Alpharetta, GA has turned to Comfort Control since 1992 for professional cooling and heating repairs, installations and maintenance.
Check out these reviews and see how we deliver air conditioning and heating service that residents of Alpharetta, GA turn to us for again and again.
On average, in the Alpharetta, GA area, you can anticipate paying between $2,000 - $8,000 to purchase a new mini split heat pump and have it professionally installed. The price will depend on the quality of the system you choose and how many zones need to be added. Overall the price is about the same as a traditional HVAC system with ductwork.
Most air conditioning repairs are fairly minor and end up costing around $350. Some larger repairs, such as the replacement of the compressor or a complicated refrigerant leak, could cost thousands of dollars. Ultimately, what you will end up paying depends almost entirely on what is wrong with the unit. If you are having issues with your air conditioner and would like to schedule a service or get a quote, contact Comfort First!
Experts recommend that you have your air conditioner serviced once a year. Annual maintenance performed will ensure that your unit is:
- Working well
- Running more efficiently
- Preventing breakdowns and repairs
- Going to last longer
for Alpharetta, GA
Fast service, satisfied with work.
ANNETTE - Alpharetta, GA
Very good and fast repair.
DONNA - Alpharetta, GA
CHRISTOPHER - Alpharetta, GA
Comfort Control has been servicing my HVAC for over 15 years and have generally done a good job. I love how they provide text alerts notifying you that the technician is in route and who it is. My only complaint is the constant up selling. They just installed a new HVAC system and now I’m being told the duct work needs to have new insulation wrap. I just had new insulation blown in 3 years ago by a different company and now I’m being told I should have more insulation blown in. When they installed my previous system 9 years ago after that it was one thing after another that they said I should have done to fix the things that were not done or done incorrectly. Despite these complaints I stick with them because of their prompt and overall good service.
GLEN - Alpharetta, GA
Excellent knowledgeable tech
Very happy with service by Vu
ANNETTE - Alpharetta, GA
Mohamed - Alpharetta, GA
PAUL - Alpharetta, GA
I had a concern with how low to the ground the AC unit was installed. Took a little time but they came out today to raise the unit a few inches and I’m happy that it’s off the ground.
Tammy - Alpharetta, GA
Jordan Roper was very professional and a pleasure to work with. He wore a mask and was careful about social distancing. He was friendly and explained everything he did. Great job!
Thank you Vu!
DONNA - Alpharetta, GA
As always you did an awesome job. 🙂
Michael - Alpharetta, GA
Fine service for 3 year old system
PAUL - Alpharetta, GA
It was as expected for having units that are only 3 years old.
CHRISTOPHER - Alpharetta, GA
Jordan is a good service technician. He is timely, honest and professional.
Rebecca - Alpharetta, GA
Thankful for his efficient expertise!
BARBARA - Alpharetta, GA
CHRIS - Alpharetta, GA
Timely with great service.
Prompt professional service
TIM - Alpharetta, GA
Assessment of Service
DAVE - Alpharetta, GA
Good job communication, efficiency of service, care in the home and recommendations
MURRAY - Alpharetta, GA
VINCENT - Alpharetta, GA
Found and fixed the concern
GREAT SERVICE, EXPERIENCED TECH,
DAVID - Alpharetta, GA
Vu is a highly experienced tech. Excellent to work with, informative, respectful. Only tech I will allow to work on my systems.
Great customer service! Jordan was courteous and professional
Earl - Alpharetta, GA
GLEN - Alpharetta, GA
JAMES - Alpharetta, GA
Tran is very thorough
Cynthia - Alpharetta, GA
Tran was very thorough and explained the options for what we needed on our HVAC system. Very pleasant and knowledgeable technician.
Awesome technician. Great service
NICKOLAS - Alpharetta, GA
No heat upstairs in Alpharetta. Check and find Amana gas furnace flame sensor fail and system calibration off. Replace sensor and complete combustion calibration service to help temperature, improve efficiency and balance blower assembly. System operating at this time. Suggest surge protection and additional water protection in attic. Suggest air purifier system.
Water heater not working in Alpharetta, Georgia. Right water heater pilot went out. Relit pilot light. Found slight drip inside water heater dripping onto burner area. This means thereâ€™s a small leak in the tank. Recommend replacement of water heater. Customer is replacing water heater. Collected $500 deposit so total after install is $975.
Heating maintenance in Alpharetta. Tested operation of 1 heat pump system. All components tested within normal manufacturing spec. Thermostats are functional but outdated and inefficient along with main level stat hanging by the wires. Recommend upgrading both thermostats. System heating normal at this time
Free consultation in Alpharetta Georgia 30005 hvac estimate
Sign 3 comfort control maintenance plan and complete heating maintenance in Alpharetta. Find upstairs 17 year old Trane gas furnace operating with rusted evaporator coil, worn ignition and flame sensor, missing in-line water protection. Find main level 17 year old Trane gas furnace operating with worn ignition and flame sensor, under-fire furnace with high CO level. System dirty and no water protection. Find basement Payne 12 year old Airhandler leaking water due to clogged drain. Clear drain for customer and change filter. System operating at this time. Suggest in-line water protection. Customer want to wait on repairs. All 3 system operating at this time. Give customer estimates.
Sign up 2 comfort control maintenance plan and complete 2 heating maintenance in Alpharetta. Find 2 Amana gas furnace in attic. Change upstairs filter, check safety and operations. Find 2 7 year old furnace operating with weak flame sensor and under-fire furnace. Find duct works undersize and not R-8 rated. Complete repair on furnace, replace flame sensor and combustion calibration service. Suggest surge protection, suggest in-line water protection and air purifier.
One system heat maintenance in Alpharetta. Arrived on site, checked upstairs unit. Main level was blocked off at the time of visit. Changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found system with dirty blower assembly, blower motor starting to leak oil due to stress put on it from the dirt on the assembly as well as a low reading capacitor, gas line not run properly (needs Drip-t). Combustion analysis states that combustion is too oxygenated and should be adjusted. Recommend equipment be replaced as apposed to repair. Unit is operating at this time.
HVAC in Alpharetta. Dropped filters off by garage door between house and plant due to Highwinds did not want it blowing away.
Heating repair in Alpharetta. Discovered system locked out on pressure switch. Cleaned port and furnace heating normally. Tested multiple times and system heating without issue. Homeowner signed up for maintenance membership. Performed maintenance on furnace. Changed apco ultraviolet light lamp. System operation normal at this time
Heating repair in Alpharetta. Discovered furnace power switch off. Turn the power switch on and system started heating. Checked operation and all components. Discovered weak blower motor controller but all other components testing within normal manufacturing specs. System is eating at the Stone
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. All components tested within normal manufacturing spec. Upstairs has no drain line water safety. Downstairs system ductwork dirty and needs a cleaning. System and home would greatly benefit from ultraviolet light systems to combat organic and viral growth in the system and throughout the home. Both systems heating at this time
Heating maintenance in Alpharetta. Tested operation of 1 furnace. All components tested within normal manufacturing spec. System and home would greatly benefit from an ultraviolet light system to combat organic and viral growth in the system and throughout the home. System heating at this time
Ac repair in Alpharetta. Discovered upstairs system low on charge. Homeowner chose to top system off. Charged system. System cooling at this time. System really need a maintenance
HVAC inspection in Alpharetta. Tested operation of 2 HVAC systems. Ac portion of both systems operation is normal other than the upstairs ac is missing service caps for refrigerant service ports and both ac systems need maintenance as the outdoor coils are dirty. Discovered upstairs furnace with dirty blower wheel, weak and leaking blower motor controller and dirty ductwork. Main level furnace which is located in the basement also has a dirty blower wheel, weak blower motor controller and dirty ductwork, but also has a very worn ignition system. Both upstairs and main level furnace are 19 years old. Typical life span is 10-15 years. Due to age and condition of furnaces, replacement is highly recommended.
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. Downstairs system producing high amounts of carbon monoxide, combustion chamber is rusted, flame safety has heavy signs of wear as well as the ignition system, system could use a duct cleaning. Upstairs furnace has no drain line water safety and gas line is not up to code and system could use a duct cleaning as well. Both systems are at end of expected life and replace of downstairs system should be considered. Both systems heating at this time
Heating tune up in Alpharetta. Tested operation of 2 furnaces. Upstairs furnace has unbalanced blower wheel causing whole system to vibrate, dirty ducts, no drain line water safety and gas line drip leg is not to code downstairs system has only return duct extremely damaged and supply plenum insulation damaged and supply duct damaged by cat. Furnaces is over firing shutting off on high limit. Downstairs suction line is too small for systems capacity and the main electrical switch is extremely burnt and pitted
Heating maintenance in Alpharetta. Homeowner stated that heat was not working. Tested operation of 1 furnace. Turned system on and system started heating. Discovered weak blower motor controller, weak flame safety, ignition system with signs of wear, and a dirty blower wheel. Syste, is 15 years old and due to age and condition replacement is highly recommended over any repair. Need to follow up tomorrow to schedule consultation
Installed Mod kit and thermostat. Warranty .
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. Discovered left side furnace with weak flame safety. All other components tested within normal manufacturing spec on both units. Both systems heating at this time. Replaced flame safety in left side carrier furnace
Heating repair in Alpharetta. Discovered 17 year old system having issues with safeties. System intermittently tripping on high limit. Tested all safeties but could not replicate. Discovered system flame safety and blower motor controller very weak. System is very old and do not know how long it will last with any repair. Replacement is highly recommended over any repair. Consultation scheduled for tomorrow for 1pm-3pm for replacement options
Complete 2 heating maintenance in Alpharetta. Find upstairs Amana gas furnace operating with in manufacturer. No concern at this time. Find downstairs carrier gas furnace operating with in manufacturer spec. Find flame sensor starting to get weak and may need to replace next fall visit. Change both system filter, check safety and operations. Both furnace operating at this time.
HVAC issues in Alpharetta Georgia. System has a bad Lennox thermostat. Thermostat needs replacing. Supply house for Lennox is not open till Monday . Will have to see what the stock is on the communications thermostat. Will call Monday and inform the family on availability.
Heating maintenance Alpharetta. Completed 2 system maintenance. Upstairs is 21 years old with dirty blower wheel. Everything else is running good. Changed filter inside furnace which is not optimum filter placement. Gas line is ran improper. Sediment trap will not collect anything the way it is now. Insulation in attic is good. Downstairs is good. Clean everything. Changed filter. Gas line ran proper. Systems are heating at this time.
Heating maintenance in Alpharetta. Tested operation of 1 furnace. All components tested within normal manufacturing spec. Ductwork has dirt and dust build up. System needs duct cleaning and and ultraviolet light system to maintain indoor air quality, combat organic growth and maintain indoor air health. System heating at this time
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. All components tested within normal manufacturing spec. Upstairs system does not have drain line water safety to help prevent flooding in the case of common drain line clogs. Both systems need ultraviolet light systems to improve and maintain indoor air quality. Both systems heating at this time