Buford, GA has turned to Comfort Control since 1992 for professional cooling and heating repairs, installations and maintenance.
Check out these reviews and see how we deliver air conditioning and heating service that residents of Buford, GA turn to us for again and again.
for Buford, GA
Very courteous and knowledgeable
Jeff - Buford, GA
Roger - Buford, GA
Thankful a repairman came tonight to repair 30 day new HVAC
Camilla - Buford, GA
After purchasing a new Hvac from Comfort Control 30 days ago. I was very disappointed the whole system shut down. But when I called, a repairman was here in 30 minutes. Repairs was quickly done and house is cooling. This is why I choose Comfort, thank you to John for being knowledgeable and professional.
Great job !!!
ELITE - Buford, GA
It was perfect !!!
Very helpful information
Jeffrey - Buford, GA
The efforts by Vu, and especially the time he took to show and explain his findings, concerns and recommendations is very much appreciated.
Great service and extremely thorough
Julie - Buford, GA
Vu Tran arrived within an hour of my call. He pinpointed the issue quickly and got my system up and running. He also suggested what they could do to prevent this issue from happening again.
KEN - Buford, GA
Awesome Job, UV light solved our problems
Super knowledgeable and very confident
THOMAS - Buford, GA
After talking with Garrett, I feel completely comfortable doing business with comfort control. Garrett was knowledgeable and confident with out being cocky, he listen to what I had to say and then gave me great advice.
Haywood - Buford, GA
RACHEL - Buford, GA
Haywood - Buford, GA
John took care of the issues. Great service
Ray - Buford, GA
Unit still now working
GERALD - Buford, GA
Unit is still not working. Stage one the compressor is not coming on
Sharon - Buford, GA
Mark was 100% WONDERFUL!!! I will recommend this company to everyone.
Camilla&Ronnie - Buford, GA
Garrett was very knowledgeable and professional. Great customer service skills
Great customer service, very professional
Camilla - Buford, GA
Great experience, he understood and complied with my social distance requests.
Adam - Buford, GA
Always quick to respond to emergencies and Jon was very helpful in explaining the issue and offering priced out solutions.
Mary - Buford, GA
Boys were efficient and friendly. Gave me good information.
Jose - Buford, GA
I was More than pleased with Jon. He was very professional and took care of everything that I needed done. I will be using comfort control in my new house when I get there because I am so pleased with the service. Jess and Mrs. Tammy were also awesome. Thank you so much.
RACHEL - Buford, GA
DENIS - Buford, GA
Another awesome experience with Comfort Control.
JEFF - Buford, GA
Carrie - Buford, GA
Jon did a really great job and offered some great options for me to consider going forward to take care of my AC.
Mark - Buford, GA
Very good experience
Mark - Buford, GA
â€¢Inducer draft motor port is clogged going to need to remove the motor and clean out the port and blow out the system . Would also highly recommend a maintenance program to prevent this issue from occurring. Family is going with the recommended repair . Took off the draft motor and cleaned it out and also blew out the flue pipe and inside the furnace system . System is now venting properly. Would also recommend with the daughter having allergies would suggest a air purification system to the HVAC equipment to clean and increase air quality along with killing biological growth and viruses in the airstream.
Furnace maintenance in Buford, Georgia. Two systems. Changed filters. Tested mechanical and electrical components, all in good shape. Found gas line drip tâ€™s not up to code, they arenâ€™t long enough. Neither gas line has a gas shut off valve near the furnace and is therefore not up to code. Recommend making gas line tâ€™s longer and adding a gas shut off valve on both gas lines near furnaces. Water safety is code compliant on both systems but neither system has an overflow protection switch. Recommend installing overflow protection switches to help protect furnaces from potential water damage and to serve as a backup to primary water safety switches. Neither system has surge protection, recommend adding on to protect equipment from power surges. Systems are heating at this time.
Ac tune up in Buford, Georgia. Tested system. Found blower wheel to be dirty. Recommend blower wheel pull and clean. System has one form of water safety but no backup. Recommend installing overflow protection switch to protect furnace from potential water damage and to serve as a backup to primary water safety. Found weak capacitor, replaced it. System has no hard start kit, recommend adding on to take a load off of compressor so it starts smoother, runs smoother and therefore lasts longer. Found condenser fan motor over amping. Recommend replacement of motor. Ductwork is undersized, recommend adding more ductwork in for proper airflow and performance, system is cooling at this time. Customer used $35 off coupon.
Heating maintenance Buford. Completed heating maintenance on 18 year old furnace. Inducer is new. Combustion is calibrated and still good. Blower is good and clean. Filters are good. No rust in burners. Capacitor is weak and out of spec. System is heating properly at this time.
â€¢Completed a Three system heating maintenance in Buford Georgia. Checked the heating integrity. Checked safety and performance. â€¢Main level heating system . Certain areas are getting low for the attic insulation. Took pictures, would highly recommend getting the insulation levels to specks for better comfort and lower utility bills . System has old technology with the smart valve / ignition system that could eventually fail due to age . Blower wheel has particle build up which is causing the blower to work harder and decreasing air quality would highly recommend a deep chemical wash on the blower wheel . Took pictures . Would recommend a pan switch on this system to prevent any water from getting on the sheet rock. Biggest concern today with the furnace is the blower amps ... the amps are 11.2 on start up which is double on what it should be a lot of this is to do with the blower wheel being dirty would highly recommend cleaning that housing to help with longevity on the blower m
Looking over a noise issue in Buford Georgia and doing the Heating Maintenance on the HVAC equipment . Line set was touching the rafter in the attic . Added some line set insulation between the rafter and line set to reduce vibration. Took pictures. Also tighten some screws on the outside system and changed the restricted air filter all of this issues can cause noise problems. Also do your best on keeping the air filters changed every 2 to 3 months. Thank you . â€¢Also completed the prepaid heating maintenance today . Checked the heating integrity. Heating elements. Amp draws and combustion levels . - Recommend having a over flow water switch in the attic to prevent water damage to the equipment. - Going to send over a proposal on adding a return into the computer room to help with the comfort in that room .
No cool air conditioning system in Buford. Check and find tstat damage, find evaporator coil in Airhandler very dirty. Give customer estimate to clean evaporator Airhandler and replace tstat, suggest to install UV Light kit to help keep system clean, comfort control inc. maintenance plan and starter kit for heatpump unit.
Inspection on HVAC systems in Buford Georgia . â€¢Unit that feeds the left side has a popped fuse. Took pictures of equipment. Fuse is popping due to chaffing on the outside low voltage wires . Wires are very brittle and bare . Indoor coil is also very rusty and has bacteria growing in the air flow . Also the system I low on R22 pressures. System has a very small leak in the indoor coil . Would highly recommend either looking Into upgrading the equipment or we could charge the system to speck levels and see how it holds off . Also this system doesnâ€™t have a air filter which is horrible for the indoor coil . â€¢Auto shop system has a caked up indoor coil took video . Also the system isnâ€™t sealed properly and pulling the air from the mechanic shop which is causing it to get dirty . System also has lots of rust and potential to leak R22 . Also outside contacter has pit and burn marks would highly recommend replacing that electrical part . â€¢Uvision/It shop . Outside unit has a
Ac service Buford. Completed diagnostic. Found furnace switch was cut off. Flipped switch back on and system came on. Blower wheel clean. Fuse is good. Capacitor is good. Amps in furnace are good. Outdoor unit amps are good. Capacitor is good and pressures are good. System is 15 years old.
No cool both 12 year old Lennox system in Buford. Check and find upstairs system leaking water due to worn secondary drain line rubber. System freezing up and coil water to leak into pan and leaking into ceiling at drain pan connector. Find both Lennox evaporator coil leaks recharge. Find upstairs almost empty of charge and downs stair low in charge and freeing up. Due to system age and conditions. Suggest to replace both Lennox system
Completed the prepaid heating maintenance in Buford Georgia . Checked heating integrity and heating elements . Changed air filter and checked heating temperatures . â€¢Inducer port is clogged going to fix that issue while doing the maintenance. Cleared the clog in the inducer . System is now heating . â€¢UV light bulb needs replacing. Family says they will keep a eye on the bulb . â€¢ The flame reader is weak and reading at 1.5 when it needs to be in range at 2.5 would highly recommend replacing to prevent issues this winter . Family wants to hold off on this repair. â€¢Blower wheel has heavy particle build up and causing a decrease in airflow and making the motor work harder would highly recommend having that pulled out and deep chemical washed . â€¢Duct work design is not very efficient nor is it insulated very well the duct work is older . Would recommend redesigning the air duct system and getting something more efficient to help the house with comfort . â€¢System was f
Ac warranty in Buford, Georgia. Found thermostat popping fuse. Replaced thermostat and system is cooling at this time.
Ac service Buford. Found frurnace not wired correctly. Re wired. System cooling at this time.
No cool on upstairs system in Buford. Check and Find system frozen at evaporator coil in attic. Courtesy melt ice and leak search for customer. Find evaporator leaking at lower right of coil. Give customer estimate to to replace evaporator with CCI plan and hard start kit for compressor.
Warranty visit Buford. Completed diagnostic. Filter was very dirty. Choking up system causing it to freeze up. Replaced filter. Cleared drain line. Pressures are good. System is cooling.
Installed New coil on Buford House boat along with a new inline filter dryer . Pressure tested system after brazing everything in . Flushed system to clean the system internally from debree / trash . Pulled a 420 micron on gauges took pictures. Charged system to speck levels and system is now cooling . Thank you 🙂 . Also customer had a $50 coupon . Service Tech Brian .
No cool on 10 year old carrier air conditioning system in Buford. Check and find damage blower assembly, find blower motor over overheating and blower wheel broken. Need to replace blower assembly. Give customer estimate to repair system. Customer need consultation visit.
No cool Buford, arrived on site to find blower capacitor burnt out and wires arcing inside unit. Recommend replacing equipment due to state of equipment.
Complete heating maintenance on Amana system in Buford. Check and find new heatpump and Airhandler operating with in manufacturer spec. Replace pureAireX 16x20x1 filter customer provided. Upgrade system software on comfortbridge. System operating at this time.
Buford house boat . Found the system low on 410A due to a leak in the system . Going to complete a leak search today . Found leak in the indoor coil on multiple spots along with the tubing on the coil. Going to call the supply house and see about the warranty and availability. Took pictures and videos. Coil will be ordered and hopefully have it by Friday . Total on project will be $1,639 . Includes labor and materials plus vacuum / flush . Will collect when the job is completed . Thank you .
No cool Buford. Arrived on site, found refrigerant pressures low. Charged unit with 5lbs 410a. Will need to come back and assess leak