Braselton, GA has turned to Comfort Control since 1992 for professional cooling and heating repairs, installations and maintenance.
Check out these reviews and see how we deliver air conditioning and heating service that residents of Braselton, GA turn to us for again and again.
for Braselton, GA
By is a great guy. Second time he has helped us.
Jorge - Braselton, GA
He knows HVAC inside and out.
Tom - Braselton, GA
Prompt, knowledgeable, polite, and thorough
Great service and attitude
DEAN - Braselton, GA
Penny - Braselton, GA
Dan - Braselton, GA
Reece always does an excellent job very professional
GERALD - Braselton, GA
Jon is extremely efficient and answers any questions I have.. Would recommend him to anyone for service.
CHET - Braselton, GA
Jon was very knowledgeable and answered all questions.
McCallum - Braselton, GA
I called Comfort Control because I had warm air blowing from my vents. It was late evening on a Friday. They were able to get me in for a Saturday appointment. Reece was the technician who came out. He was prompt to the scheduled appointment time and gave my system a through inspection and gave me some options for the repair. Reece was courteous and professional.
Maria - Braselton, GA
Excellent service. I have no complaints. Everyone we spoke to was polite and very helpful. I will definitely recommend Comfort Control to others.
Sherry - Braselton, GA
Greg - Braselton, GA
Thorough service & terrific rep.!
Tom - Braselton, GA
Chuck - Braselton, GA
Jon Fowler was very professional and answered all of our questions.
Scott - Braselton, GA
Performed routine maintenance on HVAC system, Making sure it is in tiptop shape.
Mary - Braselton, GA
Jon was extremely helpful
RICHARD - Braselton, GA
This company will stay on the job until it’s perfect
Great Presentation. We will buy from you after we resolve a Roof Replacement Situation.
RICHARD - Braselton, GA
Great !!! Wonderful !!!
RICHARD - Braselton, GA
Very well. He was knowledgeable and answered all my questions. Good Technician. An asset to your Company
Sabina - Braselton, GA
Tom - Braselton, GA
Couldn't have been better
Great Customer Service
MENDY - Braselton, GA
Ta was super friendly and very knowledgeable. He explained every single thing he was doing.
Dan - Braselton, GA
Reece did a great job. Very professional. Very friendly.
Dan - Braselton, GA
Awesome Customer Service
Alfred - Braselton, GA
TODD - Braselton, GA
Hvac inspection in Braselton, Georgia. Four systems. Tested mechanical and electrical components. Found upstairs system with no water safety and is therefore not up to todayâ€™s codes. Found upstairs system very low on refrigerant, almost empty. Leak is in the evaporator coil. System is 20 years old and runs on r22 refrigerant. R22 is a refrigerant that has been phased out by the epa in 2020. Upstairs system needs to be replaced. Master bedroom evaporater coil is rusty, corroded and therefore likely to leak refrigerant. Master bedroom system has no water safety and is therefore not up to todayâ€™s codes. Master bedroom system is slightly low on r22. Recommend topping off refrigerant in master bedroom system and installing water safety. Main level blower capacitor is weak (10 mfd). Main level evaporater coil is rusty, corroded and therefore likely to leak refrigerant. Main level has mold present in supply plenum. Main level main electrical switch has electrical pitting present. Main lev
Hvac tune up in Brasleton, Georgia. One system. Changed filters. Tested mechanical and electrical components. Found system with only one form of water protection, recommend adding addition water safety switch in drain line to shut system off as a safety in case drain line backs up. Found system with weak outdoor fan capacitor. Found system with electrical pitting present on main electrical switch. Recommend repair. System has no hard start kit, recommend installing hard start kit to take a load off of compressor so it starts smoother, runs smoother, and therefore lasts longer. Recommend installing surge protection to protect equipment from power surges. System is operating at this time.
No heat in braselton. Check and find 13 year old heatpump and Airhandler. Find Airhandler fuse pop. Replace 3 amp fuse and system operating. Check and find Airhandler evaporator coil badly rusted, and missing inline water protection. Find heatpump operating with weak capacitor, worn contactor and compressor start up stress. Suggest to upgrade equipment. Customer want to wait to til January to call for consultation.
No heat in braselton. Check and find master bedroom gas furnace #3 fail due to fail thermostat. Replace Tstat with nest customer provided and replace upstairs Honeywell tstat customer provided. Test both Tstat and bout operating at this time. Test gas furnace and find gas Lennox 13 year old furnace operating with weak flame sensor, weak capacitor, and under temperatures. Suggest repair for system. System missing in line water protection in attic. Suggest Comfort control maintenance plan.
Wire repair in braselton. Arrived on site, found both new furnaces had not been wired for common, landed common wire on both furnaces and thermostats. Tested system to make sure units are operating. No other issues present at this time
No heat in braselton. Arrived on site, found bad blower motor, will need to order one from trane
No heat braselton. Completed diagnostic on 14 year old furnace. Inducer poets were clogged. Cleared ports. System came on. Inducer motor is failing. Running really high amps. Flame sensor is starting to erode and could fail. Heat exchanger shows signs of corrosion and could be detrimental to health if holes occur in exchanger. System should be replaced due to condition and cost of repairs.
Heat pump maintenance in Braselton, Georgia. One system- bonus room system. Changed filter. Tested mechanical and electrical components, all in good shape. Static pressure readings are in good shape. System is heating at this time.
Free consultation for new heat pump Braselton Georgia 30517
One system heat maintenance in braselton. Arrived on site, checked heat strips, electrical connections, amp draw and capacitance. Found system without water safty in crawl space. Recommended installing overflow switch to system as well as surge protectors for each piece of equipment and a compressor assist kit to outdoor unit to take some of the load off of the compressor uppon startup. Unit is operating at this time.
Completed duct run in Braselton Georgia . Mastic . Cleaned .
Gave estimate on replacing a air duct and doing a tune up on the equipment and cleaning . Family wants to move forward. Office will call and schedule the repair . Thank you .
Furnace maintenance in Braselton, Georgia. Three systems. Changed upstairs filter provided by customer and basement filter. Tested mechanical and electrical components. Found upstairs gas line drip leg not up to code, it isnâ€™t long enough. Found gas line going into all furnaces not up to code, flexible gas line should not be inside furnace. Recommend making upstairs drip line longer and replacing flexible gas lines with hard pipe inside all furnaces to bring systems up to code. Brought all three gas lines up to code by moving flexible gas line to outside of furnaces, putting hard pipe inside furnaces and extending upstairs drip leg. Replaced main level flame safety sensor. Systems are heating at this time.
AC repair in Braselton. Discovered main floor variable speed blower motor not coming on. Cycled power to diagnose. Call motor started working system is 13 years old at the end of its lifespan and replacement over any repair is recommended. Need to email and keep in touch with homeowner about scheduling a consultation. System working at this time but do not know how long it will be
â€¢ Completed a two system heating maintenance in Braselton Georgia. Prepaid visit today. Checked the safety and performance. Checked heating integrity. Checked heating elements. Completed maintenance cleaning on the furnace. Both hearings systems are working properly. Family provided filters . Replaced the main floor filter today and the upstairs filter still had some life in it . â€¢Attic insulation is low and below the beams . Would recommend bringing the insulation to specks for better comfort and lower utility bills. Would also recommend a attic tent .
Heating tune up braselton. Completed tune up on 3 year old zoned system. System is heating both zones properly. All electrical connections are clean and tight. Everything inside system is clean. All safety switches working. Insulation in attic is good. System does not have enough return air for size of system. Should have at least one more return in house.
Heating maintenance in Braselton, Georgia. Two systems. Changed filters.tested mechanical and electrical components. Breaker for downstairs heat pump failed. Replaced downstairs heat pump breaker. All other components in good shape. Recommend installing hard start kits in system to reduce load on compressors so they start smoother, runs smoother and therefore last longer. Recommend surge protection to protect equipment from power surges. Recommend pureairx air purifiers to kill mold, bacteria, germs and viruses for improved air quality. Systems are heating at this time.
No cool in braselton. Arrived on site, found all systems with clogged filters, upstairs system and basement system had tripped breakers, reset and tested, both immediately tripped again. Tested outdoor unis and found both compressors grounded. Need to replace both systems. Main level found dirty 20x25x5" media filter clogged customer will replace himself. Turned off power to furnace till he is able to get new filter so no more damage is done to system.
Complete 2 heating maintenance for both gas furnace in braselton. Find upstairs 15 year old carrier gas furnace operating with in manufacturer spec. No concern at this time. Suggest in-line water protection and suggest air purifier system to help improve air quality and prevent molding. Find main level Amana gas furnace 3 year old operating with in manufacturer spec. Change main filter 16x25x5 filter customer provided. Suggest air purifier system. Both gas furnace operating at this time.
Heating maintenance braselton. Completed heating maintenance on 4 year old system. Blower and evap coil clean. Static pressure is good meaning system has good air flow. Filter is good. Heat strips are working properly. Insulation is good in attic. System has no back up water safety to protect system as well as house from water damage. System would also greatly benefit from having surge protector installed as well as UV light treatment to kill bacteria viruses and chemicals in air that could cause harm to residents.
Completed two system heating maintenance in Braselton Georgia . Changed air filters . Checked the safety and performance of the heating operation. Checked the integrity and amps . Checked heating elements. Both systems are heating at this time . Prepaid visit today .
Heating maintenance braselton. Completed 4 system heating maintenance. All 4 systems 4 years old. All clean with working electrical components. Static pressure on all are good as wel as combustion. Left filters for systems. None of the systems have back up water safety devices. Recommend inline float switches to all to protect the system as wel as the house from water damage. Systems would greatly benefit from having surge protectors added to system as well as electro static filters to better keep systems and home cleaner longer and UV air treatments installed to sanatize air and kill bacteria viruses and chemicals in the air that could cause harm to residents.
Flowery branch new furnace
Heating maintenance braselton. Completed one system heating maintenance. Found system 10 years old and working properly. Heat strips cleaned and working in range. Blower is clean. Coil is clean. Changed filter recommend electro static filter for better cleaning. Recommend surge protector for air handler. Also insulation in attic is below beams. Recommend blowing in to avoid heat loss
Looking over cooling system in Braselton Georgia . Second opinion on the upstairs system . System is slightly low on R22 charge and showing its age , the indoor coil is very rusty took pictures . Talked over some options on what we can do . Family has a home warranty and at this time they donâ€™t want to put any repairs on the unit and they want to let it ride and get it through the little bit of warm weather we have left since itâ€™s almost winter .