Alpharetta, GA has turned to Comfort Control since 1992 for professional cooling and heating repairs, installations and maintenance.
Check out these reviews and see how we deliver air conditioning and heating service that residents of Alpharetta, GA turn to us for again and again.
On average, in the Alpharetta, GA area, you can anticipate paying between $2,000 - $8,000 to purchase a new mini split heat pump and have it professionally installed. The price will depend on the quality of the system you choose and how many zones need to be added. Overall the price is about the same as a traditional HVAC system with ductwork.
Most air conditioning repairs are fairly minor and end up costing around $350. Some larger repairs, such as the replacement of the compressor or a complicated refrigerant leak, could cost thousands of dollars. Ultimately, what you will end up paying depends almost entirely on what is wrong with the unit. If you are having issues with your air conditioner and would like to schedule a service or get a quote, contact Comfort First!
Experts recommend that you have your air conditioner serviced once a year. Annual maintenance performed will ensure that your unit is:
- Working well
- Running more efficiently
- Preventing breakdowns and repairs
- Going to last longer
for Alpharetta, GA
PAUL - Alpharetta, GA
I had a concern with how low to the ground the AC unit was installed. Took a little time but they came out today to raise the unit a few inches and I’m happy that it’s off the ground.
Tammy - Alpharetta, GA
Jordan Roper was very professional and a pleasure to work with. He wore a mask and was careful about social distancing. He was friendly and explained everything he did. Great job!
Thank you Vu!
DONNA - Alpharetta, GA
As always you did an awesome job. 🙂
Michael - Alpharetta, GA
Fine service for 3 year old system
PAUL - Alpharetta, GA
It was as expected for having units that are only 3 years old.
CHRISTOPHER - Alpharetta, GA
Jordan is a good service technician. He is timely, honest and professional.
Rebecca - Alpharetta, GA
Thankful for his efficient expertise!
BARBARA - Alpharetta, GA
CHRIS - Alpharetta, GA
Timely with great service.
Prompt professional service
TIM - Alpharetta, GA
Assessment of Service
DAVE - Alpharetta, GA
Good job communication, efficiency of service, care in the home and recommendations
MURRAY - Alpharetta, GA
VINCENT - Alpharetta, GA
Found and fixed the concern
GREAT SERVICE, EXPERIENCED TECH,
DAVID - Alpharetta, GA
Vu is a highly experienced tech. Excellent to work with, informative, respectful. Only tech I will allow to work on my systems.
Great customer service! Jordan was courteous and professional
Earl - Alpharetta, GA
GLEN - Alpharetta, GA
JAMES - Alpharetta, GA
Tran is very thorough
Cynthia - Alpharetta, GA
Tran was very thorough and explained the options for what we needed on our HVAC system. Very pleasant and knowledgeable technician.
Awesome technician. Great service
NICKOLAS - Alpharetta, GA
VINCENT - Alpharetta, GA
Denise - Alpharetta, GA
ZACH - Alpharetta, GA
Friendly service - professional staff
Teun - Alpharetta, GA
Donovan - Alpharetta, GA
Ta was very knowledgeable about HVAC theory and equipment. He was very straight forward in his investigation and identified the problem quickly after troubleshooting.
Professional and prompt service!
Teun - Alpharetta, GA
Friendly staff and professional service.
Ac service in Alpharetta. Discovered service breaker tripped. Tested all components and reset breaker. System cooling at this time but is 16 year old and worn out. Replacement is highly recommended
Ac repair in Alpharetta. Wired in system with new properly sized wire from indoor to outdoor unit. Tested system in heat and cool and system cycling on and off in both modes. System operation normal at this time
No cool upstairs system. Check and find 16 year old Trane air conditioning system In Alpharetta. Find air conditioning system fail due to burnt contactor. Find system 16 year old with missing hard start kit, weak and worn capacitor, rusted Evaporator coil in attic and missing in line water protection. Customer want to repair system for today visit. Replace burnt contactor and install starter kit. System operating at this time.
Ac service Alpharetta. Completed diagnostic. Found system low on refrigerant. Leaking out of evaporator coil. System is 16 years old. Due to age recommend replacing. Having him come out Monday to give quote.
Looked over system . Found the indoor coil is in bad shape and very rusty . Took pictures. Can hear the blower housing rattling . Took video . Inrush Amps are way to high . Amps are at 98.5 which should not surpass 86LRA amps . System is struggling due to age and conditions with the amps and rusty coil . System operates on R22 which is phased out . Checked ohms on the compressor and they are restricted. Compressor is going bad / struggling. Would recommend upgrading the system . â€¢Family wants to try putting a compressor saver on the system and see what happens . This repair is no guarantee fix and could possibly not work . Family is aware . Put the compressor saver on and system is now operating but again the compressor could still fail in the near future. This is a bandaid fix. System also needs a air filter in it as soon as possible. Unit is working at this time after installing the hard start kit . If this fails in the near future I would highly recommend upgrading the equipme
Complete install new Goodman evaporator coil for main system Alpharetta. Pressure test, add ac renew and acids treatment on new ac system, install hard start kit per manufacturer spec. Recharge system to manufacturer spec. Test and system operating at this time. Waive service fee and sign 1 CCI plan for main level system. Complete cooling pm check. Wire condensation pump for water safety.
No cool main level system in Alpharetta. Check and find new system installed last Amana 2.5 ton. Find system empty of charge, find evaporator in basement for main level air conditioning system R22 and leaking charge. Find outdoor unit R410A system, miss-match. Need to replace evaporator, flush line and oil treatment. Give customer estimate. Per Jeff courtesy leak search.
One system tuneup in Alpharetta. Arrived on site, indoor; changed filter and cleared drain line. Checked electrical connections, amp draw and capacitance. Suggest installing secondary water safety switch to prevent water damage to electrical systems. Outdoor; cleaned condenser coils and checked refrigerant pressures. Checked electrical connections, amp draw and capacitance. Recommend installing compressor assist kit and surge protection to prevent damage to electrical systems. Unit is operating normally at this time
Ac repair in Alpharetta. Installed new outdoor pad underneath unit.
Ac maintenance in Alpharetta. 1 system. Discovered system has no water safeties or compressor saver. Furnace is aged and will need to be replaced soon. Homeowner declined water safeties
Ac maintenance in Alpharhetta. 2 system cool pm. Cleaned outdoor coils and checked all components. All components tested within normal manufacturing spec. Discovered upstairs system with no drain line water safety and neither system with compressor saver har start kits to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the systems. Performed all repairs. System operation normal at this time
Remote consultation for mini split in Basement in Alpharetta, GA.
1 system HVAC inspection in Alpharhetta. Ac is 2 years old and furnace is 7 years old. Systems ducts need to be cleaned along with blower wheel and dryer vent. System would also greatly benefit from compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the system. The finished basement is unconditioned which cause a concern for mold growth with basements naturally being more humid. Johnathan would like a consultation for a Mini Split
No cool system package unit#4. Find burnt capacitor kit, and blown kick start, burnt and damage wires. Find compressor terminals overheated and burnt. Find blower assembly damage and burnt. System have no power from breaker due to electrical burnt and short.
1 system hvac inspection. Furnace is 29 years old and outside of is outside of its normal life expectancy. Carbon monoxide removal vent is rusted and has holes in it, blower wheel is extremely dirty and needs to be cleaned as it causes the wheel to be unbalanced which causes premature failure of the blower motor. Ac is 3 years old and is functioning properly but needs a maintenance as the outdoor coil is dirty and not allowing proper airflow
Homeowner concern with how much water the system is producing and draining into the yard. Explained that it is normal and they system is doing a great job of pulling the humidity out of the space.
No cool upstairs. Discovered outdoor main electrical switch failed and fried float switch in attic. Replaced both and added drain line water safety to system. System operation normal at this time
Main level thermostat blank with no power upon arrival. Tested system out and found no oddities. Reset power and system operation normal. House could have experienced an electrical surge last night with the storms. Recommend surge protection for systems
Picked up old ac outdoor unit
Systems low voltage wire from indoor to outdoor heat pump is not heavy enough gauge so it has previously been wired for unit to operate temporarily until wire was changed by electrician. Temporary fix a year ago was hot wiring the outdoor unit to always stay on and homeowner would turn off by breaker next to the thermostat. Wire was never replaced, thermostat satisfied, outdoor unit stated running with indoor fan not running and system is freezing up. Wire needs to be replaced with 18/8 and us come out and wire system up for proper operation
System 22 years old and leaking refrigerant. System needs of be replaced. Garrett scheduled for tomorrow 6-8 for replacement options
2 system cool pm. Cleaned outdoor coils and checked all components. Discovered both systems with weak compressor starters. Upstairs system has no drain line water safety. Both systems could use a duct cleaning. Both systems cooling at this time
Complete HVAC inspection. Find 3 year old Trane system operating with overcharged system, flue pipe not up to code, ductwork dirty and not up to code and missing insulation for supply metal line in wall. Find outdoor lineset insulation missing spot.