as:
- Your AC unit lasts longer.
- Your AC unit breaks down less.
- Your AC unit requires less repairs.
If you get your air conditioner on a maintenance plan, your energy bills will be lower and your air conditioner will be covered under warranty. To find out more about getting your air conditioner serviced, call us today.
AC repair service usually costs about $350-$600 in Buford, GA. However, the price can vary depending on:
- The cost for replacement parts.
- The type of repair.
- How extensive the repair is.
In some instances, the cost of the repair can also fluctuate depending on the age of your AC unit since some older AC units use parts or require refrigerant that are harder to obtain now. To get your AC unit repaired, contact us today.
A few signs your indoor air is clean in your Buford, GA home are:
- You do not have increased allergies while at home.
- You are comfortable in your home and do not experience dry nose, throat or eyes.
- You do not notice excess dust in your home’s indoor air.
These are a few signs that your indoor air may be clean. However, there are some other signs of poor indoor air quality that would require a test of your indoor air quality. To learn how to improve your indoor air quality, call us today.
Local HVAC Contractor
Check out these reviews and see how we deliver air conditioning and heating service that residents of Buford, GA turn to us for again and again.
for Buford, GA
Nicole - Buford, GA
JOHN - Buford, GA
Always professional and listen.
WAYNE - Buford, GA
TERRANCE - Buford, GA
Vu Tran was very knowledgeable and very professional..
GREG - Buford, GA
CHRISTINE - Buford, GA
Reece was very knowledgeable and was very thorough with his explanation of services performed
Mark - Buford, GA
Tech was excellent and informative very thorough.
Blanca - Buford, GA
Attention was nice, I wasn’t able to get everything I wanted done because it was too pricy. 264.00 to change a switch, another 200 to change a sensor. I was also not happy with the fact that I got charged 3% for paying with a card or I could pay with check. Who pays with checks now in days? Luckily I have one from like 10 years literally.
STEVE - Buford, GA
On reason I call Comfort Control first is the expert they send out to discuss the job, provide recommendations and a resolution. There is no sales pressure and we have a very comfortable discussion. The second reason is the service is exceptional and timely. All good
Fixed our problem quickly
Joel - Buford, GA
Gas Leak Fixed!
Jordan - Buford, GA
Carrie - Buford, GA
chris did an amazing job. efficent work, good summary and great recommendations for how we can improve
Deanne - Buford, GA
Reese is very thorough and knowledgeable and communicates very well.
Brendan - Buford, GA
Brian was well prepared and well versed in his craft. He understood my issues and has a roadmap created to resolve them. He took care to listen and understand before making suggestions. Great team member you have!
Great/Awesome service and explanation of what actually can be done, and what needs to be done.
MISTY - Buford, GA
Was good to find out that the attic is accessible enough so that the duct can be cleaned. Obviously zerorez didn’t want to perform the work. Nice to know that comfort control is working diligently to rectify this problem and get the service completed. Comfort control has been nothing but professional and respectful from the start. We are more than happy to give them glowing positive performance reviews and recommend their services to people we know.
Great prompt service
Debbie - Buford, GA
Chris is very professional and knowledgeable. He offered some recommendations but did to push me into making any rash decisions. I highly recommend Comfort Control
Great customer service!
Debbie - Buford, GA
Garrett arrived on time and inspected the attic and the area where I need to put the heating/cooling unit. He proceeded to the garage to check out the panel box and looked outside where the outside unit will go. He actually called Jeff for another opinion to give me the best and most aesthetic installation possible! After taking all the measurements, Garrett went over the different units, the pricing, and the finance options with me. He answered all of my questions as was very respectful and patient while I made my decisions. Thank you, Garrett for all of your help. I can’t wait to have it installed!
Great customer service!
Debbie - Buford, GA
Reece was on time, very respectful, and polite. He checked out the system, made a few recommendations, and answered all of my questions. Job well done! Thank you, Reece.
Detailed inspection, great customer service!
ELYSSA - Buford, GA
Reece provided me with a thorough and detailed inspection. He answered all questions I had and was incredibly knowledgeable. Thank you!
Juliette - Buford, GA
Very professional knowledge
Great customer service
Debbie - Buford, GA
Reece was on time, polite and respectful. He checked out the system, made recommendations and answered all of my questions. Thank you Reece. Well done!
Great customer service!
Debbie - Buford, GA
Reece shoes up on time, checked out the system, answered my questions and made some recommendations. He was courteous and respectful!
Good service at a good price.
Diane - Buford, GA
I wasn’t home but my daughter said it went well.
Another great experience with Comfort Control
Ray - Buford, GA
Chris was fantastic. Very knowledgeable and got my unit back going.
KENDAL - Buford, GA
We were in the process of selling our home, our AC wasn’t working, I called Comfort Control and Chris came out that same day to find the problem. The problem was fixed in a timely manner. Costumer service from the office to the technician was great! Would absolutely recommend Comfort Control and will use them again as needed. Thank you!!!
No heat in Buford. Check and find 2 year Amana heatpump unit fail due to low charge. Find accumulator leaking charge. Need to order from manufacturer. Heatpump off at this time. Part will be in by next week Thursday.
Hvac maintenance in Buford, Georgia. One system. Changed filter. Tested mechanical and electrical components, all in good shape. Found blower wheel to be dirty. Uv bulb needs to be replaced. Components are in good shape. Systems is operating normally at this time.
Buford new install
No cool Buford. Completed diagnostic on upstairs 15 year old system. Blower wheel is dirty air flow is restricted mostly from filter. Recommend electro static filter to cut down restriction and better filter air and keep system cleaner longer. Capacitor is good. Door switch working. Evap coil does have concerning amount of rust. Temp difference is 17.4 from return to supply. Cooling good. System has no water safety attached. Outdoor system has all components working within manufacturing spec.
No cool Buford. Completed diagnostic. Found system with locked compressor on high pressure. Reset system. Pressures are good. Electrical components inside heat pump working within manufacturing spec. Air handker has rusted coil. Dirty blower wheel and weak capacitor. Customer has to get with landlord about approval for repairs.
Heating tune up Buford. Completed tune up on 4 year old system. System heating properly. Missing secondary water safety device. Heating elements working. Blower and coil clean. Zoning equipment working. Pressures are good. All electrical components are working. Recommend inline float switches and surge protectors for both units. Installed all. Recommend air quality treatments to system to better clean air in house.
6 system tune up in Buford Georgia. Did not change filters. Tested mechanical and electrical components. Found leak in right upstairs evaporater coil. System runs on r22 refrigerant which has been phased out by the epa in 2020. Due to age and condition of system, recommend upgrading system to a more reliable and more efficient system. Found right main level blower capacitor to be weak (15uf). Found evaporator coil to be rusty, corroded and therefore likely to leak. Found electrical pitting present on main electrical switch. Due to age and condition of system, recommend upgrading system to a more reliable, more efficient system. Found right basement system blower capacitor to be weak (15uf). Recommend repair. Found left upstairs evaporator coil to be rusty, corroded and therefore likely to leak. Found left main level evaporater coil to be rusty, corroded and likely to leak. Found blower capacitor to be weak (15uf). Found dual capacitor to be weak (55/5uf) and leaking oil. Fo
Three system tune up in Buford. Arrived on site, changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found main level evaporator coil corroded, has high potential to develop a leak in refrigerant system. Both main and basement unit have burnt and pitted contactors that should be replaced as well as installing a secondary form of water safty. Recommended installing compressor assist kits as well as surge protectors to each unit. All units are operating normally at this time
Free consultation Buford Georgia 30518
Heat pump maintenance in Buford Georgia. One system. Changed filter. Tested electrical and mechanical components. Heat strips not operating due to bad sequencer. Found evaporator coil corroded, rusty and dirty. Likely to leak and restrict air flow. Bad blower capacitor. Blower wheel dirty. Only one form of water protection and no emergency drain pan. Found bad capacitor on heat pump and overheating compressor along with probable refrigerant restriction as previously stated. Found electrical pitting on main electrical switch. Found line set insulation in bad shape. Due to age and condition of system recommend upgrading to a more reliable and efficient system. System is not operating properly at this time.
One system hvac tune up in Buford Georgia. Main level system. Changed filter. Tested mechanical and electrical components. Found evaporator coil to be rusted and corroded and likely to leak. System runs on R22 which is a refrigerant that has been phased out by the epa. System is from 2008. Due to age, condition, and lack of efficiency, recommend upgrading system to a more reliable and more efficient system. System is operating at this time.
Heat pump maintenance in Buford Georgia. One system. Changed filter. Tested mechanical and electrical components, all in good shape. Changed apco uv bulb. Flushed water heater. Recommend installing pureairx air purifier for improved air quality and pureairx electronic filter as well. System is heating normally at this time.
Heating maintenance Buford. Completed maintenance on 7 year old system. Air flow is slightly restricted from filter. Recommend installing electro static filter to better filter air as well as achieve optimum air flow. Combustion is good. Blower and coil are clean. Electrical components are working within range. System has no back water safety device to protect furnace from water damage. System would also benefit from having UV light treatment installed to kill bacteria viruses and chemicals in air that could cause harm to residents.
Heating tune up Buford. Completed tune up on 22 year old furnace. Blower is dirty ignitor is very worn. Flame sensor is good. Water safety switch working. UV light bulb needs to be replaced. Gas valve is leaking at shut off. Needs to be replaced. Gas line is not ran to utilize sediment trap. Need to re run to protect gas valve. System needs to be replaced due to age and repair price. Customer not interested in replacing at this time. Will cal back about repairs.
Heating tune up Buford. Completed tune up on 2 5 year old systems. Both heating good. All heating elements clean and within range. Blower and coil on both are very clean. Filters are good. Both systems have working water safety switches. All electrical components working in range. Both systems would benefit from having surge protectors installed to prevent smaller electrical components from failing. As well as downstairs system needs UV light like upstairs.
Furnace maintenance in Buford, Georgia. Checked all electrical and mechanical components. Found evaporator coil to be rusty and corroded and therefore likely to leak. Found dirty blower wheel. System has no water protection. System has no surge protection. Furnace is 21 years old , recommend upgrading system to a more reliable and more efficient system. System is heating at this time.
Heat tune up Buford. Completed tune up on 11 year old system. Inducer motor is failing. Bearings are giving out causing it to overheat. Roll out switches are rusted and could possibly stick when activated. Blower wheel is very dirty which is reducing the air flow a lot. Filter is good. Gas line is ran properly. Safety switch is working. Flame sensor ignitor and capacitor is good. Due to cost of repair and efficiency of system recommend replacing to a new furnace.
No heat Buford. Completed diagnostic. Found furnace with bad ignitor and flame sensor. Replaced both. System came on. Combustion is good air flow is good. Blower is dirty and capacitor is weak. System also has no secondary water safety device to protect furnace from water damage. System would also benefit from having air quality systems installed to better clean air and kill bacteria and viruses in air.
Heating tune up in Buford, Georgia. Two systems. Check all electrical and mechanical components. Found downstairs unit blower motor capacitor to be weak. Found downstairs unit blower wheel to be dirty. Found no water safety for downstairs unit. Recommend installing two forms of water safety. Downstairs unit not up to code . Has no drip leg on the gas line, and flexible gas line is being run into furnace. Found downstairs evaporator coil to be rusty and corroded, therefore likely to leak refrigerant. Due to age and condition of downstairs system, recommend upgrading system to a more reliable, more efficient system. Replaced blower capacitor for downstairs system. Systems are heating at this time.
No answer at the door
Heating tune up Buford. Completed tune up. Found 2 year old system running good. System is heating properly. Air flow is good blower and coil is clean. All electrical components are working good. System has no secondary water safety switch to protect furnace from water damage. System also would benefit from having UV light system installed to kill bacteria and viruses in air that could be harmful to residents.
Heating tune up Buford. Completed tune up on 2 2 year old furnaces. Downstairs furnace running good. With good air flow clean blower and evap coil. Changed filter. Safety switches working. Electrical components working properly. Upstairs system is all the same except air flow is very restricted. Not enough return air for the upstairs. Recommend adding return to computer room. Customer wants to do it. Will call to schedule.
Hvac tune up in Buford, Georgia. Three systems. Tested mechanical and electrical components. Found upstairs furnace with weak flame safety sensor. Found upstairs system with only one form of water protection. Found upstairs system with rusty, corroded evaporater coil likely to leak refrigerant. Upstairs static pressure is a little high on supply side, recommend changing registers out with high flow registers to reduce static. Found master bedroom system with weak flame safety sensor. Master bedroom system has a rusted, corroded evaporater coil that is likely to leak. Found main system with weak flame safety sensor. Found main system with rusty, corroded evaporater coil likely to leak refrigerant. Found main system with weak blower capacitor (5uf). Due to age and condition of systems, recommend upgrading systems to more reliable and more efficient systems. Systems are heating at this time.
Replaced inducer motor under parts warranty. System heating properly at this time.
No heat Buford. Completed diagnostic. Found ignitor and flame sensor both failed. Inducer motor also going bad. Running at much higher amps than rated for. Blower wheel is very dirty and capacitor for blower is very weak. System also has no back up water safety or air purification installed. Due to age and efficiency of system recommended replacing. Having Jom come out to give quote.