Buford, GA has turned to Comfort Control since 1992 for professional cooling and heating repairs, installations and maintenance.
Check out these reviews and see how we deliver air conditioning and heating service that residents of Buford, GA turn to us for again and again.
for Buford, GA
Another great experience with Comfort Control
Ray - Buford, GA
Chris was fantastic. Very knowledgeable and got my unit back going.
KENDAL - Buford, GA
We were in the process of selling our home, our AC wasn’t working, I called Comfort Control and Chris came out that same day to find the problem. The problem was fixed in a timely manner. Costumer service from the office to the technician was great! Would absolutely recommend Comfort Control and will use them again as needed. Thank you!!!
LEROY - Buford, GA
Chris was great and knowledgeable
KATHY - Buford, GA
Prompt, knowledgeable, respectful and informative
Patient & thorough
Jeffrey - Buford, GA
Chris handle our annual fall service appointment with the patience and thoroughness we have grown to appreciate from the service tech's we've worked with over the 18 years we've been serviced by Comfort Control. I ask a lot of questions whenever a technician is in my home. This being now our second home that CC has provided service for, I feel good about the time taken to respond and educate me on HVAC topics and concerns. Chris easily met my expectations, again.
JESSICA - Buford, GA
Christian was great! He knew exactly what he was doing and was very nice! I love comfort control, they really care about their customers!
Excellent Service !
ERNEST - Buford, GA
We really appreciate our HVAC Tech Brian coming to our house so quickly. He dove right in and solved the problem we were having. He always answers any questions we have and explains everything throughly.
Very professional & efficient.
Laurel - Buford, GA
Jordan was punctual, and listened to our concerns.
Stephen - Buford, GA
Your tech was very friendly, and knowledgeable, he works in a timely manner. I would recommend him to all my friends and family members.
CRAIG - Buford, GA
Took care of my issue quickly.
Hyun - Buford, GA
Fast Service - Great Customer Service !!
ERNEST & LARA HAYES - Buford, GA
We have been suffering with furnace issues on the 2nd floor of our house for a couple months, sometimes it (the blower) would work, sometimes not. Mostly not lately. Received a flier from Comfort Control this past weekend and gave them a call. We were able to get a service call scheduled the next day (today). When our technician Brian arrived he dove right into the issue. Turns out it was the motherboard control unit that needed to be replaced. We have an old unit 15 yrs old and decided to go with the repair and wait on replacing the unit at a later date. We can't tell you how good it feels to no be so cold you are in pain. God Bless Brian and Comfort Control !!! We are customers for life !!!
Marlene - Buford, GA
Andrea - Buford, GA
Jordan was very knowledgeable and helpful.
LINDA - Buford, GA
GINIE - Buford, GA
Reece checked the PRV on the water heater and explained it’s function. He then noted the noise was coming from the PRV for water coming into the house and advised me that he was not able to change it. He advised me to contact a plumber. Thank you Reece for your honesty and patience in explaining these things to me.
Excellent Service, Excellent Technician!
EDDIE - Buford, GA
Brian Malone was excellent! Very personable and CC knowledgeable. Absolute first rate visit!
ALICE - Buford, GA
Vu is awesome. He is always professional, polite, courteous and knowledgeable.
Excellent Service Technician
Sharon - Buford, GA
Being pretty sure that it was a thermostat issue we had a replacement thermostat and batteries on hand. The technician confirmed our suspicions and promptly changed out the thermostat and got this system up and running in very short order.
Excellent service and price as always...
CAROLYN - Buford, GA
Mark - Buford, GA
Very good service
Deanne - Buford, GA
Prompt efficient knowledgeable with clear concise but detailed information
Dwayne - Buford, GA
Very pleased with entire procedure
Gary Miners/Arron Pflug - Buford, GA
I'm located in Michigan and had service check done for my daughter and family.She had a post card for your company advertising the maintenance check up I was down in Georgia in October and scheduled Very pleased and will be following up with recommendations
Professional, knowledgeable service
Jackie - Buford, GA
Great service tech, knowledgeable and professional!
Free consultation Buford Georgia 30519
Furnace maintenance in Buford, Georgia. Two systems. Changed filters. Tested mechanical and electrical components. Found upstairs system with no water safety, dirty blower wheel, badly worn igniter, and worn flame safety sensor. Found downstairs system with badly worn igniter, worn flame safety sensor, and dirty blower wheel. Due to age and condition of furnaces, recommend upgrading them to more reliable, more efficient furnaces. Systems are heating at this time.
Renewing maintenance program in Buford Georgia. Completed the heating maintenance today . Checked the safety and performance. Checked integrity. Checked heating elements. Checked amps and motors . Changed air filter . System is heating at this time .
Free consultation Buford Georgia 30519 hvac new system installation
Pre sold repair in Buford. Arrived on site, replaced faulty heat kit, tested system, unit is operating normally at this time
Free consultation Buford Georgia mini split for basement
Giving a estimate on a maintenance program for 4 systems in Buford Georgia . Maintenance includes coming out twice a year . A heating visit and cooling visit . Checking the safety and performance. Checking integrity. Basic cleaning . Was not able to access roof ladder was not long enough. If Accent Fence wants to move forward will get the correct ladder to access the roof top . 3 package units and one hanging heater unit in the warehouse. Will send over price on the maintenance program. â€¢Signing Accent Fence up for the maintenance program. Going to get the ladder . Got a ladder to access equipment on the roof top . Completed heating maintenance. Checked the performance and safety of the equipment. Changed air filters . Checked integrity. Checked amps and motor . â€¢Workshop room . Has a bad ignition board would Recommend replacing that electrical part . Company doesnâ€™t use this system very much . Keeping that system off to prevent further damage to the equipment. â€¢Meeting
Pre-sold repair in Buford. Arrived on site, pumped down system and removed old evaporator coil, replaced with new aluminum coil. Pressure test and pull vaccum to 500 microns to remove moisture in refrigerant system. Charged to manufacture spec. Tested, system is cooling at this time. May need to come back in summer to adjust charge.
Main unit / not working / repaired main level/ performed 2 system maintenance in Buford
Heating issue in Buford Georgia. System was short cycling and tripping the high limit switch. Reset sensor and system is now heating and cycled system several times . Signing the family up for a maintenance program. Office will call and schedule first maintenance visit . Come out twice a year for a heating and cooling visit.
No cool in Buford. Arrived on site. Found heat kit only listing on one side. Split unit only able to keep up with the upstairs system. Will need to call Rheem in morning to find new 10kw heat kit
One system tune up/no heat in Buford. Arrived on site, found system fan continuously blowing due to tripped flame safty switch, reset and inducer motor came on, but pressure switch would not engage. Quoted for a bad pressure switch, but customer declined repair. Closed system up. System currently not operational.
No heat in Buford, arrived on site, found system fan constantly running with call for heat and no flame. Found zone board sending system into high limit in heat mode immediately upon startup. Determined cause to be faulty DATS. Disconnected from zone board and system started working. Will need to replace. Also found mold in system, recommend installing uv purifier to eliminate organic growth inside system
No heat in Buford. Check and find new zone panel was not set up properly. Set zone panel for second stage Aux heat with gas furnace. Tested control system and all 3 new nest tstat operating at this time.
No cool in Buford. Arrived on site to find system low on refrigerant due to leak in evaporator coil. Quoted to replace coil, collected payment and will be back to replace. System is heating at this time, but no AC.
Two system heat maintenance in Buford. Arrived on site,. Change filters and checked heat kits. Checked electrical connections, amp draw and capacitance systems are fairly new and operating without issue. Recommended installing surge protectors for each piece of equipment to protect electrical systems as well as uv purifier to prevent organic growth and improve indoor air quality.
Water heater not heating in Buford, Georgia. Forgot to relight pilot light. Relit it and water heater is heating at this time.
Furnace not heating in Buford, Georgia. Found control board to be bad. Part was under warranty, labor was not. Replaced control board and system is heating at this time.
One system heat maintenance in Buford. Arrived on site, changed filter and checked heat strips. Checked electrical connections, amp draw and capacitance. Recommended installing water safty in attic, as well as an E-Z trap, and uv purifier. Installed overflow switch to system as well as customer supplied EcoBee t-stat. Unit is operating normally at this time
Two system heat maintenance in Buford. Arrived on site, changed filters and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found both systems without water safty as well as having sections of flue pipe that are single wall and not up to code. Also recommend installing uv purifier to system to keep organic growth out of air flow as well as improving air quality in house. Installed primary and secondary water safty each to system. Both units are operating normally at this time.
Heating maintenance Buford. Completed 2 system maintenance on 2 6 year old furnaces. Both furnaces running good. Blowers are clean. All safety switches working. Changed filters. Systems heating at this time.
When I arrived the furnace was heating in Buford Georgia . Cycled the system several times and the system heated . The system is having a intermit issue and not working consistently. Testing other elements now . Found that the pressure switch vent device tripped a couple times causing the heat to stop working . Would highly recommend replacing the heating system due to the old technology thatâ€™s on this machine. Or we could replace the pressure switch vent device and keep the furnace . â€¢Installed new pressure switch vent device . Tested and working at this time . System is now heating . Told the family if this furnace continues to give issues after this repair it will be time for replacement on the heating equipment.
2 system heating maintenance prepaid visit in Buford Georgia . Checked the safety and performance of the heating equipment. Checked the integrity and heating elements. Checked amps .
Free consultation Buford Georgia 30518 hvac furnace
Two system heat maintenance in Buford. Arrived on site. Changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found both systems without secondary water safty switch, surge protection and both of the blower assemblies are dirty and should be pulled and cleaned. Recommend installing uv system to improve indoor air quality and to keep systems clear of any organic growth. Both systems are operating at this time.